-- MySQL Administrator dump 1.4
--
-- ------------------------------------------------------





--
-- Create schema samfm
--

CREATE DATABASE IF NOT EXISTS samfm;
USE samfm;

--
-- Definition of table `affect_financiere`
--

CREATE TABLE `affect_financiere` (
  `afin_seq` int(11) NOT NULL auto_increment,
  `afin_code` varchar(10) default NULL,
  `afin_libelle` varchar(35) default NULL,
  `afin_composee` tinyint(3) unsigned default NULL,
  PRIMARY KEY  (`afin_seq`),
  UNIQUE KEY `afin_code` (`afin_code`)
) ENGINE=InnoDB AUTO_INCREMENT=3 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `affect_financiere`
--

INSERT INTO `affect_financiere` (`afin_seq`,`afin_code`,`afin_libelle`,`afin_composee`) VALUES 
 (1,'RH','Ressources Humaines',1),
 (2,'COM','Communication',1);


--
-- Definition of table `agence`
--

CREATE TABLE `agence` (
  `age_seq` int(11) NOT NULL auto_increment,
  `age_code` varchar(10) default NULL,
  `age_libelle` varchar(50) default NULL,
  PRIMARY KEY  (`age_seq`),
  UNIQUE KEY `age_code` (`age_code`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `agence`
--



--
-- Definition of table `article`
--

CREATE TABLE `article` (
  `arti_seq` int(11) NOT NULL auto_increment,
  `arti_code` varchar(15) NOT NULL,
  `arti_libelle` varchar(40) NOT NULL,
  `arti_unite` char(4) NOT NULL,
  `arti_reffab` varchar(15) default NULL,
  `arti_codetva` tinyint(3) default NULL,
  `arti_interch` tinyint(2) default NULL,
  `arti_infocomp` text,
  `arti_fama_fk` int(11) NOT NULL default '0',
  `arti_entr_fk` int(11) default NULL,
  `arti_codebarre` varchar(128) default NULL,
  `arti_datmaj` datetime default NULL,
  `arti_zus_maj_fk` int(11) default NULL,
  UNIQUE KEY `art_seq` (`arti_seq`),
  KEY `arti_zus_maj_fk` (`arti_zus_maj_fk`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `article`
--



--
-- Definition of table `article_attr`
--

CREATE TABLE `article_attr` (
  `arti_att_seq` int(16) NOT NULL auto_increment,
  PRIMARY KEY  (`arti_att_seq`)
) ENGINE=InnoDB AUTO_INCREMENT=4 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `article_attr`
--

INSERT INTO `article_attr` (`arti_att_seq`) VALUES 
 (1),
 (2),
 (3);


--
-- Definition of table `att_attribut`
--

CREATE TABLE `att_attribut` (
  `atat_seq` int(11) NOT NULL auto_increment,
  `atat_libelle` varchar(30) default NULL,
  `atat_attb_fk` int(11) default NULL,
  `atat_atgr_fk` int(11) default NULL,
  `atat_type` int(11) default NULL,
  `atat_longueur` int(11) default NULL,
  `atat_ordre` int(11) default NULL,
  `atat_part_decimale` int(11) default NULL,
  `atat_obligatoire` tinyint(3) unsigned default NULL,
  `atat_champ_lie` varchar(32) default NULL,
  `atat_table_valeurs_lie` varchar(32) default NULL,
  `atat_regex_validation` varchar(255) default NULL,
  `atat_valeur_par_defaut` varchar(10) default NULL,
  `atat_atat_ori_fk` int(11) default NULL,
  PRIMARY KEY  (`atat_seq`),
  KEY `atat_attb_fk` (`atat_attb_fk`),
  KEY `atat_atgr_fk` (`atat_atgr_fk`),
  KEY `atat_atat_ori_fk` (`atat_atat_ori_fk`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `att_attribut`
--



--
-- Definition of table `att_comp_coul`
--

CREATE TABLE `att_comp_coul` (
  `ATT0000032_seq` int(16) NOT NULL auto_increment,
  `ATT0000032_libelle` varchar(30) NOT NULL,
  PRIMARY KEY  (`ATT0000032_seq`)
) ENGINE=InnoDB AUTO_INCREMENT=9 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `att_comp_coul`
--

INSERT INTO `att_comp_coul` (`ATT0000032_seq`,`ATT0000032_libelle`) VALUES 
 (1,'ROUGE'),
 (2,'VERT'),
 (3,'NOIR'),
 (4,'BLEU'),
 (5,'JAUNE'),
 (6,'GRIS'),
 (7,'BLANC'),
 (8,'ORANGE');


--
-- Definition of table `att_ctra_nom`
--

CREATE TABLE `att_ctra_nom` (
  `ATT0000033_seq` int(16) NOT NULL auto_increment,
  `ATT0000033_libelle` varchar(30) NOT NULL,
  PRIMARY KEY  (`ATT0000033_seq`)
) ENGINE=InnoDB AUTO_INCREMENT=3 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `att_ctra_nom`
--

INSERT INTO `att_ctra_nom` (`ATT0000033_seq`,`ATT0000033_libelle`) VALUES 
 (1,'M. Germain'),
 (2,'Mme Lampart');


--
-- Definition of table `att_ctra_test`
--

CREATE TABLE `att_ctra_test` (
  `ATT0000034_seq` int(16) NOT NULL auto_increment,
  `ATT0000034_libelle` varchar(30) NOT NULL,
  PRIMARY KEY  (`ATT0000034_seq`)
) ENGINE=InnoDB AUTO_INCREMENT=6 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `att_ctra_test`
--

INSERT INTO `att_ctra_test` (`ATT0000034_seq`,`ATT0000034_libelle`) VALUES 
 (4,'GERM'),
 (5,'LAMP');


--
-- Definition of table `att_groupe`
--

CREATE TABLE `att_groupe` (
  `atgr_seq` int(11) NOT NULL auto_increment,
  `atgr_attb_fk` int(11) default NULL,
  `atgr_ordre` int(11) default NULL,
  `atgr_libelle` varchar(30) default NULL,
  `atgr_atgr_ori_fk` int(11) default NULL,
  PRIMARY KEY  (`atgr_seq`),
  KEY `atgr_attb_fk` (`atgr_attb_fk`),
  KEY `atgr_atgr_ori_fk` (`atgr_atgr_ori_fk`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `att_groupe`
--



--
-- Definition of table `att_oper_2`
--

CREATE TABLE `att_oper_2` (
  `ATT0000026_seq` int(16) NOT NULL auto_increment,
  `ATT0000026_libelle` varchar(30) NOT NULL,
  PRIMARY KEY  (`ATT0000026_seq`)
) ENGINE=InnoDB AUTO_INCREMENT=5 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `att_oper_2`
--

INSERT INTO `att_oper_2` (`ATT0000026_seq`,`ATT0000026_libelle`) VALUES 
 (1,'moquette'),
 (2,'parquet'),
 (3,'carrelage'),
 (4,'lino');


--
-- Definition of table `att_oper_nivurg`
--

CREATE TABLE `att_oper_nivurg` (
  `ATT0000027_seq` int(16) NOT NULL auto_increment,
  `ATT0000027_libelle` varchar(30) NOT NULL,
  PRIMARY KEY  (`ATT0000027_seq`)
) ENGINE=InnoDB AUTO_INCREMENT=6 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `att_oper_nivurg`
--

INSERT INTO `att_oper_nivurg` (`ATT0000027_seq`,`ATT0000027_libelle`) VALUES 
 (1,'2 heures'),
 (2,'4 heures'),
 (3,'1 journée'),
 (4,'Immédiat'),
 (5,'1 semaine');


--
-- Definition of table `att_sit_horaireacc`
--

CREATE TABLE `att_sit_horaireacc` (
  `ATT0000029_seq` int(16) NOT NULL auto_increment,
  `ATT0000029_libelle` varchar(30) NOT NULL,
  PRIMARY KEY  (`ATT0000029_seq`)
) ENGINE=InnoDB AUTO_INCREMENT=4 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `att_sit_horaireacc`
--

INSERT INTO `att_sit_horaireacc` (`ATT0000029_seq`,`ATT0000029_libelle`) VALUES 
 (1,'8h30-17h30'),
 (2,'9h00-17h00'),
 (3,'9h00-18h00');


--
-- Definition of table `att_zone_zonepro`
--

CREATE TABLE `att_zone_zonepro` (
  `ATT0000030_seq` int(16) NOT NULL auto_increment,
  `ATT0000030_libelle` varchar(30) NOT NULL,
  PRIMARY KEY  (`ATT0000030_seq`)
) ENGINE=InnoDB AUTO_INCREMENT=3 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `att_zone_zonepro`
--

INSERT INTO `att_zone_zonepro` (`ATT0000030_seq`,`ATT0000030_libelle`) VALUES 
 (1,'oui'),
 (2,'non');


--
-- Definition of table `attribut`
--

CREATE TABLE `attribut` (
  `attr_seq` int(11) NOT NULL auto_increment,
  `attr_attg_fk` int(11) default NULL,
  `attr_libelle` varchar(40) NOT NULL,
  `attr_nb_car` int(11) NOT NULL default '0',
  `attr_module_id` tinyint(4) NOT NULL default '0',
  `attr_type` int(11) NOT NULL default '0',
  `attr_confidentiel` int(11) NOT NULL default '0',
  `attr_ordre` int(11) NOT NULL default '0',
  `attr_affiche_di` int(1) default '0',
  PRIMARY KEY  (`attr_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `attribut`
--



--
-- Definition of table `attribut_groupe`
--

CREATE TABLE `attribut_groupe` (
  `attg_seq` int(11) NOT NULL auto_increment,
  `attg_libelle` varchar(25) NOT NULL,
  `attg_ordre` int(11) NOT NULL default '0',
  `attg_module_id` tinyint(4) NOT NULL default '0',
  PRIMARY KEY  (`attg_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `attribut_groupe`
--



--
-- Definition of table `attribut_groupe_mlg`
--

CREATE TABLE `attribut_groupe_mlg` (
  `attg_mlg_seq` int(11) NOT NULL default '0',
  `attg_mlg_libelle` varchar(25) default NULL,
  PRIMARY KEY  (`attg_mlg_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `attribut_groupe_mlg`
--



--
-- Definition of table `attribut_liste_valeur`
--

CREATE TABLE `attribut_liste_valeur` (
  `atlv_seq` int(11) NOT NULL auto_increment,
  `atlv_attr_fk` int(11) NOT NULL default '0',
  `atlv_valeur` varchar(40) NOT NULL,
  PRIMARY KEY  (`atlv_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `attribut_liste_valeur`
--



--
-- Definition of table `attribut_mlg`
--

CREATE TABLE `attribut_mlg` (
  `attr_mlg_seq` int(11) NOT NULL default '0',
  `attr_mlg_libelle` varchar(40) default NULL,
  PRIMARY KEY  (`attr_mlg_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `attribut_mlg`
--



--
-- Definition of table `badges`
--

CREATE TABLE `badges` (
  `badg_seq` int(11) NOT NULL auto_increment,
  `badg_vst_fk` int(11) NOT NULL default '0',
  `badg_nb_impression` int(3) NOT NULL default '0',
  PRIMARY KEY  (`badg_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `badges`
--



--
-- Definition of table `bat_document`
--

CREATE TABLE `bat_document` (
  `batd_seq` int(11) NOT NULL auto_increment,
  `batd_bat_fk` int(11) NOT NULL default '0',
  `batd_url` varchar(100) NOT NULL,
  PRIMARY KEY  (`batd_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `bat_document`
--



--
-- Definition of table `batiment`
--

CREATE TABLE `batiment` (
  `bat_seq` int(11) NOT NULL auto_increment,
  `bat_code` varchar(6) default NULL,
  `bat_libelle` varchar(35) default NULL,
  `bat_surface_totale` decimal(16,2) default NULL,
  `bat_surface_utile` decimal(16,2) default NULL,
  `bat_modtotal` tinyint(3) unsigned default NULL,
  `bat_modutile` tinyint(3) unsigned default NULL,
  `bat_datconst` datetime default NULL,
  `bat_bdocument` tinyint(3) unsigned default NULL,
  `bat_emprise` decimal(16,2) default NULL,
  `bat_blocnote` text,
  `bat_codeconca` varchar(15) default NULL,
  `bat_adr1` varchar(45) default NULL,
  `bat_adr2` varchar(45) default NULL,
  `bat_cp` varchar(6) default NULL,
  `bat_ville` varchar(25) default NULL,
  `bat_region` varchar(25) default NULL,
  `bat_pays` varchar(25) default NULL,
  `bat_sat_fk` int(11) default NULL,
  `bat_code_barre` varchar(15) default NULL,
  `bat_cdbr_fk` int(11) default NULL,
  `bat_nb_usgr` int(11) default NULL,
  `bat_afin_fk` int(11) default NULL,
  `bat_crit_fk` int(11) default NULL,
  `bat_ctra_fk` int(11) default NULL,
  `bat_communaute` tinyint(3) unsigned default NULL,
  `bat_tppr_fk` int(11) default NULL,
  `bat_maint_niveau` tinyint(3) unsigned default NULL,
  `bat_datmaj` datetime default NULL,
  `bat_zus_maj_fk` int(11) default NULL,
  PRIMARY KEY  (`bat_seq`),
  UNIQUE KEY `bat_codeconca` (`bat_codeconca`),
  KEY `bat_code` (`bat_code`),
  KEY `bat_libelle` (`bat_libelle`),
  KEY `bat_sat_fk` (`bat_sat_fk`),
  KEY `bat_afin_fk` (`bat_afin_fk`),
  KEY `bat_crit_fk` (`bat_crit_fk`),
  KEY `bat_crit_fk_2` (`bat_crit_fk`),
  KEY `bat_tppr_fk` (`bat_tppr_fk`)
) ENGINE=InnoDB AUTO_INCREMENT=5 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `batiment`
--

INSERT INTO `batiment` (`bat_seq`,`bat_code`,`bat_libelle`,`bat_surface_totale`,`bat_surface_utile`,`bat_modtotal`,`bat_modutile`,`bat_datconst`,`bat_bdocument`,`bat_emprise`,`bat_blocnote`,`bat_codeconca`,`bat_adr1`,`bat_adr2`,`bat_cp`,`bat_ville`,`bat_region`,`bat_pays`,`bat_sat_fk`,`bat_code_barre`,`bat_cdbr_fk`,`bat_nb_usgr`,`bat_afin_fk`,`bat_crit_fk`,`bat_ctra_fk`,`bat_communaute`,`bat_tppr_fk`,`bat_maint_niveau`,`bat_datmaj`,`bat_zus_maj_fk`) VALUES 
 (1,'C1','Confluent Bâtiment 1',NULL,NULL,0,0,NULL,NULL,NULL,NULL,'SANOFI C.C1','2 Avenue Pont Pasteur ','Bâtiment Confluent 1','69007','Lyon','Rhône-Alpes','France',1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (2,'C2','Confluent Bâtiment 2',NULL,NULL,0,0,NULL,NULL,NULL,NULL,'SANOFI C.C2','2 Avenue Pont Pasteur ','Bâtiment Confluent 2','69007','Lyon','Rhône-Alpes','France',1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (3,'C3','Confluent Bâtiment 3',NULL,NULL,0,0,NULL,NULL,NULL,NULL,'SANOFI C.C3','8 Avenue Tony Garnier','Bâtiment Confluent 3','69007','Lyon','Rhône-Alpes','France',1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (4,'TT','Confluent Bâtiment 1, 2 & 3',NULL,NULL,0,0,NULL,NULL,NULL,NULL,'SANOFI C.TT','Gerland','Confluent','69007','Lyon','Rhône-Alpes','France',1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL);


--
-- Definition of table `batiment_attr`
--

CREATE TABLE `batiment_attr` (
  `bat_att_seq` int(16) NOT NULL auto_increment,
  PRIMARY KEY  (`bat_att_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `batiment_attr`
--



--
-- Definition of table `bon_entree_magasin`
--

CREATE TABLE `bon_entree_magasin` (
  `bem_seq` int(11) NOT NULL auto_increment,
  `bem_num` varchar(10) default NULL,
  `bem_date_crea` datetime default NULL,
  `bem_statut` tinyint(3) default NULL,
  `bem_type` tinyint(3) default NULL,
  `bem_libelle` varchar(50) default NULL,
  `bem_dateappro` datetime default NULL,
  `bem_com_fk` int(11) default NULL,
  `bem_four_fk` int(11) default NULL,
  `bem_mag_fk` int(11) default NULL,
  `bem_zus_maj_fk` int(11) default NULL,
  `bem_date_approp` datetime default NULL,
  `bem_zus_crea_fk` int(11) default NULL,
  `bem_zus_valid_fk` int(11) default NULL,
  `bem_datmaj` datetime default NULL,
  `bem_date_valid` datetime default NULL,
  `bem_montant_total` decimal(16,2) default NULL,
  PRIMARY KEY  (`bem_seq`),
  KEY `bem_zus_maj_fk` (`bem_zus_maj_fk`),
  KEY `bem_zus_crea_fk` (`bem_zus_crea_fk`),
  KEY `bem_zus_valid_fk` (`bem_zus_valid_fk`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `bon_entree_magasin`
--



--
-- Definition of table `bon_sortie_magasin`
--

CREATE TABLE `bon_sortie_magasin` (
  `bsm_seq` int(11) NOT NULL auto_increment,
  `bsm_num` varchar(10) default NULL,
  `bsm_date_crea` datetime default NULL,
  `bsm_statut` tinyint(3) default NULL,
  `bsm_type` tinyint(3) default NULL,
  `bsm_libelle` varchar(50) default NULL,
  `bsm_date_valid` datetime default NULL,
  `bsm_montant_total` decimal(16,2) default NULL,
  `bsm_inte_fk` int(11) default NULL,
  `bsm_mag_fk` int(11) default NULL,
  `bsm_date_sortier` datetime default NULL,
  `bsm_trav_fk` int(11) default NULL,
  `bsm_zus_crea_fk` int(11) default NULL,
  `bsm_datmaj` datetime default NULL,
  `bsm_date_sortiep` datetime default NULL,
  `bsm_zus_valid_fk` int(11) default NULL,
  `bsm_zus_maj_fk` int(11) default NULL,
  `bsm_oper_fk` int(11) default NULL,
  PRIMARY KEY  (`bsm_seq`),
  KEY `bsm_zus_maj_fk` (`bsm_zus_maj_fk`),
  KEY `bsm_zus_crea_fk` (`bsm_zus_crea_fk`),
  KEY `bsm_trav_fk` (`bsm_trav_fk`),
  KEY `bsm_oper_fk` (`bsm_oper_fk`),
  KEY `bsm_zus_valid_fk` (`bsm_zus_valid_fk`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `bon_sortie_magasin`
--



--
-- Definition of table `calendrier`
--

CREATE TABLE `calendrier` (
  `cale_seq` int(11) unsigned NOT NULL auto_increment,
  `cale_jour` date NOT NULL default '0000-00-00',
  `cale_nom` varchar(20) NOT NULL,
  PRIMARY KEY  (`cale_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `calendrier`
--



--
-- Definition of table `catalogue`
--

CREATE TABLE `catalogue` (
  `cata_seq` int(11) NOT NULL auto_increment,
  `cata_reference` varchar(15) default NULL,
  `cata_prix` decimal(16,2) default NULL,
  `cata_delai` int(11) default NULL,
  `cata_colisage` int(11) default NULL,
  `cata_datmaj` datetime default NULL,
  `cata_arti_fk` int(11) default NULL,
  `cata_entr_fk` int(11) default NULL,
  `cata_qtepram` int(11) default NULL,
  `cata_zus_maj_fk` int(11) default NULL,
  PRIMARY KEY  (`cata_seq`),
  KEY `cata_arti_fk` (`cata_arti_fk`),
  KEY `cata_entr_fk` (`cata_entr_fk`),
  KEY `cata_zus_maj_fk` (`cata_zus_maj_fk`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `catalogue`
--



--
-- Definition of table `centre_cout`
--

CREATE TABLE `centre_cout` (
  `ceco_seq` int(11) NOT NULL auto_increment,
  `ceco_code` varchar(8) default NULL,
  `ceco_libelle` varchar(20) default NULL,
  PRIMARY KEY  (`ceco_seq`),
  KEY `ceco_code` (`ceco_code`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `centre_cout`
--



--
-- Definition of table `cneh`
--

CREATE TABLE `cneh` (
  `cneh_seq` bigint(11) NOT NULL auto_increment,
  `cneh_code` varchar(6) default NULL,
  `cneh_libelle` varchar(80) default NULL,
  PRIMARY KEY  (`cneh_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `cneh`
--



--
-- Definition of table `communaute`
--

CREATE TABLE `communaute` (
  `comu_seq` int(11) NOT NULL auto_increment,
  `comu_code` varchar(10) default NULL,
  `comu_libelle` varchar(30) default NULL,
  PRIMARY KEY  (`comu_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `communaute`
--



--
-- Definition of table `composant`
--

CREATE TABLE `composant` (
  `comp_seq` int(11) NOT NULL auto_increment,
  `comp_libelle` varchar(45) default NULL,
  `comp_quantite` decimal(16,4) default NULL,
  `comp_code` varchar(20) default NULL,
  `comp_dateconstat` datetime default NULL,
  `comp_datinstal` datetime default NULL,
  `comp_datedebgarant` datetime default NULL,
  `comp_datefingarant` datetime default NULL,
  `comp_annemis` datetime default NULL,
  `comp_ctra_fk` int(11) default NULL,
  `comp_valaneuf` decimal(16,2) default NULL,
  `comp_steq_fk` int(11) default NULL,
  `comp_sant_fk` int(11) default NULL,
  `comp_sat_fk` int(11) default NULL,
  `comp_bat_fk` int(11) default NULL,
  `comp_zone_fk` int(11) default NULL,
  `comp_loca_fk` int(11) default NULL,
  `comp_crit_fk` int(11) default NULL,
  `comp_serv_fk` int(11) default NULL,
  `comp_dom_fk` int(11) default NULL,
  `comp_comt_fk` int(11) default NULL,
  `comp_eqip_fk` int(11) default NULL,
  `comp_entr_fab_fk` int(11) default NULL,
  `comp_entr_inst_fk` int(11) default NULL,
  `comp_entr_four_fk` int(11) default NULL,
  `comp_cont_fab_fk` int(11) default NULL,
  `comp_cont_four_fk` int(11) default NULL,
  `comp_cont_inst_fk` int(11) default NULL,
  `comp_code_barre` varchar(15) default NULL,
  `comp_moco_fk` int(11) default NULL,
  `comp_datmaj` datetime default NULL,
  `comp_zus_maj_fk` int(11) default NULL,
  UNIQUE KEY `comp_seq` (`comp_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `composant`
--



--
-- Definition of table `composant_attr`
--

CREATE TABLE `composant_attr` (
  `comp_att_seq` int(11) NOT NULL auto_increment,
  PRIMARY KEY  (`comp_att_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `composant_attr`
--



--
-- Definition of table `composant_type`
--

CREATE TABLE `composant_type` (
  `comt_seq` int(11) NOT NULL auto_increment,
  `comt_code` varchar(15) default NULL,
  `comt_libelle` varchar(30) default NULL,
  `comt_unite` varchar(5) default NULL,
  `comt_decimale` tinyint(3) unsigned default NULL,
  `comt_duramortis` tinyint(3) unsigned default NULL,
  `comt_dom_fk` int(11) default NULL,
  `comt_datmaj` datetime default NULL,
  `comt_zus_maj_fk` int(11) default NULL,
  PRIMARY KEY  (`comt_seq`),
  KEY `comt_dom_fk` (`comt_dom_fk`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `composant_type`
--



--
-- Definition of table `composant_type_attr`
--

CREATE TABLE `composant_type_attr` (
  `comt_att_seq` int(11) NOT NULL auto_increment,
  PRIMARY KEY  (`comt_att_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `composant_type_attr`
--



--
-- Definition of table `config_salle`
--

CREATE TABLE `config_salle` (
  `cfgs_seq` int(11) NOT NULL auto_increment,
  `cfgs_sreu_fk` int(11) NOT NULL default '0',
  `cfgs_libelle` varchar(12) NOT NULL,
  `cfgs_desc` text NOT NULL,
  `cfgs_capacite` int(11) NOT NULL default '0',
  `cfgs_blocage` tinyint(4) NOT NULL default '0',
  `cfgs_chemin_photo` varchar(100) default NULL,
  `cfgs_pres_fk` int(11) NOT NULL default '0',
  PRIMARY KEY  (`cfgs_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `config_salle`
--



--
-- Definition of table `contact`
--

CREATE TABLE `contact` (
  `cont_seq` int(11) NOT NULL auto_increment,
  `cont_entr_fk` int(11) default NULL,
  `cont_nom` varchar(25) default NULL,
  `cont_teldirect` varchar(18) default NULL,
  `cont_fonction` varchar(40) default NULL,
  `cont_prenom` varchar(25) default NULL,
  `cont_civilite` varchar(5) default NULL,
  `cont_email` varchar(45) default NULL,
  `cont_zus_fk` int(11) default '0',
  `cont_telportable` varchar(18) default NULL,
  `cont_radiomessage` varchar(18) default NULL,
  `cont_telperso` varchar(18) default NULL,
  `cont_datmaj` date default NULL,
  `cont_assist_cont_fk` int(11) default NULL,
  PRIMARY KEY  (`cont_seq`),
  UNIQUE KEY `cont_seq` (`cont_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `contact`
--



--
-- Definition of table `contact_attr`
--

CREATE TABLE `contact_attr` (
  `cont_att_seq` int(11) NOT NULL auto_increment,
  PRIMARY KEY  (`cont_att_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `contact_attr`
--



--
-- Definition of table `contact_gestion`
--

CREATE TABLE `contact_gestion` (
  `cogest_seq` int(11) NOT NULL auto_increment,
  `cogest_eqgest_fk` int(11) NOT NULL default '0',
  `cogest_civilite` varchar(5) default NULL,
  `cogest_nom` varchar(25) default NULL,
  `cogest_prenom` varchar(25) default NULL,
  `cogest_fonction` varchar(60) default NULL,
  `cogest_tel` varchar(18) default NULL,
  `cogest_mail` varchar(45) default NULL,
  PRIMARY KEY  (`cogest_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `contact_gestion`
--



--
-- Definition of table `contrat`
--

CREATE TABLE `contrat` (
  `ctra_seq` int(11) NOT NULL auto_increment,
  `ctra_code` varchar(10) default NULL,
  `ctra_libelle` varchar(50) default NULL,
  `ctra_objet` text,
  `ctra_actif` tinyint(3) unsigned default NULL,
  `ctra_coefheures` decimal(16,2) default NULL,
  `ctra_coeffournit` decimal(16,2) default NULL,
  `ctra_mode_reconduction` varchar(30) default NULL,
  `ctra_date_limite_reconduction` datetime default NULL,
  `ctra_mode_resiliation` varchar(30) default NULL,
  `ctra_date_limite_resiliation` datetime default NULL,
  `ctra_historique` text,
  `ctra_datedebut` datetime default NULL,
  `ctra_datefin` datetime default NULL,
  `ctra_calculavance` tinyint(3) unsigned default NULL,
  `ctra_avancement` tinyint(3) unsigned default NULL,
  `ctra_pcoutglobal` decimal(16,2) default NULL,
  `ctra_rcoutglobal` decimal(16,2) default NULL,
  `ctra_pheure` int(11) default NULL,
  `ctra_pcoutheure` decimal(16,2) default NULL,
  `ctra_pcoutfour` decimal(16,2) default NULL,
  `ctra_pcoutdivers` decimal(16,2) default NULL,
  `ctra_pcoutprev` decimal(16,2) default NULL,
  `ctra_pcoutcor` decimal(16,2) default NULL,
  `ctra_pcoutautre` decimal(16,2) default NULL,
  `ctra_rheure` decimal(16,2) default NULL,
  `ctra_rcoutheure` decimal(16,2) default NULL,
  `ctra_rcoutfour` decimal(16,2) default NULL,
  `ctra_rcoutdivers` decimal(16,2) default NULL,
  `ctra_rcoutcor` decimal(16,2) default NULL,
  `ctra_rcoutautre` decimal(16,2) default NULL,
  `ctra_supe_fk` int(11) default NULL,
  `ctra_entr_client_fk` int(11) default NULL,
  `ctra_cont_client_fk` int(11) default NULL,
  `ctra_entr_four_fk` int(11) default NULL,
  `ctra_cont_four_fk` int(11) default NULL,
  `ctra_comment` text,
  `ctra_crit_fk` int(11) default NULL,
  `ctra_afin_fk` int(11) default NULL,
  `ctra_tppr_fk` int(11) default NULL,
  `ctra_maint_niveau` tinyint(3) unsigned default NULL,
  `ctra_datmaj` datetime default NULL,
  `ctra_zus_maj_fk` int(11) default NULL,
  PRIMARY KEY  (`ctra_seq`),
  KEY `ctra_code` (`ctra_code`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `contrat`
--



--
-- Definition of table `contrat_attr`
--

CREATE TABLE `contrat_attr` (
  `cont_att_seq` int(11) NOT NULL auto_increment,
  PRIMARY KEY  (`cont_att_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `contrat_attr`
--



--
-- Definition of table `criticite`
--

CREATE TABLE `criticite` (
  `crit_seq` int(11) NOT NULL auto_increment,
  `crit_code` varchar(4) default NULL,
  `crit_libelle` varchar(20) default NULL,
  `crit_ordre` tinyint(3) unsigned default NULL,
  PRIMARY KEY  (`crit_seq`),
  KEY `crit_code` (`crit_code`)
) ENGINE=InnoDB AUTO_INCREMENT=4 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `criticite`
--

INSERT INTO `criticite` (`crit_seq`,`crit_code`,`crit_libelle`,`crit_ordre`) VALUES 
 (1,'URG','Urgent',99),
 (2,'NORM','Normal',50),
 (3,'NPRI','Non prioritaire',5);


--
-- Definition of table `csslayout`
--

CREATE TABLE `csslayout` (
  `id` varchar(20) NOT NULL,
  `pageName` varchar(20) NOT NULL,
  `x` int(11) NOT NULL,
  `y` int(11) NOT NULL,
  `width` int(11) NOT NULL,
  `height` int(11) NOT NULL
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `csslayout`
--

INSERT INTO `csslayout` (`id`,`pageName`,`x`,`y`,`width`,`height`) VALUES 
 ('lblSite','gstdi',32,20,50,-1),
 ('lblBatiment','gstdi',211,21,-1,-1),
 ('lblZone','gstdi',477,15,-1,-1),
 ('lblLocal','gstdi',703,21,-1,-1),
 ('siteLibelle','gstdi',75,42,-1,-1),
 ('batLibelle','gstdi',318,44,-1,-1),
 ('zoneLibelle','gstdi',537,47,-1,-1),
 ('localLibelle','gstdi',788,49,-1,-1),
 ('lblEquip','gstdi',634,76,-1,-1),
 ('lblTypeDefaut','gstdi',1,85,-1,-1),
 ('equipLibelle','gstdi',121,118,-1,-1),
 ('defautLibelle','gstdi',468,124,-1,-1),
 ('acSite','gstdi',104,18,-1,-1),
 ('acBatiment','gstdi',287,16,-1,-1),
 ('acZone','gstdi',549,13,-1,-1),
 ('acEquip','gstdi',741,77,-1,-1),
 ('acTypeDef','gstdi',183,78,-1,-1),
 ('acLocal','',786,17,0,0);


--
-- Definition of table `db_champ`
--

CREATE TABLE `db_champ` (
  `dbc_seq` int(11) NOT NULL auto_increment,
  `dbc_attb_fk` int(11) default NULL,
  `dbc_libelle` varchar(32) default NULL,
  `dbc_dbt_fk` int(11) default NULL,
  `dbc_longueur` int(11) default NULL,
  `dbc_part_decimale` int(11) default NULL,
  `dbc_obligatoire` tinyint(3) unsigned default NULL,
  PRIMARY KEY  (`dbc_seq`),
  KEY `dbc_attb_fk` (`dbc_attb_fk`),
  KEY `dbc_dbt_fk` (`dbc_dbt_fk`)
) ENGINE=InnoDB AUTO_INCREMENT=29 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `db_champ`
--

INSERT INTO `db_champ` (`dbc_seq`,`dbc_attb_fk`,`dbc_libelle`,`dbc_dbt_fk`,`dbc_longueur`,`dbc_part_decimale`,`dbc_obligatoire`) VALUES 
 (1,13,'oper_dateinscri',4,NULL,NULL,NULL),
 (2,13,'oper_heureinscri',6,NULL,NULL,NULL),
 (3,13,'oper_dateacquit',4,NULL,NULL,NULL),
 (4,13,'oper_heureacquit',6,NULL,NULL,NULL),
 (5,13,'oper_dateacquitlim',4,NULL,NULL,NULL),
 (6,13,'oper_heureacquitlim',6,NULL,NULL,NULL),
 (7,13,'oper_daterelance',4,NULL,NULL,NULL),
 (8,13,'oper_heurelance',6,NULL,NULL,NULL),
 (9,13,'oper_datedebutp',4,NULL,NULL,NULL),
 (10,13,'oper_heurdebutp',6,NULL,NULL,NULL),
 (11,13,'oper_datedebutr',4,NULL,NULL,NULL),
 (12,13,'oper_heurdebutr',6,NULL,NULL,NULL),
 (13,13,'oper_datedebutrlim',4,NULL,NULL,NULL),
 (14,13,'oper_heurdebutrlim',6,NULL,NULL,NULL),
 (15,13,'oper_datefinp',4,NULL,NULL,NULL),
 (16,13,'oper_heurfinp',6,NULL,NULL,NULL),
 (17,13,'oper_datefinr',4,NULL,NULL,NULL),
 (18,13,'oper_heurfinr',6,NULL,NULL,NULL),
 (19,13,'oper_datefinrlim',4,NULL,NULL,NULL),
 (20,13,'oper_heurfinrlim',6,NULL,NULL,NULL),
 (21,13,'oper_datesup',4,NULL,NULL,NULL),
 (22,13,'oper_dateannul',4,NULL,NULL,NULL),
 (23,13,'oper_dateexport',4,NULL,NULL,NULL),
 (24,13,'oper_datestamp',5,NULL,NULL,NULL),
 (25,13,'oper_datedebutpp',4,NULL,NULL,NULL),
 (26,13,'oper_heurdebutpp',6,NULL,NULL,NULL),
 (27,13,'oper_datefinpp',4,NULL,NULL,NULL),
 (28,13,'oper_heurfinpp',6,NULL,NULL,NULL);


--
-- Definition of table `db_sa_type`
--

CREATE TABLE `db_sa_type` (
  `dbt_seq` int(11) NOT NULL auto_increment,
  `dbt_libelle` varchar(32) default NULL,
  `dbt_presentation` varchar(32) default NULL,
  PRIMARY KEY  (`dbt_seq`)
) ENGINE=InnoDB AUTO_INCREMENT=12 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `db_sa_type`
--

INSERT INTO `db_sa_type` (`dbt_seq`,`dbt_libelle`,`dbt_presentation`) VALUES 
 (1,'Séquentiel',NULL),
 (2,'Booléen',NULL),
 (3,'Caractère',NULL),
 (4,'Date','yyyy-mm-dd'),
 (5,'Date','yyyy-mm-dd hh:mm:ss'),
 (6,'Date','hh:mm:ss'),
 (7,'Date','mm-dd'),
 (8,'Entier court',NULL),
 (9,'Entier long',NULL),
 (10,'Nombre',NULL),
 (11,'Nombre','DecimalPointDeMesure');


--
-- Definition of table `dd_covoiturage`
--

CREATE TABLE `dd_covoiturage` (
  `ddco_seq` int(11) NOT NULL auto_increment,
  `ddco_statut` tinyint(1) default NULL,
  `ddco_alternance` tinyint(1) default NULL,
  `ddco_type_trajet` tinyint(1) default NULL,
  `ddco_sens_trajet` tinyint(1) default NULL,
  `ddco_ptdepart` varchar(50) default NULL,
  `ddco_sat_ptdepart_fk` int(11) default NULL,
  `ddco_ptarrive` varchar(50) default NULL,
  `ddco_sat_ptarrive_fk` int(11) default NULL,
  `ddco_heure_min` time NOT NULL default '00:00:00',
  `ddco_heure_max` time NOT NULL default '00:00:00',
  `ddco_lundi` tinyint(1) default NULL,
  `ddco_mardi` tinyint(1) default NULL,
  `ddco_mercredi` tinyint(1) default NULL,
  `ddco_jeudi` tinyint(1) default NULL,
  `ddco_vendredi` tinyint(1) default NULL,
  `ddco_samedi` tinyint(1) default NULL,
  `ddco_dimanche` tinyint(1) default NULL,
  `ddco_dem_fk` int(11) default NULL,
  `ddco_demandeur` varchar(50) default NULL,
  `ddco_sloc_fk` int(11) default NULL,
  `ddco_telephone` varchar(15) default NULL,
  `ddco_email` varchar(200) default NULL,
  `ddco_commentaire` text,
  `ddco_date_inscri` date NOT NULL default '0000-00-00',
  `ddco_heure_inscri` time NOT NULL default '00:00:00',
  `ddco_date_validite` date NOT NULL default '0000-00-00',
  `ddco_zus_inscri_fk` int(11) default NULL,
  `ddco_ddco_fk` int(11) default NULL,
  `ddco_date_depart` date default NULL,
  `ddco_date_arrive` date default NULL,
  PRIMARY KEY  (`ddco_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_covoiturage`
--



--
-- Definition of table `dd_covoiturage_jumelage`
--

CREATE TABLE `dd_covoiturage_jumelage` (
  `ddcj_seq` int(11) NOT NULL auto_increment,
  `ddcj_dem_fk` int(11) default NULL,
  `ddcj_sloc_fk` int(11) default NULL,
  `ddcj_zus_fk` int(11) default NULL,
  `ddcj_distance` int(11) default NULL,
  `ddcj_frequence_mois` int(11) default NULL,
  `ddcj_frequence_an` int(11) default NULL,
  `ddcj_date_inscri` date default NULL,
  `ddcj_demandeur` varchar(50) default NULL,
  `ddcj_telephone` varchar(15) default NULL,
  `ddcj_email` varchar(200) default NULL,
  PRIMARY KEY  (`ddcj_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_covoiturage_jumelage`
--



--
-- Definition of table `dd_dechet_histo`
--

CREATE TABLE `dd_dechet_histo` (
  `dddh_seq` int(11) NOT NULL auto_increment,
  `dddh_dddr_fk` int(11) default NULL,
  `dddh_action` varchar(25) default NULL,
  `dddh_date` date default NULL,
  `dddh_heure` time default NULL,
  PRIMARY KEY  (`dddh_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_dechet_histo`
--



--
-- Definition of table `dd_dechet_lieucollecte`
--

CREATE TABLE `dd_dechet_lieucollecte` (
  `dddl_seq` int(11) NOT NULL auto_increment,
  `dddl_libelle` varchar(50) default NULL,
  `dddl_unite` varchar(20) default NULL,
  `dddl_nbr_unite` decimal(10,2) default NULL,
  `dddl_sat_fk` int(11) NOT NULL default '0',
  `dddl_code` varchar(9) default NULL,
  PRIMARY KEY  (`dddl_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_dechet_lieucollecte`
--



--
-- Definition of table `dd_dechet_qte`
--

CREATE TABLE `dd_dechet_qte` (
  `dddq_seq` int(11) NOT NULL auto_increment,
  `dddq_dddr_fk` int(11) default NULL,
  `dddq_quantite` decimal(12,4) default NULL,
  `dddq_dddl_fk` int(11) default NULL,
  `dddq_dddt_fk` int(11) default NULL,
  PRIMARY KEY  (`dddq_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_dechet_qte`
--



--
-- Definition of table `dd_dechet_rlv`
--

CREATE TABLE `dd_dechet_rlv` (
  `dddr_seq` int(11) NOT NULL auto_increment,
  `dddr_date_releve` date default NULL,
  `dddr_zus_fk` int(11) NOT NULL default '0',
  PRIMARY KEY  (`dddr_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_dechet_rlv`
--



--
-- Definition of table `dd_dechet_type`
--

CREATE TABLE `dd_dechet_type` (
  `dddt_seq` int(11) NOT NULL auto_increment,
  `dddt_libelle` varchar(50) default NULL,
  `dddt_recyclable` tinyint(1) default NULL,
  `dddt_unite` varchar(20) default NULL,
  `dddt_equivalent_tonne` decimal(5,3) default NULL,
  `dddt_nbr_decimale` tinyint(1) default NULL,
  `dddt_nbr_decimale_par_unite` tinyint(3) default NULL,
  `dddt_code` varchar(9) default NULL,
  PRIMARY KEY  (`dddt_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_dechet_type`
--



--
-- Definition of table `dd_eau_histo`
--

CREATE TABLE `dd_eau_histo` (
  `ddah_seq` int(11) NOT NULL auto_increment,
  `ddah_zus_fk` int(11) NOT NULL default '0',
  `ddah_ddar_fk` int(11) default NULL,
  `ddah_action` varchar(25) default NULL,
  `ddah_date` date default NULL,
  `ddah_heure` time default NULL,
  PRIMARY KEY  (`ddah_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_eau_histo`
--



--
-- Definition of table `dd_eau_mesucomp`
--

CREATE TABLE `dd_eau_mesucomp` (
  `ddam_seq` int(11) NOT NULL auto_increment,
  `ddam_qte_mesu_fk` int(11) NOT NULL default '0',
  `ddam_cost_mesu_fk` int(11) NOT NULL default '0',
  `ddam_ddas_fk` int(11) NOT NULL default '0',
  PRIMARY KEY  (`ddam_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_eau_mesucomp`
--



--
-- Definition of table `dd_eau_qte`
--

CREATE TABLE `dd_eau_qte` (
  `ddaq_seq` int(11) NOT NULL auto_increment,
  `ddaq_ddar_fk` int(11) NOT NULL default '0',
  `ddaq_quantite` decimal(19,4) default NULL,
  `ddaq_ddas_fk` int(11) default NULL,
  `ddaq_cout` decimal(19,4) default NULL,
  `ddaq_quantite_is_update` int(1) default '0',
  `ddaq_cout_is_update` int(1) default '0',
  PRIMARY KEY  (`ddaq_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_eau_qte`
--



--
-- Definition of table `dd_eau_rlv`
--

CREATE TABLE `dd_eau_rlv` (
  `ddar_seq` int(11) NOT NULL auto_increment,
  `ddar_date_releve` date NOT NULL default '0000-00-00',
  `ddar_zus_fk` int(11) default '0',
  PRIMARY KEY  (`ddar_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_eau_rlv`
--



--
-- Definition of table `dd_eau_rlv_sam`
--

CREATE TABLE `dd_eau_rlv_sam` (
  `ddal_seq` int(11) NOT NULL auto_increment,
  `ddal_rele_fk` int(11) NOT NULL default '0',
  `ddal_ddaq_fk` int(11) default NULL,
  `ddal_mesu_fk` int(11) default NULL,
  `ddal_date_rlv` datetime default '0000-00-00 00:00:00',
  `ddal_value_rlv` decimal(19,4) default NULL,
  `ddal_typeoper` char(1) default NULL,
  `ddal_heure_rlv` time default NULL,
  `ddal_comment` varchar(255) default NULL,
  `ddal_inte_fk` int(11) default '0',
  PRIMARY KEY  (`ddal_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_eau_rlv_sam`
--



--
-- Definition of table `dd_eau_secteur`
--

CREATE TABLE `dd_eau_secteur` (
  `ddas_seq` int(11) NOT NULL auto_increment,
  `ddas_sat_fk` int(11) NOT NULL default '0',
  `ddas_libelle` varchar(50) default NULL,
  `ddas_unite` varchar(20) NOT NULL,
  `ddas_nbr_unite` decimal(12,4) default NULL,
  `ddas_code` varchar(9) default NULL,
  PRIMARY KEY  (`ddas_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_eau_secteur`
--



--
-- Definition of table `dd_energie_affectation_usages`
--

CREATE TABLE `dd_energie_affectation_usages` (
  `ddeau_seq` int(11) NOT NULL auto_increment,
  `ddeau_ddel_fk` int(11) default NULL,
  `ddeau_ddet_fk` int(11) default NULL,
  `ddeau_ddeu_fk` int(11) default NULL,
  PRIMARY KEY  (`ddeau_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_affectation_usages`
--



--
-- Definition of table `dd_energie_dju`
--

CREATE TABLE `dd_energie_dju` (
  `ddedju_seq` int(11) NOT NULL auto_increment,
  `ddedju_ddesm_fk` int(11) default NULL,
  `ddedju_annee` int(11) default NULL,
  `ddedju_valeur` int(11) default NULL,
  PRIMARY KEY  (`ddedju_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_dju`
--



--
-- Definition of table `dd_energie_histo`
--

CREATE TABLE `dd_energie_histo` (
  `ddeh_seq` int(11) NOT NULL auto_increment,
  `ddeh_zus_fk` int(11) default NULL,
  `ddeh_dder_fk` int(11) default NULL,
  `ddeh_action` varchar(25) default NULL,
  `ddeh_date` date default NULL,
  `ddeh_heure` time default NULL,
  PRIMARY KEY  (`ddeh_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_histo`
--



--
-- Definition of table `dd_energie_lien_lieux_unite_etalonnage`
--

CREATE TABLE `dd_energie_lien_lieux_unite_etalonnage` (
  `ddellue_seq` int(11) NOT NULL auto_increment,
  `ddellue_ddel_fk` int(11) default NULL,
  `ddellue_ddeue_fk` int(11) default NULL,
  `ddellue_annee` int(11) default NULL,
  `ddellue_mois` int(11) default NULL,
  `ddellue_mesure` decimal(16,2) default NULL,
  PRIMARY KEY  (`ddellue_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_lien_lieux_unite_etalonnage`
--



--
-- Definition of table `dd_energie_lien_modeles_usage`
--

CREATE TABLE `dd_energie_lien_modeles_usage` (
  `ddelmu_seq` int(11) NOT NULL auto_increment,
  `ddelmu_ddeu_fk` int(11) default NULL,
  `ddelmu_ordre` int(11) default NULL,
  `ddelmu_ddeu_fk2` int(11) default NULL,
  PRIMARY KEY  (`ddelmu_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_lien_modeles_usage`
--



--
-- Definition of table `dd_energie_lieux`
--

CREATE TABLE `dd_energie_lieux` (
  `ddel_seq` int(11) NOT NULL auto_increment,
  `ddel_ddel_fk` int(11) default NULL,
  `ddel_code` varchar(10) default NULL,
  `ddel_libelle` varchar(25) default NULL,
  `ddel_niveau` int(11) default NULL,
  `ddel_responsable` varchar(15) default NULL,
  `ddel_mail` varchar(55) default NULL,
  `ddel_entite` varchar(55) default NULL,
  `ddel_ddesm_fk` int(11) default NULL,
  PRIMARY KEY  (`ddel_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_lieux`
--



--
-- Definition of table `dd_energie_mesucomp`
--

CREATE TABLE `dd_energie_mesucomp` (
  `ddem_seq` int(11) NOT NULL auto_increment,
  `ddem_qte_mesu_fk` int(11) NOT NULL default '0',
  `ddem_cost_mesu_fk` int(11) NOT NULL default '0',
  `ddem_ddes_fk` int(11) NOT NULL default '0',
  `ddem_ddet_fk` int(11) NOT NULL default '0',
  PRIMARY KEY  (`ddem_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_mesucomp`
--



--
-- Definition of table `dd_energie_modele_parametre`
--

CREATE TABLE `dd_energie_modele_parametre` (
  `ddemp_seq` int(11) NOT NULL auto_increment,
  `ddemp_ddeu_fk` int(11) default NULL,
  `ddemp_code` varchar(10) default NULL,
  `ddemp_m1` decimal(16,2) default NULL,
  `ddemp_m2` decimal(16,2) default NULL,
  `ddemp_m3` decimal(16,2) default NULL,
  `ddemp_m4` decimal(16,2) default NULL,
  `ddemp_m5` decimal(16,2) default NULL,
  `ddemp_m6` decimal(16,2) default NULL,
  `ddemp_m7` decimal(16,2) default NULL,
  `ddemp_m8` decimal(16,2) default NULL,
  `ddemp_m9` decimal(16,2) default NULL,
  `ddemp_m10` decimal(16,2) default NULL,
  `ddemp_m11` decimal(16,2) default NULL,
  `ddemp_m12` decimal(16,2) default NULL,
  PRIMARY KEY  (`ddemp_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_modele_parametre`
--



--
-- Definition of table `dd_energie_niveaux`
--

CREATE TABLE `dd_energie_niveaux` (
  `dden_seq` int(11) NOT NULL auto_increment,
  `dden_num_niveau` tinyint(3) unsigned default NULL,
  `dden_libelle_niveau1` varchar(10) default NULL,
  `dden_libelle_niveau2` varchar(10) default NULL,
  `dden_libelle_niveau3` varchar(10) default NULL,
  `dden_libelle_niveau4` varchar(10) default NULL,
  PRIMARY KEY  (`dden_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_niveaux`
--



--
-- Definition of table `dd_energie_qte`
--

CREATE TABLE `dd_energie_qte` (
  `ddeq_seq` int(11) NOT NULL auto_increment,
  `ddeq_dder_fk` int(11) NOT NULL default '0',
  `ddeq_quantite` decimal(19,4) default NULL,
  `ddeq_cout` decimal(19,4) default NULL,
  `ddeq_ddes_fk` int(11) default NULL,
  `ddeq_ddet_fk` int(11) default NULL,
  `ddeq_quantite_is_update` int(1) default '0',
  `ddeq_cout_is_update` int(1) default '0',
  PRIMARY KEY  (`ddeq_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_qte`
--



--
-- Definition of table `dd_energie_qte_lisse`
--

CREATE TABLE `dd_energie_qte_lisse` (
  `ddeql_seq` int(11) NOT NULL auto_increment,
  `ddeql_ddeq_fk` int(11) default NULL,
  `ddeql_niveau` int(11) default NULL,
  `ddeql_ddel1_fk` int(11) default NULL,
  `ddeql_ddel2_fk` int(11) default NULL,
  `ddeql_ddel3_fk` int(11) default NULL,
  `ddeql_ddel4_fk` int(11) default NULL,
  `ddeql_ddelf_fk` int(11) default NULL,
  `ddeql_ddet_fk` int(11) default NULL,
  `ddeql_annee` int(11) default NULL,
  `ddeql_mois` int(11) default NULL,
  `ddeql_quantite` decimal(16,4) default NULL,
  `ddeql_cout` decimal(16,4) default NULL,
  `ddeql_jours` int(11) default NULL,
  PRIMARY KEY  (`ddeql_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_qte_lisse`
--



--
-- Definition of table `dd_energie_rlv`
--

CREATE TABLE `dd_energie_rlv` (
  `dder_seq` int(11) NOT NULL auto_increment,
  `dder_date_releve` datetime default NULL,
  `dder_zus_fk` int(11) default NULL,
  PRIMARY KEY  (`dder_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_rlv`
--



--
-- Definition of table `dd_energie_rlv_sam`
--

CREATE TABLE `dd_energie_rlv_sam` (
  `ddel_seq` int(11) NOT NULL auto_increment,
  `ddel_rele_fk` int(11) NOT NULL default '0',
  `ddel_ddeq_fk` int(11) default NULL,
  `ddel_mesu_fk` int(11) default NULL,
  `ddel_date_rlv` datetime default '0000-00-00 00:00:00',
  `ddel_value_rlv` decimal(19,4) default NULL,
  `ddel_typeoper` char(1) default NULL,
  `ddel_heure_rlv` time default NULL,
  `ddel_comment` varchar(255) default NULL,
  `ddel_inte_fk` int(11) default '0',
  PRIMARY KEY  (`ddel_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_rlv_sam`
--



--
-- Definition of table `dd_energie_secteur`
--

CREATE TABLE `dd_energie_secteur` (
  `ddes_seq` int(11) NOT NULL auto_increment,
  `ddes_sat_fk` int(11) NOT NULL default '0',
  `ddes_libelle` varchar(50) default NULL,
  `ddes_unite` varchar(20) NOT NULL,
  `ddes_nbr_unite` decimal(10,2) default NULL,
  `ddes_code` varchar(9) default NULL,
  PRIMARY KEY  (`ddes_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_secteur`
--



--
-- Definition of table `dd_energie_station_meteo`
--

CREATE TABLE `dd_energie_station_meteo` (
  `ddesm_seq` int(11) NOT NULL auto_increment,
  `ddesm_libelle` varchar(20) default NULL,
  `ddesm_reference` tinyint(3) unsigned default NULL,
  PRIMARY KEY  (`ddesm_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_station_meteo`
--



--
-- Definition of table `dd_energie_type`
--

CREATE TABLE `dd_energie_type` (
  `ddet_seq` int(11) NOT NULL auto_increment,
  `ddet_libelle` varchar(50) default NULL,
  `ddet_unite` varchar(30) default NULL,
  `ddet_equivalent_kwh` decimal(8,3) default NULL,
  `ddet_nbr_decimale` tinyint(4) default NULL,
  `ddet_nbr_decimale_par_unite` tinyint(4) default NULL,
  `ddet_type_calcul` tinyint(4) default NULL,
  `ddet_code` varchar(9) default NULL,
  `ddet_renouvelable` tinyint(1) default NULL,
  `ddet_valeur_renouvelable` decimal(4,1) default NULL,
  PRIMARY KEY  (`ddet_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_type`
--



--
-- Definition of table `dd_energie_unite_etalonnage`
--

CREATE TABLE `dd_energie_unite_etalonnage` (
  `ddeue_seq` int(11) NOT NULL auto_increment,
  `ddeue_libelle` varchar(20) default NULL,
  `ddeue_unite` varchar(8) default NULL,
  `ddeue_ordre` int(11) default NULL,
  `ddeue_niveau` int(11) default NULL,
  `ddeue_nature` int(11) default NULL,
  PRIMARY KEY  (`ddeue_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_unite_etalonnage`
--



--
-- Definition of table `dd_energie_usage`
--

CREATE TABLE `dd_energie_usage` (
  `ddeu_seq` int(11) NOT NULL auto_increment,
  `ddeu_code` varchar(10) default NULL,
  `ddeu_libelle` varchar(15) default NULL,
  `ddeu_simple` tinyint(3) unsigned default NULL,
  `ddeu_lie_dju` tinyint(3) unsigned default NULL,
  `ddeu_nbr_decimale` int(11) default NULL,
  `ddeu_nbr_decimale_par_unite` int(11) default NULL,
  PRIMARY KEY  (`ddeu_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_energie_usage`
--



--
-- Definition of table `dd_information`
--

CREATE TABLE `dd_information` (
  `ddin_seq` int(11) NOT NULL auto_increment,
  `ddin_libelle` varchar(80) NOT NULL,
  `ddin_text` text NOT NULL,
  `ddin_image` varchar(100) NOT NULL,
  `ddin_telecharge` varchar(100) NOT NULL,
  `ddin_num_fnct` varchar(10) NOT NULL,
  `ddin_date` date NOT NULL default '0000-00-00',
  `ddin_ordre` int(3) NOT NULL default '0',
  `ddin_ddth_fk` int(11) default NULL,
  PRIMARY KEY  (`ddin_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_information`
--



--
-- Definition of table `dd_lien_utile`
--

CREATE TABLE `dd_lien_utile` (
  `ddlu_seq` int(11) NOT NULL auto_increment,
  `ddlu_libelle` varchar(80) NOT NULL,
  `ddlu_url` varchar(250) NOT NULL,
  `ddlu_date` date NOT NULL default '0000-00-00',
  `ddlu_ordre` int(3) default '0',
  `ddlu_num_fnct` tinyint(1) default NULL,
  PRIMARY KEY  (`ddlu_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_lien_utile`
--



--
-- Definition of table `dd_qualite_lieu`
--

CREATE TABLE `dd_qualite_lieu` (
  `ddql_seq` int(11) NOT NULL auto_increment,
  `ddql_libelle` varchar(30) NOT NULL,
  `ddql_temoin` tinyint(3) default NULL,
  `ddql_sat_fk` int(11) default NULL,
  `ddql_ddqt_fk` int(11) default NULL,
  `ddql_order` tinyint(3) NOT NULL default '0',
  `ddql_ddqtl_fk` int(11) NOT NULL default '0',
  PRIMARY KEY  (`ddql_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_qualite_lieu`
--



--
-- Definition of table `dd_qualite_mesucomp`
--

CREATE TABLE `dd_qualite_mesucomp` (
  `ddqm_seq` int(11) NOT NULL auto_increment,
  `ddqm_mesu_fk` int(11) default '0',
  `ddqm_ddql_fk` int(11) default '0',
  `ddqm_ddqp_fk` int(11) default '0',
  PRIMARY KEY  (`ddqm_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_qualite_mesucomp`
--



--
-- Definition of table `dd_qualite_param_analyse`
--

CREATE TABLE `dd_qualite_param_analyse` (
  `ddqp_seq` int(11) NOT NULL auto_increment,
  `ddqp_libelle` varchar(15) default NULL,
  `ddqp_unite` varchar(8) default NULL,
  `ddqp_seuil` varchar(70) default NULL,
  `ddqp_ddqt_fk` int(11) default NULL,
  `ddqp_nbr_decimale` tinyint(3) default NULL,
  `ddqp_type` int(3) NOT NULL default '0',
  `ddqp_bool0_libelle` varchar(8) default NULL,
  `ddqp_bool1_libelle` varchar(8) default NULL,
  PRIMARY KEY  (`ddqp_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_qualite_param_analyse`
--



--
-- Definition of table `dd_qualite_releve`
--

CREATE TABLE `dd_qualite_releve` (
  `ddqr_seq` int(11) NOT NULL auto_increment,
  `ddqr_valeur` varchar(10) default NULL,
  `ddqr_date_releve` date default NULL,
  `ddqr_ddqp_fk` int(11) default NULL,
  `ddqr_zus_fk` int(11) default NULL,
  `ddqr_ddql_fk` int(11) default NULL,
  `ddqr_param_analyse` tinyint(3) default NULL,
  `ddqr_horaire_releve` varchar(5) default NULL,
  `ddqr_commentaire` varchar(255) default NULL,
  `ddqr_valeur_is_update` tinyint(1) NOT NULL default '0',
  `ddqr_inte_fk` tinyint(3) default NULL,
  `ddqr_appareillage` varchar(15) default NULL,
  PRIMARY KEY  (`ddqr_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_qualite_releve`
--



--
-- Definition of table `dd_qualite_rlv_sam`
--

CREATE TABLE `dd_qualite_rlv_sam` (
  `ddqrs_seq` int(11) NOT NULL auto_increment,
  `ddqrs_rele_fk` int(11) default '0',
  `ddqrs_ddqr_fk` int(11) default '0',
  `ddqrs_mesu_fk` int(11) default '0',
  `ddqrs_inte_fk` int(11) default '0',
  `ddqrs_date_rlv` datetime default '0000-00-00 00:00:00',
  `ddqrs_heure_rlv` time default NULL,
  `ddqrs_valeur_rlv` decimal(19,4) default NULL,
  `ddqrs_typeoper` char(1) default NULL,
  `ddqrs_comment` varchar(255) default NULL,
  `ddqrs_appareillage` varchar(15) default NULL,
  PRIMARY KEY  (`ddqrs_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_qualite_rlv_sam`
--



--
-- Definition of table `dd_qualite_seuil`
--

CREATE TABLE `dd_qualite_seuil` (
  `ddqs_seq` int(11) NOT NULL auto_increment,
  `ddqs_ddqt_fk` int(11) NOT NULL default '0',
  `ddqs_ddqp_fk` int(11) NOT NULL default '0',
  `ddqs_saisonnalite` tinyint(4) NOT NULL default '0',
  `ddqs_date1_debut` varchar(5) default NULL,
  `ddqs_date1_fin` varchar(5) default NULL,
  `ddqs_date2_debut` varchar(5) default NULL,
  `ddqs_date2_fin` varchar(5) default NULL,
  `ddqs_valeur_compar` tinyint(4) NOT NULL default '0',
  `ddqs_valeur_sup` varchar(10) default NULL,
  `ddqs_valeur_inf` varchar(10) default NULL,
  PRIMARY KEY  (`ddqs_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_qualite_seuil`
--



--
-- Definition of table `dd_qualite_theme`
--

CREATE TABLE `dd_qualite_theme` (
  `ddqt_seq` int(11) NOT NULL auto_increment,
  `ddqt_libelle` varchar(30) NOT NULL,
  `ddqt_visible` tinyint(3) default NULL,
  `ddqt_fixe` tinyint(3) default NULL,
  `ddqt_ordre` tinyint(3) default NULL,
  `ddqt_lieux_alea` tinyint(3) NOT NULL default '1',
  `ddqt_indic_horaire` tinyint(3) NOT NULL default '1',
  `ddqt_intervenant` tinyint(3) default NULL,
  `ddqt_appareillage` tinyint(3) default NULL,
  `ddqt_titre_page_1` varchar(70) default NULL,
  `ddqt_logo_page_1` varchar(70) default NULL,
  `ddqt_haut_page_n` varchar(50) default NULL,
  PRIMARY KEY  (`ddqt_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_qualite_theme`
--



--
-- Definition of table `dd_qualite_type_lieu`
--

CREATE TABLE `dd_qualite_type_lieu` (
  `ddqtl_seq` int(11) NOT NULL auto_increment,
  `ddqtl_code` varchar(15) NOT NULL,
  `ddqtl_libelle` varchar(30) NOT NULL,
  PRIMARY KEY  (`ddqtl_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_qualite_type_lieu`
--



--
-- Definition of table `dd_theme`
--

CREATE TABLE `dd_theme` (
  `ddth_seq` int(11) NOT NULL auto_increment,
  `ddth_libelle` varchar(20) default NULL,
  `ddth_ordre` tinyint(3) default NULL,
  PRIMARY KEY  (`ddth_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dd_theme`
--



--
-- Definition of table `demandeur`
--

CREATE TABLE `demandeur` (
  `dem_seq` int(11) NOT NULL auto_increment,
  `dem_serv_fk` int(11) NOT NULL default '0',
  `dem_sat_fk` int(11) default '0',
  `dem_bat_fk` int(11) default '0',
  `dem_zone_fk` int(11) default '0',
  `dem_loca_fk` int(11) default '0',
  `dem_code` varchar(15) NOT NULL,
  `dem_nom` varchar(25) default NULL,
  `dem_prenom` varchar(25) default NULL,
  `dem_civilite` varchar(5) default NULL,
  `dem_fonction` varchar(40) default NULL,
  `dem_teldirect` varchar(15) default NULL,
  `dem_telportable` varchar(15) default NULL,
  `dem_email` varchar(60) default NULL,
  `dem_assist_dem_fk` int(11) default NULL,
  `dem_correspondant` int(11) default NULL,
  `dem_photo` varchar(30) default NULL,
  `dem_blocage` int(11) NOT NULL default '0',
  PRIMARY KEY  (`dem_seq`),
  UNIQUE KEY `dem_seq` (`dem_seq`)
) ENGINE=InnoDB AUTO_INCREMENT=5 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `demandeur`
--

INSERT INTO `demandeur` (`dem_seq`,`dem_serv_fk`,`dem_sat_fk`,`dem_bat_fk`,`dem_zone_fk`,`dem_loca_fk`,`dem_code`,`dem_nom`,`dem_prenom`,`dem_civilite`,`dem_fonction`,`dem_teldirect`,`dem_telportable`,`dem_email`,`dem_assist_dem_fk`,`dem_correspondant`,`dem_photo`,`dem_blocage`) VALUES 
 (1,1,1,1,1,72,'CAMAR','CAMARA','Johann','M',NULL,'0123456789','0123456792','j.camara@sodexo.fr',NULL,NULL,NULL,0),
 (2,2,1,2,0,0,'ANDAL','ANDALOUSSI','Hassan','M',NULL,'0123456790','0123456793','h.andaloussi@sodexo.fr',NULL,NULL,NULL,0),
 (3,3,1,3,0,0,'PAROT','PAROT','Jérémy','M',NULL,'0123456791','0123456794','j.parot@sitealpha.com',NULL,NULL,NULL,0),
 (4,2,1,4,0,0,'CHANU','CHANUT','Laurent','M',NULL,'0123456792','0123456795','l.chanut@sodexo.fr',NULL,NULL,NULL,0);


--
-- Definition of table `demandeur_attr`
--

CREATE TABLE `demandeur_attr` (
  `dem_att_seq` int(11) NOT NULL auto_increment,
  PRIMARY KEY  (`dem_att_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `demandeur_attr`
--



--
-- Definition of table `df_demande_fourniture`
--

CREATE TABLE `df_demande_fourniture` (
  `dfdf_seq` int(11) NOT NULL auto_increment,
  `dfdf_bsm_fk` int(11) NOT NULL default '0',
  `dfdf_bat_fk` int(11) default NULL,
  `dfdf_zone_fk` int(11) default NULL,
  `dfdf_loca_fk` int(11) default NULL,
  `dfdf_sloc_fk` int(11) NOT NULL default '0',
  `dfdf_dem_fk` int(11) default NULL,
  `dfdf_demandeur` varchar(15) default NULL,
  `dfdf_dem_telephone` varchar(15) default NULL,
  `dfdf_dem_email` varchar(45) default NULL,
  PRIMARY KEY  (`dfdf_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `df_demande_fourniture`
--



--
-- Definition of table `df_dotation_consommee_tmp_sfm`
--

CREATE TABLE `df_dotation_consommee_tmp_sfm` (
  `dfdc_seq` int(11) NOT NULL auto_increment,
  `dfdc_dem_fk` int(11) NOT NULL default '0',
  `dfdc_sloc_fk` int(11) NOT NULL default '0',
  `dfdc_dotation_m1` decimal(13,2) default NULL,
  `dfdc_dotation_m2` decimal(13,2) default NULL,
  `dfdc_dotation_m3` decimal(13,2) default NULL,
  `dfdc_dotation_m4` decimal(13,2) default NULL,
  `dfdc_dotation_m5` decimal(13,2) default NULL,
  `dfdc_dotation_m6` decimal(13,2) default NULL,
  `dfdc_dotation_m7` decimal(13,2) default NULL,
  `dfdc_dotation_m8` decimal(13,2) default NULL,
  `dfdc_dotation_m9` decimal(13,2) default NULL,
  `dfdc_dotation_m10` decimal(13,2) default NULL,
  `dfdc_dotation_m11` decimal(13,2) default NULL,
  `dfdc_dotation_m12` decimal(13,2) default NULL,
  `dfdc_nb_demande` int(11) default NULL,
  `dfdc_time` datetime default NULL,
  PRIMARY KEY  (`dfdc_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `df_dotation_consommee_tmp_sfm`
--



--
-- Definition of table `df_lstfourniture_modele`
--

CREATE TABLE `df_lstfourniture_modele` (
  `dflm_seq` int(11) NOT NULL auto_increment,
  `dflm_libelle` varchar(100) default NULL,
  `dflm_zus_fk` int(11) default '0',
  PRIMARY KEY  (`dflm_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `df_lstfourniture_modele`
--



--
-- Definition of table `document`
--

CREATE TABLE `document` (
  `docm_seq` int(11) NOT NULL auto_increment,
  `docm_libelle` varchar(70) default NULL,
  `docm_legende` text,
  `docm_chemin_access` varchar(255) default NULL,
  `docm_date` datetime default NULL,
  `docm_inscrit_par` varchar(5) default NULL,
  `docm_gdct_fk` int(11) default NULL,
  `docm_gdcs_fk` int(11) default NULL,
  `docm_mime_type` varchar(50) default NULL,
  `docm_icone` varchar(50) default NULL,
  `docm_tdoc_fk` int(11) default NULL,
  PRIMARY KEY  (`docm_seq`),
  KEY `docm_gdct_fk` (`docm_gdct_fk`),
  KEY `docm_gdcs_fk` (`docm_gdcs_fk`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `document`
--



--
-- Definition of table `document_attr`
--

CREATE TABLE `document_attr` (
  `docm_att_seq` int(11) NOT NULL auto_increment,
  PRIMARY KEY  (`docm_att_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `document_attr`
--



--
-- Definition of table `documentation`
--

CREATE TABLE `documentation` (
  `docu_seq` int(11) NOT NULL default '0',
  `docu_code` varchar(20) NOT NULL,
  `docu_indice` char(2) default NULL,
  `docu_titre` varchar(60) default NULL,
  `docu_comment` text,
  `docu_dateinit` date default '0000-00-00',
  `docu_datemodif` date default '0000-00-00',
  `docu_auteur` varchar(20) default NULL,
  `docu_chemin` text,
  `docu_echelle` varchar(8) default NULL,
  `docu_format` varchar(8) default NULL,
  `docu_etablipar` varchar(10) default NULL,
  `docu_modif` varchar(30) default NULL,
  `docu_rub1` varchar(50) default NULL,
  `docu_rub2` varchar(20) default NULL,
  `docu_rub3` varchar(20) default NULL,
  `docu_tdoc_code` varchar(8) NOT NULL,
  `docu_tdoc_libelle` varchar(15) NOT NULL,
  PRIMARY KEY  (`docu_seq`),
  UNIQUE KEY `DOCU_SEQ` (`docu_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `documentation`
--



--
-- Definition of table `dol_sous_theme`
--

CREATE TABLE `dol_sous_theme` (
  `dols_seq` int(11) NOT NULL auto_increment,
  `dols_dolt_fk` int(11) NOT NULL default '0',
  `dols_libelle` varchar(20) NOT NULL,
  `dols_ordre` int(3) default NULL,
  PRIMARY KEY  (`dols_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dol_sous_theme`
--



--
-- Definition of table `dol_theme`
--

CREATE TABLE `dol_theme` (
  `dolt_seq` int(11) NOT NULL auto_increment,
  `dolt_libelle` varchar(50) default NULL,
  `dolt_image` varchar(150) default NULL,
  `dolt_ordre` tinyint(3) unsigned default NULL,
  PRIMARY KEY  (`dolt_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `dol_theme`
--



--
-- Definition of table `domaine`
--

CREATE TABLE `domaine` (
  `dom_seq` int(11) NOT NULL auto_increment,
  `dom_code` varchar(6) NOT NULL,
  `dom_libelle` varchar(30) NOT NULL,
  `dom_sdom_fk` int(11) default NULL,
  `dom_bool_inactive` tinyint(3) unsigned default '0',
  `dom_totaliser` tinyint(3) unsigned default NULL,
  `dom_unite` varchar(5) default NULL,
  `dom_decimale` tinyint(3) unsigned default NULL,
  `dom_ordre` tinyint(3) unsigned default NULL,
  `dom_bdocument` tinyint(3) unsigned default NULL,
  `dom_afin_fk` int(11) default NULL,
  `dom_crit_fk` int(11) default NULL,
  `dom_form_fk` int(11) default NULL,
  `dom_ctra_fk` int(11) default NULL,
  `dom_communaute` tinyint(3) default NULL,
  `dom_datmaj` datetime default NULL,
  `dom_zus_maj_fk` int(11) default NULL,
  PRIMARY KEY  (`dom_seq`),
  UNIQUE KEY `DOM_SEQ` (`dom_seq`),
  KEY `DOM_CODE` (`dom_code`),
  KEY `DOM_AFIN_FK` (`dom_afin_fk`),
  KEY `dom_crit_fk` (`dom_crit_fk`),
  KEY `dom_crit_fk_2` (`dom_crit_fk`)
) ENGINE=InnoDB AUTO_INCREMENT=11 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `domaine`
--

INSERT INTO `domaine` (`dom_seq`,`dom_code`,`dom_libelle`,`dom_sdom_fk`,`dom_bool_inactive`,`dom_totaliser`,`dom_unite`,`dom_decimale`,`dom_ordre`,`dom_bdocument`,`dom_afin_fk`,`dom_crit_fk`,`dom_form_fk`,`dom_ctra_fk`,`dom_communaute`,`dom_datmaj`,`dom_zus_maj_fk`) VALUES 
 (1,'CFA','Electricité - Courants faible',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (2,'CFO','Electricité - Courants forts',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (3,'CVCD','Chauf - Ventil - Clim - Desenf',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (4,'LEVA','Levage',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (5,'2ND','Second Œuvre',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (6,'PLOM','Plomberie',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (7,'SINC','Sécurité Incendie',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (8,'PAU','Portes automatiques',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (9,'MATCUI','Matériel de cuisine',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (10,'DIV','Divers',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL);


--
-- Definition of table `domaine_attr`
--

CREATE TABLE `domaine_attr` (
  `dom_att_seq` int(16) NOT NULL default '0',
  PRIMARY KEY  (`dom_att_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `domaine_attr`
--



--
-- Definition of table `domaine_frequence`
--

CREATE TABLE `domaine_frequence` (
  `dofr_seq` int(11) NOT NULL auto_increment,
  `dofr_frequence` int(11) default NULL,
  `dofr_dom_fk` int(11) NOT NULL default '0',
  `dofr_zus_fk` int(11) NOT NULL default '0',
  PRIMARY KEY  (`dofr_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `domaine_frequence`
--



--
-- Definition of table `domaine_mlg`
--

CREATE TABLE `domaine_mlg` (
  `dom_mlg_seq` int(11) NOT NULL default '0',
  `dom_mlg_libelle` varchar(30) default NULL,
  PRIMARY KEY  (`dom_mlg_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `domaine_mlg`
--



--
-- Definition of table `enquete`
--

CREATE TABLE `enquete` (
  `enqu_seq` int(11) NOT NULL auto_increment,
  `enqu_libelle` varchar(200) NOT NULL,
  `enqu_destinataire` tinyint(2) default NULL,
  `enqu_adresse_fixe` varchar(255) default NULL,
  `enqu_systematique` tinyint(1) default NULL,
  `enqu_pourcentage` tinyint(2) default NULL,
  `enqu_format_mail` varchar(50) default NULL,
  `enqu_avec_filtre` tinyint(1) default '0',
  `enqu_filtre` text,
  `enqu_date_debut` date NOT NULL default '0000-00-00',
  `enqu_date_fin` date NOT NULL default '0000-00-00',
  `enqu_nb_envoie` int(5) default '0',
  `enqu_date_dernier_envoie` date default NULL,
  `enqu_module_id` int(11) NOT NULL default '0',
  PRIMARY KEY  (`enqu_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `enquete`
--



--
-- Definition of table `enquete_donnee`
--

CREATE TABLE `enquete_donnee` (
  `enqd_seq` int(11) NOT NULL auto_increment,
  `enqd_enqu_fk` int(11) NOT NULL default '0',
  `enqd_date_envoie` date NOT NULL default '0000-00-00',
  `enqd_date_retour` date default NULL,
  `enqd_nom_destinataire` varchar(100) default NULL,
  `enqd_mail_destinataire` varchar(100) default NULL,
  `enqd_oper_fk` int(11) NOT NULL default '0',
  `enqd_trav_fk` int(11) default NULL,
  `enqd_commentaire` text,
  PRIMARY KEY  (`enqd_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `enquete_donnee`
--



--
-- Definition of table `enquete_question`
--

CREATE TABLE `enquete_question` (
  `enqq_seq` int(11) NOT NULL auto_increment,
  `enqq_enqu_fk` int(11) NOT NULL default '0',
  `enqq_libelle` text NOT NULL,
  `enqq_ordre` int(3) default NULL,
  PRIMARY KEY  (`enqq_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `enquete_question`
--



--
-- Definition of table `enquete_question_mlg`
--

CREATE TABLE `enquete_question_mlg` (
  `enqq_mlg_seq` int(11) NOT NULL default '0',
  `enqq_mlg_libelle` text NOT NULL,
  PRIMARY KEY  (`enqq_mlg_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `enquete_question_mlg`
--



--
-- Definition of table `enquete_reponse`
--

CREATE TABLE `enquete_reponse` (
  `enqr_seq` int(11) NOT NULL auto_increment,
  `enqr_enqd_fk` int(11) NOT NULL default '0',
  `enqr_enqq_fk` int(11) NOT NULL default '0',
  `enqr_reponse` tinyint(1) NOT NULL default '0',
  PRIMARY KEY  (`enqr_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `enquete_reponse`
--



--
-- Definition of table `entreprise`
--

CREATE TABLE `entreprise` (
  `entr_seq` int(11) NOT NULL auto_increment,
  `entr_code` varchar(15) default NULL,
  `entr_libelle` varchar(40) default NULL,
  `entr_estfournisseur` tinyint(3) unsigned default NULL,
  `entr_estconstructeur` tinyint(3) unsigned default NULL,
  `entr_estmainteneur` tinyint(3) unsigned default NULL,
  `entr_estinstallateur` tinyint(3) unsigned default NULL,
  `entr_estsav` tinyint(3) unsigned default NULL,
  `entr_adr1` varchar(35) default NULL,
  `entr_adr2` varchar(35) default NULL,
  `entr_adr3` varchar(35) default NULL,
  `entr_cp` varchar(6) default NULL,
  `entr_ville` varchar(25) default NULL,
  `entr_telephone` varchar(15) default NULL,
  `entr_telecopie` varchar(15) default NULL,
  `entr_region` varchar(25) default NULL,
  `entr_pays` varchar(25) default NULL,
  `entr_datmaj` date default NULL,
  `entr_email` varchar(45) default NULL,
  `entr_website` varchar(45) default NULL,
  `entr_spec_fk` int(11) default NULL,
  `entr_dansstock` tinyint(3) unsigned default NULL,
  PRIMARY KEY  (`entr_seq`),
  KEY `entr_code` (`entr_code`),
  KEY `entr_libelle` (`entr_libelle`),
  KEY `entr_ville` (`entr_ville`),
  KEY `entr_spec_fk` (`entr_spec_fk`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `entreprise`
--



--
-- Definition of table `entreprise_attr`
--

CREATE TABLE `entreprise_attr` (
  `entr_att_seq` int(16) NOT NULL auto_increment,
  PRIMARY KEY  (`entr_att_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `entreprise_attr`
--



--
-- Definition of table `equipe_gestion`
--

CREATE TABLE `equipe_gestion` (
  `eqgest_seq` int(11) NOT NULL auto_increment,
  `eqgest_nom` varchar(80) NOT NULL,
  `eqgest_text` text NOT NULL,
  PRIMARY KEY  (`eqgest_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `equipe_gestion`
--



--
-- Definition of table `equipe_travaux`
--

CREATE TABLE `equipe_travaux` (
  `trav_seq` int(11) NOT NULL auto_increment,
  `trav_code` varchar(6) default NULL,
  `trav_libelle` varchar(25) default NULL,
  `trav_boolintern` tinyint(3) unsigned default NULL,
  `trav_couthoraire` decimal(16,2) default NULL,
  `trav_lundi` tinyint(3) unsigned default NULL,
  `trav_mardi` tinyint(3) unsigned default NULL,
  `trav_mercredi` tinyint(3) unsigned default NULL,
  `trav_jeudi` tinyint(3) unsigned default NULL,
  `trav_vendredi` tinyint(3) unsigned default NULL,
  `trav_samedi` tinyint(3) unsigned default NULL,
  `trav_dimanche` tinyint(3) unsigned default NULL,
  `trav_feries` tinyint(3) unsigned default NULL,
  `trav_controle` tinyint(3) unsigned default NULL,
  `trav_couthoraire2` decimal(16,2) default NULL,
  `trav_supe_fk` int(11) default NULL,
  `trav_numappel1` varchar(15) default NULL,
  `trav_typbip` tinyint(3) unsigned default NULL,
  `trav_heuresem` decimal(16,2) default NULL,
  `trav_datmaj` datetime default NULL,
  `trav_numappel2` varchar(15) default NULL,
  `trav_numappel3` varchar(15) default NULL,
  `trav_numappel4` varchar(15) default NULL,
  `trav_numappel_info` varchar(15) default NULL,
  `trav_email` varchar(45) default NULL,
  `trav_connex_palm` tinyint(3) unsigned default NULL,
  `trav_palm_id` varchar(10) default NULL,
  `trav_age_fk` int(11) default NULL,
  `trav_numfax` varchar(15) default NULL,
  `trav_actif` tinyint(3) unsigned default NULL,
  `trav_entr_fk` int(11) default NULL,
  `trav_pot_lundi` decimal(16,2) default NULL,
  `trav_pot_mardi` decimal(16,2) default NULL,
  `trav_pot_mercredi` decimal(16,2) default NULL,
  `trav_pot_jeudi` decimal(16,2) default NULL,
  `trav_pot_vendredi` decimal(16,2) default NULL,
  `trav_pot_samedi` decimal(16,2) default NULL,
  `trav_pot_dimanche` decimal(16,2) default NULL,
  `trav_modpotentiel` tinyint(3) unsigned default NULL,
  `trav_cont_fk` int(11) default NULL,
  `trav_connex_crmail` tinyint(3) unsigned default NULL,
  `trav_zus_maj_fk` int(11) default NULL,
  `trav_pda_1_fk` int(11) default NULL,
  `trav_pda_2_fk` int(11) default NULL,
  `trav_pda_3_fk` int(11) default NULL,
  `trav_pda_4_fk` int(11) default NULL,
  `trav_delai1` int(11) default NULL,
  `trav_delai2` int(11) default NULL,
  `trav_delai3` int(11) default NULL,
  `trav_delai4` int(11) default NULL,
  `trav_chgt_eq2` tinyint(3) unsigned default NULL,
  `trav_chgt_eq3` tinyint(3) unsigned default NULL,
  `trav_chgt_eq4` tinyint(3) unsigned default NULL,
  `trav_trav_nouv2_fk` int(11) default NULL,
  `trav_trav_nouv3_fk` int(11) default NULL,
  `trav_trav_nouv4_fk` int(11) default NULL,
  PRIMARY KEY  (`trav_seq`),
  KEY `trav_code` (`trav_code`),
  KEY `trav_libelle` (`trav_libelle`),
  KEY `trav_boolintern` (`trav_boolintern`),
  KEY `trav_supe_fk` (`trav_supe_fk`),
  KEY `trav_age_fk` (`trav_age_fk`),
  KEY `trav_entr_fk` (`trav_entr_fk`),
  KEY `trav_cont_fk` (`trav_cont_fk`),
  KEY `trav_pda_1_fk` (`trav_pda_1_fk`),
  KEY `trav_pda_2_fk` (`trav_pda_2_fk`),
  KEY `trav_pda_3_fk` (`trav_pda_3_fk`),
  KEY `trav_pda_4_fk` (`trav_pda_4_fk`),
  KEY `trav_trav_nouv2_fk` (`trav_trav_nouv2_fk`),
  KEY `trav_trav_nouv3_fk` (`trav_trav_nouv3_fk`),
  KEY `trav_trav_nouv4_fk` (`trav_trav_nouv4_fk`)
) ENGINE=InnoDB AUTO_INCREMENT=5 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `equipe_travaux`
--

INSERT INTO `equipe_travaux` (`trav_seq`,`trav_code`,`trav_libelle`,`trav_boolintern`,`trav_couthoraire`,`trav_lundi`,`trav_mardi`,`trav_mercredi`,`trav_jeudi`,`trav_vendredi`,`trav_samedi`,`trav_dimanche`,`trav_feries`,`trav_controle`,`trav_couthoraire2`,`trav_supe_fk`,`trav_numappel1`,`trav_typbip`,`trav_heuresem`,`trav_datmaj`,`trav_numappel2`,`trav_numappel3`,`trav_numappel4`,`trav_numappel_info`,`trav_email`,`trav_connex_palm`,`trav_palm_id`,`trav_age_fk`,`trav_numfax`,`trav_actif`,`trav_entr_fk`,`trav_pot_lundi`,`trav_pot_mardi`,`trav_pot_mercredi`,`trav_pot_jeudi`,`trav_pot_vendredi`,`trav_pot_samedi`,`trav_pot_dimanche`,`trav_modpotentiel`,`trav_cont_fk`,`trav_connex_crmail`,`trav_zus_maj_fk`,`trav_pda_1_fk`,`trav_pda_2_fk`,`trav_pda_3_fk`,`trav_pda_4_fk`,`trav_delai1`,`trav_delai2`,`trav_delai3`,`trav_delai4`,`trav_chgt_eq2`,`trav_chgt_eq3`,`trav_chgt_eq4`,`trav_trav_nouv2_fk`,`trav_trav_nouv3_fk`,`trav_trav_nouv4_fk`) VALUES 
 (1,'AGIN','Agent Interne',0,NULL,1,1,1,1,1,0,0,0,NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (2,'EQIN','Equipe Interne',0,NULL,1,1,1,1,1,0,0,0,NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (3,'SOEX','Société Externe',1,NULL,1,1,1,1,1,0,0,0,NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (4,'MIXT','Equipe Mixte Int/Ext',0,NULL,1,1,1,1,1,0,0,0,NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL);


--
-- Definition of table `equipe_travaux_attr`
--

CREATE TABLE `equipe_travaux_attr` (
  `trav_att_seq` int(16) NOT NULL auto_increment,
  PRIMARY KEY  (`trav_att_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `equipe_travaux_attr`
--



--
-- Definition of table `equipement`
--

CREATE TABLE `equipement` (
  `eqip_seq` int(11) NOT NULL auto_increment,
  `eqip_code` varchar(20) default NULL,
  `eqip_libelle` varchar(45) default NULL,
  `eqip_type` tinyint(3) unsigned default NULL,
  `eqip_niveau` tinyint(3) unsigned default NULL,
  `eqip_datinstal` date default NULL,
  `eqip_datedebgarant` date default NULL,
  `eqip_datefingarant` date default NULL,
  `eqip_dureegarant` int(11) default NULL,
  `eqip_infocomp` text,
  `eqip_dateconstat` date default NULL,
  `eqip_quantite` int(16) default NULL,
  `eqip_unite` varchar(4) default NULL,
  `eqip_bdocument` tinyint(3) unsigned default NULL,
  `eqip_valaneuf` decimal(16,2) default NULL,
  `eqip_valaneuf2` decimal(16,2) default NULL,
  `eqip_sat_fk` int(11) default NULL,
  `eqip_bat_fk` int(11) default NULL,
  `eqip_dom_fk` int(11) default NULL,
  `eqip_loca_fk` int(11) default NULL,
  `eqip_zone_fk` int(11) default NULL,
  `eqip_trav_fk` int(11) default NULL,
  `eqip_sant_fk` int(11) default NULL,
  `eqip_fame_fk` int(11) default NULL,
  `eqip_four_entr_fk` int(11) default NULL,
  `eqip_fab_entr_fk` int(11) default NULL,
  `eqip_inst_entr_fk` int(11) default NULL,
  `eqip_maint_entr_fk` int(11) default NULL,
  `eqip_sav_entr_fk` int(11) default NULL,
  `eqip_four_cont_fk` int(11) default NULL,
  `eqip_fab_cont_fk` int(11) default NULL,
  `eqip_inst_cont_fk` int(11) default NULL,
  `eqip_maint_cont_fk` int(11) default NULL,
  `eqip_sav_cont_fk` int(11) default NULL,
  `eqip_stde_fk` int(11) default NULL,
  `eqip_codeconca` varchar(27) default NULL,
  `eqip_code_barre` varchar(15) default NULL,
  `eqip_cdbr_fk` int(11) default NULL,
  `eqip_steq_fk` int(11) default NULL,
  `eqip_crit_fk` int(11) default NULL,
  `eqip_ceco_fk` int(11) default NULL,
  `eqip_serv_fk` int(11) default NULL,
  `eqip_dateachat` date default NULL,
  `eqip_datemisexpl` date default NULL,
  `eqip_consiparti` text,
  `eqip_numserie` varchar(80) default NULL,
  `eqip_afin_fk` int(11) default NULL,
  `eqip_ctra_fk` int(11) default NULL,
  `eqip_proj_fk` int(11) default NULL,
  `eqip_inte_fk` int(11) default NULL,
  `eqip_supe_fk` int(11) default NULL,
  `eqip_cneh` varchar(6) default NULL,
  `eqip_communaute` tinyint(3) default NULL,
  `eqip_moeq_fk` int(11) default NULL,
  `eqip_eqip_pere_fk` int(11) default NULL,
  `eqip_codeconca_decomp` varchar(255) default NULL,
  `eqip_datmaj` datetime default NULL,
  `eqip_zus_maj_fk` int(11) default NULL,
  PRIMARY KEY  (`eqip_seq`),
  KEY `eqip_code` (`eqip_code`),
  KEY `eqip_libelle` (`eqip_libelle`),
  KEY `eqip_bat_fk` (`eqip_bat_fk`),
  KEY `eqip_dom_fk` (`eqip_dom_fk`),
  KEY `eqip_loca_fk` (`eqip_loca_fk`),
  KEY `eqip_zone_fk` (`eqip_zone_fk`),
  KEY `eqip_trav_fk` (`eqip_trav_fk`),
  KEY `eqip_sant_fk` (`eqip_sant_fk`),
  KEY `eqip_fame_fk` (`eqip_fame_fk`),
  KEY `eqip_four_entr_fk` (`eqip_four_entr_fk`),
  KEY `eqip_fab_entr_fk` (`eqip_fab_entr_fk`),
  KEY `eqip_inst_entr_fk` (`eqip_inst_entr_fk`),
  KEY `eqip_maint_entr_fk` (`eqip_maint_entr_fk`),
  KEY `eqip_sav_entr_fk` (`eqip_sav_entr_fk`),
  KEY `eqip_four_cont_fk` (`eqip_four_cont_fk`),
  KEY `eqip_fab_cont_fk` (`eqip_fab_cont_fk`),
  KEY `eqip_inst_cont_fk` (`eqip_inst_cont_fk`),
  KEY `eqip_maint_cont_fk` (`eqip_maint_cont_fk`),
  KEY `eqip_sav_cont_fk` (`eqip_sav_cont_fk`),
  KEY `eqip_cdbr_fk` (`eqip_cdbr_fk`),
  KEY `eqip_steq_fk` (`eqip_steq_fk`),
  KEY `eqip_crit_fk` (`eqip_crit_fk`),
  KEY `eqip_ceco_fk` (`eqip_ceco_fk`),
  KEY `eqip_serv_fk` (`eqip_serv_fk`),
  KEY `eqip_afin_fk` (`eqip_afin_fk`)
) ENGINE=InnoDB AUTO_INCREMENT=193 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `equipement`
--

INSERT INTO `equipement` (`eqip_seq`,`eqip_code`,`eqip_libelle`,`eqip_type`,`eqip_niveau`,`eqip_datinstal`,`eqip_datedebgarant`,`eqip_datefingarant`,`eqip_dureegarant`,`eqip_infocomp`,`eqip_dateconstat`,`eqip_quantite`,`eqip_unite`,`eqip_bdocument`,`eqip_valaneuf`,`eqip_valaneuf2`,`eqip_sat_fk`,`eqip_bat_fk`,`eqip_dom_fk`,`eqip_loca_fk`,`eqip_zone_fk`,`eqip_trav_fk`,`eqip_sant_fk`,`eqip_fame_fk`,`eqip_four_entr_fk`,`eqip_fab_entr_fk`,`eqip_inst_entr_fk`,`eqip_maint_entr_fk`,`eqip_sav_entr_fk`,`eqip_four_cont_fk`,`eqip_fab_cont_fk`,`eqip_inst_cont_fk`,`eqip_maint_cont_fk`,`eqip_sav_cont_fk`,`eqip_stde_fk`,`eqip_codeconca`,`eqip_code_barre`,`eqip_cdbr_fk`,`eqip_steq_fk`,`eqip_crit_fk`,`eqip_ceco_fk`,`eqip_serv_fk`,`eqip_dateachat`,`eqip_datemisexpl`,`eqip_consiparti`,`eqip_numserie`,`eqip_afin_fk`,`eqip_ctra_fk`,`eqip_proj_fk`,`eqip_inte_fk`,`eqip_supe_fk`,`eqip_cneh`,`eqip_communaute`,`eqip_moeq_fk`,`eqip_eqip_pere_fk`,`eqip_codeconca_decomp`,`eqip_datmaj`,`eqip_zus_maj_fk`) VALUES 
 (1,'ADO C1','Adoucisseur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,5,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.ADO C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (2,'ACA OND A','Armoire de climatisation autonome',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.ACA OND A',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (3,'ACA OND B','Armoire de climatisation autonome',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.ACA OND B',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (4,'ACA INFO1','Armoire de climatisation autonome',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.ACA INFO1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (5,'ACA INFO2','Armoire de climatisation autonome',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.ACA INFO2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (6,'ACA INFO 3','Armoire de climatisation autonome',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.ACA INFO 3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (7,'ACA INFO4','Armoire de climatisation autonome',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.ACA INFO4',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (8,'ACA OND C2','Armoire de climatisation autonome',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.ACA OND C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (9,'ACA C3','Armoire de climatisation autonome',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.ACA C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (10,'ARM C1','Armoire électrotechnique',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,2,NULL,NULL,1,1,11,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.ARM C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (11,'ARM PCS','Armoire électrotechnique',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,1,2,NULL,NULL,1,1,11,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.ARM PCS',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (12,'ARM C2','Armoire électrotechnique',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,2,NULL,NULL,1,1,11,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.ARM C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (13,'ARM C3','Armoire électrotechnique',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,2,NULL,NULL,1,1,11,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.ARM C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (14,'ARM HT C2','Armoire électrotechnique',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,2,2,NULL,NULL,1,1,11,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.ARM HT C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (15,'ASC 7N','Ascenseur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,4,NULL,NULL,1,1,12,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.ASC 7N',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (16,'ASC N7 C2','Ascenseur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,4,NULL,NULL,1,1,12,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.ASC N7 C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (17,'MC 7N','Ascenseur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,4,NULL,NULL,1,1,12,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.MC 7N',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (18,'MC C2N7','Ascenseur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,4,NULL,NULL,1,1,12,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.MC C2N7',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (19,'ASC  C3','Ascenseur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,3,4,NULL,NULL,1,1,12,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.ASC  C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (20,'ASC 8N','Ascenseur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,1,4,NULL,NULL,1,1,12,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.ASC 8N',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (21,'MC C3','Ascenseur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,4,NULL,NULL,1,1,12,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.MC C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (22,'ASC N9C2','Ascenseur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,4,NULL,NULL,1,1,12,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.ASC N9C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (23,'MC 8N','Ascenseur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,4,NULL,NULL,1,1,12,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.MC 8N',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (24,'BAG C1','Bac à graisse',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,15,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.BAG C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (25,'BEC C2','Ballon d\'eau chaude sanitaire',0,1,NULL,NULL,NULL,NULL,NULL,NULL,12,NULL,NULL,NULL,NULL,1,2,6,NULL,NULL,1,1,20,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.BEC C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (26,'BEC C1','Ballon d\'eau chaude sanitaire',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,20,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.BEC C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (27,'BEC C3','Ballon d\'eau chaude sanitaire',0,1,NULL,NULL,NULL,NULL,NULL,NULL,9,NULL,NULL,NULL,NULL,1,3,6,NULL,NULL,1,1,20,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.BEC C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (28,'BEL C2','Ballon d\'eau chaude sanitaire (Prod locale)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,25,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,23,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.BEL C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (29,'BEL C1','Ballon d\'eau chaude sanitaire (Prod locale)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,40,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,23,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.BEL C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (30,'BAR C1','Barrière automatique parking',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,1,8,NULL,NULL,1,1,17,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.BAR C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (31,'BAU C3','Bloc autonome d\'éclairage de sécurité',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,2,NULL,NULL,1,1,18,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.BAU C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (32,'BAU C2','Bloc autonome d\'éclairage de sécurité',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,2,NULL,NULL,1,1,18,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.BAU C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (33,'BAU C1','Bloc autonome d\'éclairage de sécurité',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,2,NULL,NULL,1,1,18,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.BAU C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (34,'SAN C1','Bloc sanitaire',0,1,NULL,NULL,NULL,NULL,NULL,NULL,20,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,112,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.SAN C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (35,'SAN C2','Bloc sanitaire',0,1,NULL,NULL,NULL,NULL,NULL,NULL,20,NULL,NULL,NULL,NULL,1,2,6,NULL,NULL,1,1,112,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.SAN C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (36,'SAN C3','Bloc sanitaire',0,1,NULL,NULL,NULL,NULL,NULL,NULL,12,NULL,NULL,NULL,NULL,1,3,6,NULL,NULL,1,1,112,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.SAN C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (37,'CAS 1 C3','Cassette plafonnière',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,3,3,NULL,NULL,1,1,29,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.CAS 1 C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (38,'CAS 2 C3','Cassette plafonnière',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,29,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.CAS 2 C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (39,'CAS 3 C2','Cassette plafonnière  des bureaux',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,29,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.CAS 3 C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (40,'CAS 1 C2','Cassette plafonnière office/ z livraison',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,29,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.CAS 1 C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (41,'CAS 2 C2','Cassette plafonnière s réunion/foyer/hall',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,29,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.CAS 2 C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (42,'CEL C3','Cellule haute tension',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,2,NULL,NULL,1,1,32,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.CEL C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (43,'CEL C1','Cellule haute tension',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,2,NULL,NULL,1,1,32,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.CEL C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (44,'CEL C2','Cellule haute tension',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,2,2,NULL,NULL,1,1,32,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.CEL C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (45,'CTA C3','Centrale de traitement d\'air',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.CTA C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (46,'CTA CAF C3','Centrale de traitement d\'air',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.CTA CAF C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (47,'CTA 2 C2','Centrale de traitement d\'air',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.CTA 2 C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (48,'CTA 3 C2','CTA  Aile B et Atrium (CTA 3)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.CTA 3 C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (49,'CTA AMPHC2','Centrale de traitement d\'air (Amphithéâtre)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.CTA AMPHC2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (50,'CTA ATR C2','Centrale de traitement d\'air (CTA Atrium)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.CTA ATR C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (51,'CTA A','Centrale de traitement d\'air A,AN,Atrium',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.CTA A',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (52,'CTA 2/3 C2','CTA  Aile A + Aile B + Atrium (CTA 2/3)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.CTA 2/3 C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (53,'CTA ATR N6','Centrale de traitement d\'air atrium 6',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.CTA ATR N6',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (54,'CTA ATR N1','Centrale de traitement d\'air atrium Niv 1',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.CTA ATR N1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (55,'CTA ATR N2','Centrale de traitement d\'air atrium Niv 2',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.CTA ATR N2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (56,'CRA ATR N3','Centrale de traitement d\'air atrium Niv 3',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.CRA ATR N3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (57,'CTA ATR N4','Centrale de traitement d\'air atrium Niv 4',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.CTA ATR N4',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (58,'CTA ATR N5','Centrale de traitement d\'air atrium Niv 5',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.CTA ATR N5',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (59,'CTA EX B','Centrale de traitement d\'air extraction Bat B',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.CTA EX B',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (60,'CTA EX RIE','CTA extraction Restaurent',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.CTA EX RIE',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (61,'CTA RIE','CTA restaurent ,cuisine,scramble',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.CTA RIE',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (62,'CTA SC','Centrale de traitement d\'air Salle de conseil',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.CTA SC',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (63,'CTA 4 C2','CTA salle de réunion (CTA 4)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.CTA 4 C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (64,'CTA B','Centrale de traitement d\'air soufflage bat B',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.CTA B',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (65,'CTA C','Centrale de traitement d\'air soufflage C',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,48,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.CTA C',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (66,'CHE C1','Chaudière électrique basse pression',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,34,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.CHE C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (67,'CHE C2','Chaudière électrique basse pression',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,34,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.CHE C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (68,'CCF C2','Clapet coupe feu',0,1,NULL,NULL,NULL,NULL,NULL,NULL,40,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,30,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.CCF C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (69,'CCF C1','Clapet coupe feu',0,1,NULL,NULL,NULL,NULL,NULL,NULL,54,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,30,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.CCF C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (70,'CCF C3','Clapet coupe feu',0,1,NULL,NULL,NULL,NULL,NULL,NULL,30,NULL,NULL,NULL,NULL,1,3,3,NULL,NULL,1,1,30,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.CCF C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (71,'SPLIT C2','Climatiseur Split systèm',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,29,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.SPLIT C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (72,'SPL LP','Climatiseur Split systèm',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,29,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.SPL LP',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (73,'SSI C2','Détection incendie',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,7,NULL,NULL,1,1,118,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.SSI C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (74,'SSI C1','Détection incendie',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,7,NULL,NULL,1,1,118,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.SSI C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (75,'SSI C3','Détection incendie',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,7,NULL,NULL,1,1,118,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.SSI C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (76,'DIS C2','Disconnecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,6,NULL,NULL,1,1,55,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.DIS C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (77,'DIS C1','Disconnecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,55,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.DIS C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (78,'DIS C3','Disconnecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,6,NULL,NULL,1,1,55,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.DIS C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (79,'ECH C2','Echangeur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,6,NULL,NULL,1,1,57,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.ECH C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (80,'ECH1  C1','Echangeur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,57,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.ECH1  C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (81,'FILT C1','Filtre',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,67,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.FILT C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (82,'FILT C3','Filtre à tamis',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,6,NULL,NULL,1,1,67,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.FILT C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (83,'FOSSE C1','fosse',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,104,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.FOSSE C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (84,'GTC C3','Gestion technique du Batiment',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,1,NULL,NULL,1,1,73,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.GTC C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (85,'GE C2','Groupe électrogène',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,2,NULL,NULL,1,1,68,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.GE C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (86,'GE  C1','Groupe électrogène',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,2,NULL,NULL,1,1,68,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.GE  C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (87,'GFV C2','Groupe frigorifique à vis',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,72,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.GFV C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (88,'GFC C1','Groupe frigorifique type Scroll',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,71,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.GFC C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (89,'GTC C1','GTC',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,1,NULL,NULL,1,1,73,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.GTC C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (90,'GTC C2','GTC',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,1,NULL,NULL,1,1,73,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.GTC C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (91,'MPR','Maintien de pression d\'eau glacée',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,83,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.MPR',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (92,'NAC C2','Nacelle de nettoyage',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,4,NULL,NULL,1,1,85,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.NAC C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (93,'OND 4','Onduleur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,2,NULL,NULL,1,1,87,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.OND 4',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (94,'OND 2 C3','Onduleur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,2,NULL,NULL,1,1,87,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.OND 2 C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (95,'OND 3','Onduleur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,2,NULL,NULL,1,1,87,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.OND 3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (96,'OND 1 C2','Onduleur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,2,NULL,NULL,1,1,87,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.OND 1 C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (97,'OND 1 C3','Onduleur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,2,NULL,NULL,1,1,87,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.OND 1 C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (98,'OND A','Onduleur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,2,NULL,NULL,1,1,87,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.OND A',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (99,'OND 2 C2','Onduleur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,2,NULL,NULL,1,1,87,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.OND 2 C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (100,'OND B','Onduleur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,2,NULL,NULL,1,1,87,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.OND B',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (101,'PARA C2','Paratonnerre',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,2,2,NULL,NULL,1,1,90,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.PARA C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (102,'MPR C2','Pompe de circulation',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,6,NULL,NULL,1,1,83,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.MPR C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (103,'PPE EC C3','Pompe de circulation  Réseau EC –VC',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,3,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.PPE EC C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (104,'PPE EG2 C3','Pompe de circulation  réseau EG-CTA toiture',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,3,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.PPE EG2 C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (105,'PPE EG C3','Pompe de circulation  réseau EG-VC',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,3,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.PPE EG C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (106,'PPE CH C2','Pompe de circulation ( circuit chaudière)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.PPE CH C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (107,'PPE B C2','Pompe decirculation(Cchauffage AILE B+LT CTA)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.PPE B C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (108,'PPE ANC2','Pompe de circulation(C rafrai AILE A NORD)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.PPE ANC2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (109,'PPE A C2','Pompe de circulation (C chauff AILE A NORD)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.PPE A C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (110,'PPE BC2','Pompe de circulation (C rafrai AILE B+L CTA)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.PPE BC2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (111,'PPE COEVC2','Pompe de circulation (condenseur évaporateur)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.PPE COEVC2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (112,'PPE CON','Pompe de circulation Condenseur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.PPE CON',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (113,'PPE CTA A','Pompe de circulation CTA A',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.PPE CTA A',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (114,'PPE CTA B','Pompe de circulation CTA B',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.PPE CTA B',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (115,'PPE CTA C','Pompe de circulation CTA C',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.PPE CTA C',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (116,'PPE B EC','Pompe de circulation EC',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.PPE B EC',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (117,'PPE A EC','Pompe de circulation EC',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.PPE A EC',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (118,'PPE C EC','Pompe de circulation EC',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.PPE C EC',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (119,'PPE B EG','Pompe de circulation EG',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.PPE B EG',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (120,'PPE A EG','Pompe de circulation EG',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.PPE A EG',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (121,'PPE C EG','Pompe de circulation EG',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.PPE C EG',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (122,'PPE EVA','Pompe de circulation Evaporateur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.PPE EVA',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (123,'PPE RECU B','Pompe de circulation Récup Bat B',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.PPE RECU B',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (124,'PPE CTA C3','Pompe de circulation réseau EC – CTA toiture',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,3,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.PPE CTA C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (125,'PPE RI C3','Pompe de circulation réseau EG- informatique',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,3,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.PPE RI C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (126,'PPE CTA RE','Pompe de circulation RESSTAU',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,97,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.PPE CTA RE',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (127,'REL PUIT','Pompe de puit',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,104,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.REL PUIT',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (128,'REL C3','Pompe de relevage et fosse',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,6,NULL,NULL,1,1,104,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.REL C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (129,'REL EU C1','Pompe de relevage et fosse',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,104,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.REL EU C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (130,'BAR C2','Porte battante',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,2,5,NULL,NULL,1,1,17,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.BAR C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (131,'ACC C1','Porte coulissante, sas, porte tambour',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,8,NULL,NULL,1,1,10,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.ACC C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (132,'ACC PARKC1','Porte coulissante, sas, porte tambour',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,1,8,NULL,NULL,1,1,10,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.ACC PARKC1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (133,'ACC C3','Porte coulissante, sas, porte tambour',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,8,NULL,NULL,1,1,10,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.ACC C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (134,'ACC C2','Porte coulissante, sas, porte tambour',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,8,NULL,NULL,1,1,10,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.ACC C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (135,'PORT C3','Portes',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,5,NULL,NULL,1,1,95,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.PORT C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (136,'PORT C1','Portes',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,5,NULL,NULL,1,1,95,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.PORT C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (137,'PORT C2','Portes',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,5,NULL,NULL,1,1,95,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.PORT C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (138,'RAC C2','Rideau d\'air chaud',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,99,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.RAC C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (139,'RAC C1','Rideau d\'air chaud',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,99,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.RAC C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (140,'RAC C3','Rideau d\'air chaud',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,3,NULL,NULL,1,1,99,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.RAC C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (141,'SAS C1','SAS',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,8,NULL,NULL,1,1,10,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.SAS C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (142,'SAS C2','SAS',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,8,NULL,NULL,1,1,10,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.SAS C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (143,'LUM C1','Source lumineuse',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,2,NULL,NULL,1,1,79,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.LUM C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (144,'LUM C2','Source lumineuse',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,2,NULL,NULL,1,1,79,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.LUM C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (145,'LUM C3','Source lumineuse',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,2,NULL,NULL,1,1,79,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.LUM C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (146,'STO C2','Store',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,5,NULL,NULL,1,1,119,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.STO C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (147,'STO C3','Store',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,5,NULL,NULL,1,1,119,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.STO C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (148,'STO C1','Store',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,5,NULL,NULL,1,1,119,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.STO C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (149,'TAB C1','Tableau électrique',0,1,NULL,NULL,NULL,NULL,NULL,NULL,22,NULL,NULL,NULL,NULL,1,1,2,NULL,NULL,1,1,121,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.TAB C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (150,'TAB C2','Tableau électrique',0,1,NULL,NULL,NULL,NULL,NULL,NULL,20,NULL,NULL,NULL,NULL,1,2,2,NULL,NULL,1,1,121,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.TAB C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (151,'TAB C3','Tableau électrique',0,1,NULL,NULL,NULL,NULL,NULL,NULL,25,NULL,NULL,NULL,NULL,1,3,2,NULL,NULL,1,1,121,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.TAB C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (152,'TGBT C1','TGBT',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,2,NULL,NULL,1,1,124,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.TGBT C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (153,'TGBT C2','TGBT',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,2,NULL,NULL,1,1,124,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.TGBT C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (154,'TGBT C3','TGBT',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,2,NULL,NULL,1,1,124,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.TGBT C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (155,'DES C3','Traitement des réseaux fermés',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,6,NULL,NULL,1,1,53,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.DES C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (156,'TRH C2','Transformateur à huile',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,2,NULL,NULL,1,1,128,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.TRH C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (157,'TRH C1','Transformateur à huile',0,1,NULL,NULL,NULL,NULL,NULL,NULL,2,NULL,NULL,NULL,NULL,1,1,2,NULL,NULL,1,1,128,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.TRH C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (158,'TRS C3','Transformateur sec',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,2,NULL,NULL,1,1,130,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.TRS C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (159,'TRS TGBT','Transformateur sec',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,2,NULL,NULL,1,1,130,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.TRS TGBT',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (160,'TRS OND A','Transformateur sec',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,2,NULL,NULL,1,1,130,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.TRS OND A',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (161,'ROB C2','Vannes et robinetterie',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,2,6,NULL,NULL,1,1,109,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.ROB C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (162,'ROB C3','Vannes et robinetterie',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,6,NULL,NULL,1,1,109,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.ROB C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (163,'ROB C1','Vannes et robinetterie',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,109,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.ROB C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (164,'EXP 1 C1','Vase et réservoir d\'expansion',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,63,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.EXP 1 C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (165,'EXP 2 C1','Vase et réservoir d\'expansion',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,6,NULL,NULL,1,1,63,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.EXP 2 C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (166,'EXP C3','Vase et réservoir d\'expansion',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,6,NULL,NULL,1,1,63,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.EXP C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (167,'VEC C','Ventilateur centrifuge',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,135,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.VEC C',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (168,'VEC L PAC','Ventilateur centrifuge',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,135,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.VEC L PAC',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (169,'VEC C3','Ventilateur centrifuge',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,3,3,NULL,NULL,1,1,135,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.VEC C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (170,'VEC A','Ventilateur centrifuge',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,135,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.VEC A',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (171,'DES  CIRC','Ventilateur désenfumage (Circulation Bat C)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,7,NULL,NULL,1,1,53,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.DES  CIRC',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (172,'DES CIR','Ventilateur  désenfumage (Circulation Bat)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,7,NULL,NULL,1,1,53,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.DES CIR',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (173,'DES CIRB','Ventilateur désenfumage (Circulation BatB)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,7,NULL,NULL,1,1,53,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.DES CIRB',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (174,'DES SCR','Ventilateur de désenfumage (SCRAMBLE)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,7,NULL,NULL,1,1,53,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.DES SCR',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (175,'DES A','Ventilateur de désenfumage Bat A',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,7,NULL,NULL,1,1,53,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.DES A',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (176,'DES CUI','Ventilateur de désenfumage(CUISINE)',0,1,NULL,NULL,NULL,NULL,NULL,NULL,1,NULL,NULL,NULL,NULL,1,1,7,NULL,NULL,1,1,53,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.DES CUI',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (177,'VC4C2','Ventilo-convecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,75,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,133,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.VC4C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (178,'VC4C3','Ventilo-convecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,58,NULL,NULL,NULL,NULL,1,3,3,NULL,NULL,1,1,133,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.VC4C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (179,'VC3C3','Ventilo-convecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,58,NULL,NULL,NULL,NULL,1,3,3,NULL,NULL,1,1,133,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.VC3C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (180,'VC2C3','Ventilo-convecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,58,NULL,NULL,NULL,NULL,1,3,3,NULL,NULL,1,1,133,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.VC2C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (181,'VC5C3','Ventilo-convecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,58,NULL,NULL,NULL,NULL,1,3,3,NULL,NULL,1,1,133,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.VC5C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (182,'VC5C2','Ventilo-convecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,75,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,133,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.VC5C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (183,'VC3C2','Ventilo-convecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,75,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,133,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.VC3C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (184,'VC2C2','Ventilo-convecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,75,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,133,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.VC2C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (185,'VC1C2','Ventilo-convecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,75,NULL,NULL,NULL,NULL,1,2,3,NULL,NULL,1,1,133,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C2.VC1C2',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (186,'VC6C1','Ventilo-convecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,90,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,133,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.VC6C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (187,'VC5C1','Ventilo-convecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,90,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,133,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.VC5C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (188,'VC4C1','Ventilo-convecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,90,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,133,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.VC4C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (189,'VC3C1','Ventilo-convecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,90,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,133,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.VC3C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (190,'VC2C1','Ventilo-convecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,90,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,133,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.VC2C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (191,'VC1C1','Ventilo-convecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,90,NULL,NULL,NULL,NULL,1,1,3,NULL,NULL,1,1,133,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C1.VC1C1',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL),
 (192,'VC1C3','Ventilo-convecteur',0,1,NULL,NULL,NULL,NULL,NULL,NULL,58,NULL,NULL,NULL,NULL,1,3,3,NULL,NULL,1,1,133,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,'C3.VC1C3',NULL,NULL,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,NULL,1,1,NULL,NULL,NULL,NULL,NULL,NULL,NULL);


--
-- Definition of table `equipement_attr`
--

CREATE TABLE `equipement_attr` (
  `eqip_att_seq` int(16) NOT NULL auto_increment,
  PRIMARY KEY  (`eqip_att_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `equipement_attr`
--



--
-- Definition of table `etatavance`
--

CREATE TABLE `etatavance` (
  `avan_seq` int(11) NOT NULL auto_increment,
  `avan_code` char(3) NOT NULL,
  `avan_libelle` varchar(15) default NULL,
  `avan_ordre` int(11) default '0',
  `avan_obligatoire` tinyint(3) unsigned default NULL,
  PRIMARY KEY  (`avan_seq`),
  UNIQUE KEY `AVAN_SEQ` (`avan_seq`),
  KEY `AVAN_CODE` (`avan_code`)
) ENGINE=InnoDB AUTO_INCREMENT=10 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `etatavance`
--

INSERT INTO `etatavance` (`avan_seq`,`avan_code`,`avan_libelle`,`avan_ordre`,`avan_obligatoire`) VALUES 
 (1,'IN','Inscrit',100,1),
 (2,'PR','Programmé',200,1),
 (3,'EC','En cours',300,1),
 (4,'TE','Terminé',400,1),
 (5,'AR','Archivé',500,1),
 (6,'EV','En validation',600,1),
 (7,'T+','Terminé+',410,1),
 (8,'AN','Annulé',490,1),
 (9,'AA','Archivé(Annulé)',590,1);


--
-- Definition of table `etatsante`
--

CREATE TABLE `etatsante` (
  `sant_seq` int(11) NOT NULL auto_increment,
  `sant_code` char(1) default NULL,
  `sant_libelle` varchar(15) default NULL,
  `sant_estmauvais` tinyint(3) unsigned default NULL,
  PRIMARY KEY  (`sant_seq`)
) ENGINE=InnoDB AUTO_INCREMENT=4 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `etatsante`
--

INSERT INTO `etatsante` (`sant_seq`,`sant_code`,`sant_libelle`,`sant_estmauvais`) VALUES 
 (1,'B','Bon',0),
 (2,'O','Obsolète',1),
 (3,'A','Acceptable',0);


--
-- Definition of table `export`
--

CREATE TABLE `export` (
  `exp_seq` int(11) NOT NULL auto_increment,
  `exp_liste` int(11) default NULL,
  `exp_ordre` int(11) default NULL,
  `exp_nomchamp` varchar(30) default NULL,
  `exp_libellechamp` varchar(30) default NULL,
  `exp_zus_fk` int(11) default NULL,
  PRIMARY KEY  (`exp_seq`),
  KEY `exp_zus_fk` (`exp_zus_fk`),
  KEY `exp_liste` (`exp_liste`),
  KEY `exp_ordre` (`exp_ordre`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `export`
--



--
-- Definition of table `famille_article`
--

CREATE TABLE `famille_article` (
  `fama_seq` int(11) NOT NULL auto_increment,
  `fama_code` varchar(15) NOT NULL,
  `fama_libelle` varchar(40) NOT NULL,
  PRIMARY KEY  (`fama_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `famille_article`
--



--
-- Definition of table `famille_equip`
--

CREATE TABLE `famille_equip` (
  `fame_seq` int(11) NOT NULL auto_increment,
  `fame_code` varchar(15) default NULL,
  `fame_libelle` varchar(30) default NULL,
  `fame_preventif` tinyint(3) unsigned default NULL,
  `fame_bdocument` tinyint(3) unsigned default NULL,
  `fame_duramortis` tinyint(3) unsigned default NULL,
  `fame_dom_fk` int(11) default NULL,
  `fame_trav_fk` int(11) default NULL,
  `fame_supe_fk` int(11) default NULL,
  `fame_bool_inactive` tinyint(3) unsigned default NULL,
  `fame_inte_fk` int(11) default NULL,
  `fame_datmaj` datetime default NULL,
  `fame_zus_maj_fk` int(11) default NULL,
  PRIMARY KEY  (`fame_seq`),
  KEY `fame_code` (`fame_code`),
  KEY `fame_libelle` (`fame_libelle`),
  KEY `fame_dom_fk` (`fame_dom_fk`),
  KEY `fame_trav_fk` (`fame_trav_fk`),
  KEY `fame_supe_fk` (`fame_supe_fk`)
) ENGINE=InnoDB AUTO_INCREMENT=137 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `famille_equip`
--

INSERT INTO `famille_equip` (`fame_seq`,`fame_code`,`fame_libelle`,`fame_preventif`,`fame_bdocument`,`fame_duramortis`,`fame_dom_fk`,`fame_trav_fk`,`fame_supe_fk`,`fame_bool_inactive`,`fame_inte_fk`,`fame_datmaj`,`fame_zus_maj_fk`) VALUES 
 (1,'ACA','Armoire de clim autonome',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (2,'ACB','Armoire de Clim à eau glacée',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (3,'ACC','Porte coulissante, tambour/SAS',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (4,'ACO','Production air comprimé',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (5,'ADO','Adoucisseur',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (6,'AER','Aérotherme',NULL,NULL,NULL,1,2,1,NULL,NULL,NULL,NULL),
 (7,'ALA','Alarmes techniques',NULL,NULL,NULL,2,2,1,NULL,NULL,NULL,NULL),
 (8,'ANI','Système anti-intrusion',NULL,NULL,NULL,4,3,1,NULL,NULL,NULL,NULL),
 (9,'AOIP','Démarreur bac AOIP',NULL,NULL,NULL,1,2,1,NULL,NULL,NULL,NULL),
 (10,'APK','Porte automatique parking',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (11,'ARM','Armoire électrotechnique',NULL,NULL,NULL,6,3,1,NULL,NULL,NULL,NULL),
 (12,'ASC','Ascenseur',NULL,NULL,NULL,2,2,1,NULL,NULL,NULL,NULL),
 (13,'BAC','Réservoir et bâche à eau',NULL,NULL,NULL,2,2,1,NULL,NULL,NULL,NULL),
 (14,'BAE','Batterie d\'accu étanche',NULL,NULL,NULL,8,2,1,NULL,NULL,NULL,NULL),
 (15,'BAG','Bac à graisse',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (16,'BAO','Batteries d\'accu ouvert',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (17,'BAR','Barrière automatique parking',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (18,'BAU','Bloc autonome (BAES)',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (19,'BDV','Boite de détente à débit varia',NULL,NULL,NULL,2,2,1,NULL,NULL,NULL,NULL),
 (20,'BEC','Ballon d\'eau chaude Prod Centr',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (21,'BECG','Ballon d\'eau chaude gaz',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (22,'BEG','Batterie terminale Eau Glacée',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (23,'BEL','Ballon d\'eau chaude Prod local',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (24,'CAC','Contrôle d\'accès',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (25,'CAD','Compacteur à déchets',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (26,'CAL','Caloduc',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (27,'CAN','Canalis',NULL,NULL,NULL,1,2,1,NULL,NULL,NULL,NULL),
 (28,'CAO','Console à eau',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (29,'CAS','Cassette plafonnière',NULL,NULL,NULL,2,2,1,NULL,NULL,NULL,NULL),
 (30,'CCF','Clapet coupe feu',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (31,'CEIA','Centrale d\'extinction auto',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (32,'CEL','Cellule haute tension',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (33,'CEX','Caisson d\'extraction',NULL,NULL,NULL,2,2,1,NULL,NULL,NULL,NULL),
 (34,'CHE','Chaudière élec basse pression',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (35,'CHF','Chaudière fioul basse pression',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (36,'CHG','Chaudière gaz basse pression',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (37,'CHM','Chaudière mixte F/G basse Pr',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (38,'CHV','Chaudière vapeur',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (39,'CIR','Circulateur -Sans accouplement',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (40,'CMG','Chaudière murale',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (41,'CO2','Extinction CO²',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (42,'COF','Coffret électrique',NULL,NULL,NULL,2,2,1,NULL,NULL,NULL,NULL),
 (43,'COL','Colonne montante',NULL,NULL,NULL,2,2,1,NULL,NULL,NULL,NULL),
 (44,'CON','Batteries de condensateurs',NULL,NULL,NULL,7,2,1,NULL,NULL,NULL,NULL),
 (45,'COR','Cordon chauffant',NULL,NULL,NULL,7,2,1,NULL,NULL,NULL,NULL),
 (46,'COS','Colonne sèche',NULL,NULL,NULL,2,2,1,NULL,NULL,NULL,NULL),
 (47,'CPCU','CPCU',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (48,'CTA','Centrale de traitement d\'air',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (49,'CUV','Cuve à fuel',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (50,'CVEL','Convecteur électrique',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (51,'DCO','Détection Co',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (52,'DEO','Détection d\'eau',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (53,'DES','Ventilateur de désenfumage',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (54,'DIG','Digicode',NULL,NULL,NULL,1,2,1,NULL,NULL,NULL,NULL),
 (55,'DIS','Disconnecteur',NULL,NULL,NULL,2,2,1,NULL,NULL,NULL,NULL),
 (56,'DRY','Dry cooler',NULL,NULL,NULL,2,2,1,NULL,NULL,NULL,NULL),
 (57,'ECH','Echangeur',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (58,'ECS','Réseaux eau chaude sanitaire',NULL,NULL,NULL,1,2,1,NULL,NULL,NULL,NULL),
 (59,'EFR','Réseau Eau froide',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (60,'EJE','Ejecto-Convecteur',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (61,'ENS','Enseigne',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (62,'EVA','Réseaux d\'évacuation EU/EV/EP',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (63,'EXP','Vase et réservoir d\'expansion',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (64,'EXT','Extincteur mobile',NULL,NULL,NULL,2,2,1,NULL,NULL,NULL,NULL),
 (65,'EXU','Exutoire de fumée',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (66,'FEN','Fenêtre',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (67,'FILT','Filtre à tamis',NULL,NULL,NULL,2,2,1,NULL,NULL,NULL,NULL),
 (68,'GE','Groupe électrogène',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (69,'GFC','Groupe frigorifique centrifuge',NULL,NULL,NULL,7,2,1,NULL,NULL,NULL,NULL),
 (70,'GFP','Groupe frigorifique à piston',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (71,'GFS','Groupe frigorifique Scroll',NULL,NULL,NULL,7,2,1,NULL,NULL,NULL,NULL),
 (72,'GFV','Groupe frigorifique à vis',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (73,'GTC','GTC',NULL,NULL,NULL,5,2,1,NULL,NULL,NULL,NULL),
 (74,'HOT','Hottes d\'extraction de cuisine',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (75,'HUM','Humidificateur',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (76,'HYD','Séparateur à hydrocarbure',NULL,NULL,NULL,2,3,1,NULL,NULL,NULL,NULL),
 (77,'INT','Interphonie',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (78,'INV','Inverseur de source',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (79,'LUM','Source lum & appareillage élec',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (80,'MAR','Mobilier armoire',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (81,'MBU','Mobilier bureau',NULL,NULL,NULL,1,2,1,NULL,NULL,NULL,NULL),
 (82,'MOD','Moduline',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (83,'MPR','Maintien de pression',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (84,'MTA','Module de traitement d\'air',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (85,'NAC','Nacelle de nettoyage',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (86,'NCV','Nettoyage par le vide',NULL,NULL,NULL,1,2,1,NULL,NULL,NULL,NULL),
 (87,'OND','Onduleur',NULL,NULL,NULL,2,2,1,NULL,NULL,NULL,NULL),
 (88,'PAC','Pompe à chaleur',NULL,NULL,NULL,5,2,1,NULL,NULL,NULL,NULL),
 (89,'PACB','Pompes à  chaleur sur boucle',NULL,NULL,NULL,5,2,1,NULL,NULL,NULL,NULL),
 (90,'PARA','Paratonnerre',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (91,'PCF','Porte coupe feu',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (92,'PDO','Pompe doseuse',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (93,'PLG','Poste de livraison GAZ',NULL,NULL,NULL,4,2,1,NULL,NULL,NULL,NULL),
 (94,'POB','Porte battante',NULL,NULL,NULL,2,2,1,NULL,NULL,NULL,NULL),
 (95,'PORT','Portes',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (96,'POT','Poteau et bouche d\'incendie',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (97,'PPE','Pompe de circulation',NULL,NULL,NULL,2,2,1,NULL,NULL,NULL,NULL),
 (98,'PRE','Préparateur d\'eau chaude sani',NULL,NULL,NULL,8,2,1,NULL,NULL,NULL,NULL),
 (99,'RAC','Rideau d\'air chaud',NULL,NULL,NULL,8,2,1,NULL,NULL,NULL,NULL),
 (100,'RAD','Radiateur',NULL,NULL,NULL,8,2,1,NULL,NULL,NULL,NULL),
 (101,'RAE','Batterie terminale électrique',NULL,NULL,NULL,8,2,1,NULL,NULL,NULL,NULL),
 (102,'RAY','Panneau rayonnant',NULL,NULL,NULL,5,2,1,NULL,NULL,NULL,NULL),
 (103,'REG','Régulation',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (104,'REL','Pompe de relevage et fosse',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (105,'RESA','Réseau Aéraulique',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (106,'RESH','Réseau hydraulique',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (107,'RIA','Réseau incendie armé',NULL,NULL,NULL,5,2,1,NULL,NULL,NULL,NULL),
 (108,'RID','Rideau métallique',NULL,NULL,NULL,5,2,1,NULL,NULL,NULL,NULL),
 (109,'ROB','Vannes et robinetterie',NULL,NULL,NULL,7,2,1,NULL,NULL,NULL,NULL),
 (110,'RON','Ronde',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (111,'SAI','Système d\'alarme incendie',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (112,'SAN','Bloc sanitaire',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (113,'SAS','SAS',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (114,'SEC','Assécheur d\'air',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (115,'SON','Sonorisation',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (116,'SPK','Extinction auto sprinkler',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (117,'SPL','Climatiseur Split systèm',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (118,'SSI','Détection incendie',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (119,'STO','Store',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (120,'SUR','Surpresseur',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (121,'TAB','Tableau électrique',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (122,'TEG','Traitement des réseaux glycolé',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (123,'TER','Entretien terrasse',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (124,'TGBT','TGBT',NULL,NULL,NULL,7,2,1,NULL,NULL,NULL,NULL),
 (125,'TOF','Traitement des réseaux fermés',NULL,NULL,NULL,8,2,1,NULL,NULL,NULL,NULL),
 (126,'TOO','Traitement des réseaux ouverts',NULL,NULL,NULL,7,2,1,NULL,NULL,NULL,NULL),
 (127,'TOU','Tour de refroidissement',NULL,NULL,NULL,1,2,1,NULL,NULL,NULL,NULL),
 (128,'TRH','Transformateur à huile',NULL,NULL,NULL,7,2,1,NULL,NULL,NULL,NULL),
 (129,'TRP','Transformateur PCB',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (130,'TRS','Transformateur sec',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (131,'UGA','Unité gainable',NULL,NULL,NULL,7,2,1,NULL,NULL,NULL,NULL),
 (132,'VAR','Variateur',NULL,NULL,NULL,5,2,1,NULL,NULL,NULL,NULL),
 (133,'VC','Ventilo-convecteur',NULL,NULL,NULL,6,2,1,NULL,NULL,NULL,NULL),
 (134,'VCF','Volet coupe feu',NULL,NULL,NULL,2,2,1,NULL,NULL,NULL,NULL),
 (135,'VEC','Ventilateur centrifuge',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL),
 (136,'VEH','Ventilateur hélicoïdal',NULL,NULL,NULL,3,2,1,NULL,NULL,NULL,NULL);


--
-- Definition of table `famille_equip_attr`
--

CREATE TABLE `famille_equip_attr` (
  `fame_att_seq` int(16) NOT NULL auto_increment,
  PRIMARY KEY  (`fame_att_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `famille_equip_attr`
--



--
-- Definition of table `file`
--

CREATE TABLE `file` (
  `file_seq` int(11) NOT NULL auto_increment,
  `file_libelle` varchar(40) default NULL,
  `file_type` varchar(40) default NULL,
  `file_date` date default NULL,
  `file_emetteur` varchar(40) default NULL,
  PRIMARY KEY  (`file_seq`)
) ENGINE=InnoDB AUTO_INCREMENT=56 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `file`
--

INSERT INTO `file` (`file_seq`,`file_libelle`,`file_type`,`file_date`,`file_emetteur`) VALUES 
 (1,'Test','Test','2008-10-10','JPB'),
 (2,'Test','Plan','2009-03-03','XL'),
 (3,'Test2','Plan','2009-03-03','XL'),
 (4,'Test3','Plan','2009-03-03','XL'),
 (5,'Plan 4','Plan','2009-03-03','XL'),
 (6,'Plan 5','Plan','2009-03-03','XL'),
 (7,'Plan 6','Plan','2009-03-03','XL'),
 (8,'Plan 7','Plan','2009-03-03','XL'),
 (9,'Plan 8','Plan','2009-03-03','XL'),
 (10,'CDC 1','CDC','2009-03-04','JPB'),
 (11,'CDC 2','CDC','2009-03-04','JPB'),
 (12,'CDC 3','CDC','2009-03-04','JPB'),
 (13,'CDC 4','CDC','2009-03-04','JPB'),
 (14,'CDC 5','CDC','2009-03-04','JPB'),
 (15,'CDC 6','CDC','2009-03-04','JPB'),
 (16,'CDC 7','CDC','2009-03-04','JPB'),
 (17,'CDC 8','CDC','2009-03-04','JPB'),
 (18,'Budget Mensuel 1','Document','2009-03-05','JPB'),
 (19,'Budget Mensuel 2','Document','2009-03-05','JPB'),
 (20,'Budget Mensuel 3','Document','2009-03-05','JPB'),
 (21,'Budget Mensuel 4','Document','2009-03-05','JPB'),
 (22,'Budget Mensuel 5','Document','2009-03-05','JPB'),
 (23,'Budget Mensuel 6','Document','2009-03-05','JPB'),
 (24,'Budget Mensuel 7','Document','2009-03-05','JPB'),
 (25,'Budget Mensuel 8','Document','2009-03-05','JPB'),
 (26,'Budget Mensuel 9','Document','2009-03-05','JPB'),
 (27,'Budget Mensuel 10','Document','2009-03-05','JPB'),
 (28,'Budget Mensuel 11','Document','2009-03-05','JPB'),
 (29,'Budget Mensuel 12','Document','2009-03-05','JPB'),
 (30,'Budget Mensuel 13','Document','2009-03-05','JPB'),
 (31,'Budget Mensuel 14','Document','2009-03-05','JPB'),
 (32,'Budget Mensuel 15','Document','2009-03-05','JPB'),
 (33,'Budget Mensuel 16','Document','2009-03-05','JPB'),
 (34,'Budget Mensuel 17','Document','2009-03-05','JPB'),
 (35,'Budget Mensuel 18','Document','2009-03-05','JPB'),
 (36,'Budget Mensuel 119','Document','2009-03-05','JPB'),
 (37,'Image 1','Image','2009-03-06','JPB'),
 (38,'Image 2','Image','2009-03-06','JPB'),
 (39,'Image 3','Image','2009-03-06','JPB'),
 (40,'Image 4','Image','2009-03-06','JPB'),
 (41,'Image 5','Image','2009-03-06','JPB'),
 (42,'Image 6','Image','2009-03-06','JPB'),
 (43,'Image 7','Image','2009-03-06','JPB'),
 (44,'Image 8','Image','2009-03-06','JPB'),
 (45,'Image 9','Image','2009-03-06','JPB'),
 (46,'Image 10','Image','2009-03-06','JPB'),
 (47,'Image 11','Image','2009-03-06','JPB'),
 (48,'Image 12','Image','2009-03-06','JPB'),
 (49,'Image 13','Image','2009-03-06','JPB'),
 (50,'Image 14','Image','2009-03-06','JPB'),
 (51,'Image 15','Image','2009-03-06','JPB'),
 (52,'Image 16','Image','2009-03-06','JPB'),
 (53,'Image 17','Image','2009-03-06','JPB'),
 (54,'Image 18','Image','2009-03-06','JPB'),
 (55,'Image 19','Image','2009-03-06','JPB');


--
-- Definition of table `formulaire`
--

CREATE TABLE `formulaire` (
  `form_seq` int(11) NOT NULL auto_increment,
  `form_code` varchar(10) default NULL,
  `form_libelle` varchar(30) default NULL,
  `form_utilisedefaut` tinyint(3) unsigned default NULL,
  `form_module_fk` tinyint(3) unsigned default NULL,
  `form_unique` tinyint(3) unsigned default NULL,
  PRIMARY KEY  (`form_seq`),
  KEY `form_code` (`form_code`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `formulaire`
--



--
-- Definition of table `formulaire_bloc`
--

CREATE TABLE `formulaire_bloc` (
  `fobl_seq` int(11) NOT NULL auto_increment,
  `fobl_libelle_voc_code` varchar(127) default NULL,
  `fobl_ordre` int(11) default NULL,
  `fobl_module_fk` tinyint(3) unsigned default NULL,
  `fobl_commentaire_voc_code` varchar(127) default NULL,
  `fobl_posatt_voc_code` varchar(127) default NULL,
  `fobl_mode` tinyint(3) unsigned default NULL,
  `fobl_atat` tinyint(3) unsigned default NULL,
  `fobl_constante` varchar(127) default NULL,
  `fobl_unique` tinyint(3) unsigned default NULL,
  PRIMARY KEY  (`fobl_seq`)
) ENGINE=InnoDB AUTO_INCREMENT=14 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `formulaire_bloc`
--

INSERT INTO `formulaire_bloc` (`fobl_seq`,`fobl_libelle_voc_code`,`fobl_ordre`,`fobl_module_fk`,`fobl_commentaire_voc_code`,`fobl_posatt_voc_code`,`fobl_mode`,`fobl_atat`,`fobl_constante`,`fobl_unique`) VALUES 
 (1,'Details',1,1,NULL,NULL,1,0,'bloc_details',0),
 (2,'Demandeur',2,1,NULL,NULL,1,0,'bloc_demandeur',0),
 (3,'Ressources',3,1,NULL,NULL,1,0,'bloc_ressources',0),
 (4,'AffectationPatrimoine',4,1,NULL,NULL,1,0,'bloc_affectationpatrimoine',0),
 (5,'AffectationAnalytique',5,1,NULL,NULL,1,0,'bloc_affectationanalytique',0),
 (6,'InfosComplementaires',6,1,NULL,NULL,1,1,'bloc_infoscomplementaires',0),
 (7,'Couts',7,1,NULL,NULL,1,0,'bloc_couts',0),
 (8,'CompteRendu',8,1,'EnModeConsultation','HeureReelleDeFin',2,0,'bloc_compterenduconsmodif',0),
 (9,'CompteRendu',9,1,'EnModeCompteRendu_','HeureReelleDeFin',3,0,'bloc_compterendu',0),
 (10,'Demandeur',1,2,NULL,NULL,1,0,'bloc_demandeur',0),
 (11,'Details',2,2,NULL,NULL,1,1,'bloc_details',0),
 (12,'Localisation',3,2,NULL,NULL,1,0,'bloc_localisation',0),
 (13,'InfosComplementaires',4,2,NULL,NULL,1,1,'bloc_infoscomplementaires',0);


--
-- Definition of table `formulaire_rubrique`
--

CREATE TABLE `formulaire_rubrique` (
  `foru_seq` int(11) NOT NULL auto_increment,
  `foru_libelle_voc_code` varchar(127) default NULL,
  `foru_ordre` int(11) default NULL,
  `foru_fobl_fk` int(11) default NULL,
  `foru_obligatoire` tinyint(3) unsigned default NULL,
  `foru_fige` tinyint(3) unsigned default NULL,
  `foru_atat_fk` int(11) default NULL,
  `foru_mode` tinyint(3) unsigned default NULL,
  `foru_commentaire_voc_code` varchar(127) default NULL,
  `foru_constante` varchar(127) default NULL,
  `foru_prgn` varchar(30) default NULL,
  PRIMARY KEY  (`foru_seq`)
) ENGINE=InnoDB AUTO_INCREMENT=80 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `formulaire_rubrique`
--

INSERT INTO `formulaire_rubrique` (`foru_seq`,`foru_libelle_voc_code`,`foru_ordre`,`foru_fobl_fk`,`foru_obligatoire`,`foru_fige`,`foru_atat_fk`,`foru_mode`,`foru_commentaire_voc_code`,`foru_constante`,`foru_prgn`) VALUES 
 (1,'Details',1,1,1,0,0,1,NULL,'oper_contenu',NULL),
 (2,'ConsignesParticulieres',2,1,1,0,0,1,NULL,'oper_consiparti',NULL),
 (3,'OpPrecedentes',3,1,0,0,0,1,NULL,'opprecedentes',NULL),
 (4,'Historique',4,1,0,0,0,1,NULL,'historique',NULL),
 (5,'DateEtHeureInscription',5,1,0,0,0,1,NULL,'dateetheureinscription',NULL),
 (6,'DateEtHeureAcquittement',6,1,0,0,0,1,NULL,'dateetheureacquittement',NULL),
 (7,'DatesPrevisionnellesDeDebut',7,1,1,0,0,1,NULL,'oper_datedebutp',NULL),
 (8,'DureeEnJours',8,1,1,0,0,1,NULL,'oper_dureejourp',NULL),
 (9,'DatesPrevisionnellesDeFin',9,1,1,0,0,1,NULL,'oper_datefinp',NULL),
 (10,'HorairePrevisionnel',10,1,0,0,0,1,NULL,'oper_dureepresp',NULL),
 (11,'DatesReelles',11,1,0,0,0,4,'EnConsultation_','datesrelles',NULL),
 (12,'HoraireReel',12,1,0,0,0,4,'EnConsultation_','horairereel',NULL),
 (13,'VisualisationEcheance',13,1,0,0,0,1,NULL,'visualisationecheance',NULL),
 (14,'Service',1,2,1,0,0,1,NULL,'service',NULL),
 (15,'Demandeur',2,2,1,0,0,1,NULL,'nometprenom',NULL),
 (16,'Telephone',3,2,1,0,0,1,NULL,'telephone',NULL),
 (17,'Email',4,2,1,0,0,1,NULL,'email',NULL),
 (18,'Agence',1,3,1,0,0,1,NULL,'agence','PRGN_AGENCE_ACT'),
 (19,'Superviseur',2,3,1,0,0,1,NULL,'superviseur',NULL),
 (20,'EquipeDeTravaux',3,3,1,0,0,1,NULL,'equipeTrav',NULL),
 (21,'Intervenant',4,3,1,0,0,1,NULL,'intervenant',NULL),
 (22,'Site',1,4,1,0,0,1,NULL,'site','PRGN_GDA_SITE_VIS'),
 (23,'Batiment',2,4,1,0,0,1,NULL,'batiment',NULL),
 (24,'Zone',3,4,1,0,0,1,NULL,'zone',NULL),
 (25,'Local',4,4,1,0,0,1,NULL,'local',NULL),
 (26,'Equipement',5,4,1,0,0,1,NULL,'equipement',NULL),
 (27,'TypeDeDefaut',6,4,1,0,0,1,NULL,'typeDefaut',NULL),
 (28,'Criticite',1,5,1,0,0,1,NULL,'criticite','PRGN_CRITICITE_ACT'),
 (29,'Contrat',2,5,1,0,0,1,NULL,'contrat',NULL),
 (30,'Projet',3,5,1,0,0,1,NULL,'projet',NULL),
 (31,'AffectationFinanciere',5,5,1,0,0,1,NULL,'affectFin','PRGN_AFFECT_FINAN_ACT'),
 (32,'Facturable',4,5,0,0,0,1,NULL,'facturable',NULL),
 (33,'FichiersJoints',1,6,0,0,0,1,NULL,'fichiersjoints',NULL),
 (34,'CoutsPrevisionnels',1,7,0,0,0,1,NULL,'coutsprevisionnels',NULL),
 (35,'CoutsReels',2,7,0,0,0,1,NULL,'coutsreels',NULL),
 (36,'NotionsDePrestation',3,7,0,0,0,1,NULL,'notionsdeprestation',NULL),
 (37,'NotionsDeFournitures',4,7,0,0,0,1,NULL,'notionsdefournitures',NULL),
 (38,'NotionsDeDivers',5,7,0,0,0,1,NULL,'notionsdedivers',NULL),
 (39,'Commentaires',9,8,0,0,0,1,NULL,'commentaires',NULL),
 (40,'DateReelleDeDebut',1,8,0,0,0,1,NULL,'datereellededebut',NULL),
 (41,'HeureReelleDeDebut',2,8,0,0,0,1,NULL,'heurereellededebut',NULL),
 (42,'DateReelleDeFin',4,8,0,0,0,1,NULL,'datereelledefin',NULL),
 (43,'HeureReelleDeFin',5,8,0,0,0,1,NULL,'heurereelledefin',NULL),
 (44,'CumulDeLaPrestation',6,8,0,0,0,1,NULL,'nombredheuresdeprestation',NULL),
 (45,'Coefficient',8,8,0,0,0,1,NULL,'coefficient',NULL),
 (46,'GestionParIntervenant',10,8,0,0,0,1,NULL,'gestionparintervenant',NULL),
 (47,'GestionDesDivers',11,8,0,0,0,1,NULL,'gestiondesdivers',NULL),
 (48,'Commentaires',9,9,1,0,0,1,NULL,'commentaires',NULL),
 (49,'DateReelleDeDebut',1,9,1,0,0,1,NULL,'datereellededebut',NULL),
 (50,'HeureReelleDeDebut',2,9,1,0,0,1,NULL,'heurereellededebut',NULL),
 (51,'DateReelleDeFin',4,9,1,0,0,1,NULL,'datereelledefin',NULL),
 (52,'HeureReelleDeFin',5,9,1,0,0,1,NULL,'heurereelledefin',NULL),
 (53,'NombreDHeuresDePrestation',6,9,1,0,0,1,NULL,'nombredheuresdeprestation',NULL),
 (54,'Coefficient',8,9,0,0,0,1,NULL,'coefficient',NULL),
 (55,'GestionParIntervenant',10,9,1,0,0,1,NULL,'gestionparintervenant',NULL),
 (56,'GestionDesDivers',11,9,0,0,0,1,NULL,'gestiondesdivers',NULL),
 (57,'Service',1,10,1,0,0,1,NULL,'service',NULL),
 (58,'NomEtPrenom',2,10,1,0,0,1,NULL,'nometprenom',NULL),
 (59,'Telephone',3,10,1,0,0,1,NULL,'telephone',NULL),
 (60,'Email',4,10,1,0,0,1,NULL,'email',NULL),
 (61,'Details',1,11,1,0,0,1,NULL,'detail',NULL),
 (62,'Criticite',2,11,1,1,0,1,NULL,'criticite','PRGN_CRITICITE_ACT'),
 (63,'Contrat',3,11,1,1,0,1,NULL,'contrat',NULL),
 (64,'Projet',4,11,1,0,0,1,NULL,'projet',NULL),
 (65,'Facturable',5,11,0,1,0,1,NULL,'facturable',NULL),
 (66,'AffectationFinanciere',6,11,1,1,0,1,NULL,'affectFin','PRGN_AFFECT_FINAN_ACT'),
 (67,'Site',1,12,1,0,0,1,NULL,'site','PRGN_GDA_SITE_VIS'),
 (68,'Batiment',2,12,1,0,0,1,NULL,'batiment',NULL),
 (69,'Zone',3,12,1,0,0,1,NULL,'zone',NULL),
 (70,'Local',4,12,1,0,0,1,NULL,'local',NULL),
 (71,'Equipement',5,12,1,0,0,1,NULL,'equipement',NULL),
 (72,'GestionDesFichiersJoints',1,13,0,0,0,1,NULL,'gestiondesfichiersjoints',NULL),
 (74,'DureeIndisponibilite',7,8,0,0,0,1,'','oper_nbheureindisp',''),
 (75,'DureeIndisponibilite',7,9,0,0,0,1,'','oper_nbheureindisp',''),
 (76,'DureeEnJours',3,8,0,0,0,1,NULL,'dureeenjours',NULL),
 (77,'DureeEnJours',3,9,0,0,0,1,NULL,'dureeenjours',NULL),
 (78,'OperationVerte',14,1,0,0,0,1,NULL,'oper_verte',NULL),
 (79,'InterruptionDeService',15,1,0,0,0,1,NULL,'oper_stopservic',NULL);


--
-- Definition of table `fournisseurs`
--

CREATE TABLE `fournisseurs` (
  `four_seq` int(11) NOT NULL auto_increment,
  `four_libelle` varchar(40) NOT NULL,
  `four_adr1` varchar(35) default NULL,
  `four_adr2` varchar(35) default NULL,
  `four_adr3` varchar(35) default NULL,
  `four_cp` varchar(7) default NULL,
  `four_ville` varchar(25) default NULL,
  `four_pays` varchar(20) default NULL,
  `four_code` varchar(10) default NULL,
  `four_telephone` varchar(15) default NULL,
  `four_telecopie` varchar(15) default NULL,
  `four_siret` varchar(14) default NULL,
  `four_ape` varchar(10) default NULL,
  `four_datmaj` date default NULL,
  `four_email` varchar(45) default NULL,
  `four_website` varchar(45) default NULL,
  `four_spec_fk` int(11) default NULL,
  PRIMARY KEY  (`four_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `fournisseurs`
--



--
-- Definition of table `fparam_assignment_group`
--

CREATE TABLE `fparam_assignment_group` (
  `fpag_seq` int(11) NOT NULL auto_increment,
  `fpag_pweb_fk` int(11) default NULL,
  `fpag_zgrp_fk` int(11) default NULL,
  `fpag_sloc_fk` int(11) default NULL,
  PRIMARY KEY  (`fpag_seq`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `fparam_assignment_group`
--



--
-- Definition of table `fparam_dit_domain`
--

CREATE TABLE `fparam_dit_domain` (
  `FPDD_SEQ` int(11) NOT NULL auto_increment,
  `FPDD_PWEB_FK` int(11) default NULL,
  `FPDD_DOM_FK` int(11) default NULL,
  PRIMARY KEY  (`FPDD_SEQ`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `fparam_dit_domain`
--



--
-- Definition of table `fparam_dit_workorder_type`
--

CREATE TABLE `fparam_dit_workorder_type` (
  `FDWT_SEQ` int(11) NOT NULL auto_increment,
  `FDWT_PWEB_FK` int(11) default NULL,
  `FDWT_TOPE_FK` int(11) default NULL,
  PRIMARY KEY  (`FDWT_SEQ`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `fparam_dit_workorder_type`
--



--
-- Definition of table `fparam_module_free_access`
--

CREATE TABLE `fparam_module_free_access` (
  `FMFA_SEQ` int(11) NOT NULL auto_increment,
  `FMFA_PWEB_FK` int(11) default NULL,
  `FMFA_MODULE_ID` int(11) default NULL,
  `FMFA_IS_MODULE_SELECTED` int(1) default NULL,
  PRIMARY KEY  (`FMFA_SEQ`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `fparam_module_free_access`
--



--
-- Definition of table `fparam_sre_time_range`
--

CREATE TABLE `fparam_sre_time_range` (
  `FSTR_SEQ` int(11) NOT NULL auto_increment,
  `FSTR_PWEB_FK` int(11) default NULL,
  `FSTR_BEGIN_TIME` time default NULL,
  `FSTR_END_TIME` time default NULL,
  PRIMARY KEY  (`FSTR_SEQ`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `fparam_sre_time_range`
--



--
-- Definition of table `fsql_rechs`
--

CREATE TABLE `fsql_rechs` (
  `RECH_SEQ` int(11) NOT NULL default '0',
  `RECH_CODE` int(11) default NULL,
  `RECH_NOM` varchar(30) default NULL,
  `RECH_DESC` varchar(64) default NULL,
  `RECH_SQL_TXT` text,
  `RECH_EVAL` int(3) default NULL,
  PRIMARY KEY  (`RECH_SEQ`),
  KEY `RECH_NOM` (`RECH_NOM`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1;

--
-- Dumping data for table `fsql_rechs`
--



--
-- Definition of table `gamme`
--

CREATE TABLE `gamme` (
  `game_seq` int(11) NOT NULL auto_increment,
  `game_code` varchar(10) default NULL,
  `game_libelle` varchar(30) default NULL,
  `game_contenu` text,
  `game_consiparti` text,
  `game_dureepres` decimal(16,2) default NULL,
  `game_dureejour` int(11) default NULL,
  `game_verte` tinyint(3) unsigned default NULL,
  `game_stopservic` tinyint(3) unsigned default NULL,
  `game_gen_diff` tinyint(3) unsigned default NULL,
  `game_bool_inactive` tinyint(3) unsigned default NULL,
  `game_bdocument` tinyint(3) unsigned default NULL,
  `game_maj_gene` tinyint(3) unsigned default NULL,
  `game_tope_fk` int(11) default NULL,
  `game_dom_fk` int(11) default NULL,
  `game_tdef_fk` int(11) default NULL,
  PRIMARY KEY  (`game_seq`),
  KEY `game_code` (`game_code`),
  KEY `game_tope_fk` (`game_tope_fk`),
  KEY `game_dom_fk` (`game_dom_fk`)
) ENGINE=InnoDB AUTO_INCREMENT=203 DEFAULT CHARSET=latin1;

--
-- Dumping data for table `gamme`
--

INSERT INTO `gamme` (`game_seq`,`game_code`,`game_libelle`,`game_contenu`,`game_consiparti`,`game_dureepres`,`game_dureejour`,`game_verte`,`game_stopservic`,`game_gen_diff`,`game_bool_inactive`,`game_bdocument`,`game_maj_gene`,`game_tope_fk`,`game_dom_fk`,`game_tdef_fk`) VALUES 
 (1,'21.07.S','Armoire de clim autonome','\r\n[…] Essai des fonctions Auto/Arrêt/Manu\r\n[…] Contrôle de la commande locale Chaud/Froid/Vitesse ventilateur\r\n[…] Contrôle de la programmation horaire\r\n[…] Nettoyage général interne, externe\r\n[…] Contrôle des filtres et remplacement si nécessaire\r\n[…] Manœuvre des vannes d\'isolement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nVentilateur\r\n[…] Contrôle de la tension de l\'alignement et de l\'état des courroies\r\n[…] Graissage des paliers moteurs et turbine\r\n[…] Contrôle de l\'isolement et de l\'intensité absorbée du moteur\r\n[…] Contrôle du serrage de la boite à bornes moteur\r\n[…] Contrôle de la fixation de l\'ensemble moteur ventilateur\r\n[…] Contrôle de l\'état des roulements moteur et ventilateur\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nCircuit frigorifique\r\n[…] Contrôle  des connexions plaque à borne moteur du compresseur\r\n[…] Contrôle des pressions HP/BP et de l\'état anhydre du circuit\r\n[…] Contrôle des pressostats de régulation HP/BP\r\n[…] Contrôle des pressostats de sécurité HP/BP\r\n[…] Contrôle du voyant liquide\r\n[…] Contrôle du filtre déhydrateur\r\n[…] Contrôle de l\'isolement et de l\'intensité absorbée du ou des compresseurs\r\n[…] Contrôle de l\'état des calorifuges\r\n[…] Contrôle de la charge frigorifique et  de l\'étanchéité du circuit \r\nAttention remplir le certificat de recherche de fuite annuelle\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRéseau évaporateur \r\n[…] Contrôle évacuation condensats et nettoyage du bac\r\n[…] Contrôle état de la batterie\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nCondensation à air\r\n[…] Contrôle général du condenseur\r\n[…] Contrôle de l\'intensité absorbée du ou des ventilateurs\r\n[…] Contrôle de la protection électrique du condenseur\r\n[…] Nettoyage du condenseur\r\n[…] Nettoyage du ou des ventilateurs\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nCondensation à eau\r\n[…] Con trôle de la vanne pressostatique\r\n[…] Vérification de l\'étanchéité des joints et des flexibles\r\n[…] Contrôle vanne d\'isolement et filtre à tamis\r\n[…] Contrôle du bon écoulement des eaux\r\n[…] Relevé du compteur d\'eau\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nBatterie électrique\r\n[…] Contrôle du fonctionnement \r\n[…] Contrôle de l\'isolement et de l\'intensité absorbée\r\n[…] Contrôle du thermostat de sécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nHumidificateur\r\n[…] Contrôle du système d\'alimentation automatique en eau\r\n[…] Nettoyage du bac\r\n[…] Contrôle de la régulation\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nHumidificateur vapeur\r\n[…] Contrôle de l\'intensité absorbée\r\n[…] Contrôle de l\'étanchéité des conduits vapeur\r\n[…] Contrôle des électrodes et de la cuve\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRégulation\r\n[…] Contrôle du serrage des connexions\r\n[…] Contrôle du fonctionnement de la régulation (Points de consignes, paramètres de fonctionnement)\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (2,'26.01.S','Armoire de Climatisation à eau','\r\n[…] Essai des fonctions Auto/Arrêt/Manu \r\n[…] Contrôle de la commande locale Chaud/Froid/Vitesse ventilateur\r\n[…] Contrôle de la programmation horaire\r\n[…] Nettoyage général interne, externe\r\n[…] Contrôle des filtres et remplacement si nécessaire\r\n[…] Manœuvre des vannes d\'isolement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nVentilateur\r\n[…] Contrôle de la tension de l\'alignement et de l\'état des courroies\r\n[…] Graissage des paliers moteurs et turbine\r\n[…] Contrôle de l\'isolement et de l\'intensité absorbée du moteur\r\n[…] Contrôle du serrage de la boite à bornes moteur\r\n[…] Contrôle de la fixation de l\'ensemble moteur ventilateur\r\n[…] Contrôle de l\'état des roulements moteur et ventilateur\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRéseau hydraulique\r\n[…] Contrôle de l\'étanchéité des vannes d\'isolement\r\n[…] Contrôle de l\'étanchéité et de l\'état de la batterie\r\n[…] Contrôle évacuation condensats et nettoyage du bac\r\n[…] Contrôle de l\'état du calorifuge\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nBatterie électrique\r\n[…] Contrôle du fonctionnement \r\n[…] Contrôle de l\'isolement et de l\'intensité absorbée\r\n[…] Contrôle du thermostat de sécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nHumidificateur\r\n[…] Contrôle du système d\'alimentation automatique en eau\r\n[…] Nettoyage du bac\r\n[…] Contrôle de la régulation\r\n[…] Humidificateur vapeur\r\n[…] Contrôle de l\'intensité absorbée\r\n[…] Contrôle de l\'étanchéité des conduits vapeur\r\n[…] Contrôle des électrodes et de la cuve\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRégulation\r\n[…] Contrôle du serrage des connexions\r\n[…] Contrôle du fonctionnement de la régulation (Points de consignes, paramètres de fonctionnement)\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (3,'80.02.S','Porte piétonne, coulissante, t','[...] Opération sous traitée à _________________________________________\r\n\r\nContrat N° ____________________________\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (4,'90.01.S','Production air comprimé','[…] Opération sous  traité selon contrat N°\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (5,'30.02.A','Adoucisseur','[…] Nettoyage de la vanne et de la canne d\'aspiration et de la crépine\r\n[…] Manœuvre de la robinetterie\r\n[…] Contrôle des clapets\r\n[…] Vidange et nettoyage des bipasses\r\n[…] Resserrage des presse-étoupes\r\n[…] Contrôle des connexions électriques\r\n[…] Nettoyage du bac à saumure\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (6,'30.02.T','Adoucisseur','[…] Analyse TH, PH, et TCL à l\'arrivée eau de ville\r\n[…] Analyse TH, PH, et TCL en sortie d\'adoucisseur\r\n[…] Analyse TH, PH, et TCL après mixage\r\n[…] Contrôle de la programmation de l\'horloge\r\n[…] Contrôle du fonctionnement de l\'électrovanne pilote\r\n[…] Contrôle de la bonne régénération\r\n[…] Contrôle du bon écoulement des eaux\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (7,'24.02.S','Aérotherme','[…] Contrôle du filtre et remplacement si nécessaire\r\n[…] Dépoussiérage des batteries et du moto ventilateur\r\n[…] Contrôle de l\'intensité et de l\'isolement du moto ventilateur \r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nBatterie chaude\r\n[…] Purge de l\'air de la batterie\r\n[…] Contrôle du fonctionnement de la régulation et des électrovannes\r\n[…] Contrôle de la robinetterie d\'isolement, manœuvre des vannes\r\n[…] Contrôle des presses étoupes\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nBatterie électrique\r\n[…] Contrôle de l\'intensité batterie électrique\r\n[…] Contrôle du fonctionnement de la régulation et des sécurités\r\n[…] Contrôle des connexions électriques\r\n[…] Contrôle de l\'état du calorifuge\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (8,'A10000','Baie report d\'alarmes techniqu','[…] Dépoussiérage et nettoyage de la baie\r\n[…] Contrôle des voyants\r\n[…] Contrôle des connexions\r\n[…] Contrôle du report effectif des alarmes\r\n[…] Contrôle de l’alarme sonore\r\n[…] Contrôle de la bonne transmission des alarmes (télétransmetteur, imprimante, modem …)\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (9,'60.03.A','Anti-intrusion','[..] Opération sous traitée à _________________________________________\r\n\r\nContrat N° ____________________________\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (10,'11.12.A','Démarreur bac AOIP','[…] Contrôle des connexions\r\n[…] Contrôle de l\'état du bac\r\n[…] Contrôle du niveau d\'eau et ajout si nécessaire ( eau distillée)\r\n[…] \"Contrôle des performances:\r\n -Relevé Id/IN\r\n -Relevé du temps de démarrage et comparaison avec les caractéristiques plaquées    \"\r\n[…] Contrôle du ou des thermostat de sécurité\r\n[…] Contrôle de l\'interrupteur centrifuge\r\n[…] Renouvellement de l\'électrolyte ( suivant prescriptions constructeur (5ans) ou suivant performances\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEnvironnement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n\"Les batteries sont des DID.En fin de vie, elles doivent être éliminées ou valorisée spécifiquement dans les filières appropriées .\r\nIl doit être réalisé un Bordereau de Suivi de Déchets Industriels \r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (11,'80.03.S','Porte parking','[...] Opération sous traitée à _________________________________________\r\n\r\nContrat N° ____________________________\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'6.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (12,'11.09.A','Armoire électrotechnique','[…] Essai Auto/Arrêt/Manu\r\n[…] Essai arrêt d\'urgence\r\n[…] Contrôle de la présence du schéma dans l\'armoire électrique. Remise à jour du schéma si nécessaire\r\n[…] Contrôle de l\'intensité et de l\'équilibrage des phases\r\n[…] Essai des disjoncteurs différentiels\r\n[…] Essai des reports et télécommandes GTB\r\n[…] Contrôle cohérence des indicateurs de mesure en façade\r\n[…] Suivi de la procédure de consignation \r\n[…] Contrôle du serrage des connexions  En fonction de la thermographie\r\n[…] Contrôle du calibrage des fusibles par rapport au schéma\r\n[…] Contrôle du réglage des relais thermiques par rapport au schéma\r\n[…] Contrôle des temporisations\r\n[…] Contrôle du pouvoir coupe circuit des disjoncteurs par rapport au schéma\r\n[…] Contrôle des liaisons équipotentielles\r\n[…] Contrôle état des goulottes\r\n[…] Contrôle état des presse-étoupes\r\n[…] Contrôle fixation de l\'armoire\r\n[…] Nettoyage et dépoussiérage de l\'armoire\r\n[…] Suivi de la procédure de déconsignation \r\n[…] Contrôle thermique infrarouge Ost Si contractuel\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (13,'70.02.M','Ascenseur','[…] Opération sous  traité selon contrat N°\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.10',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (14,'30.07.A','Réservoir et bâche à eau','[…] Vidange de la bâche\r\n[…] Contrôle des différentes vannes\r\n[…] Contrôle du flotteur\r\n[…] Nettoyage de la bâche\r\n[…] Contrôle remplissage par flotteur et surpresseur\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (15,'11.04.A','Batterie d\'accumulateurs type ','[…] Relevé du courant de charge\r\n[…] Mesure de la tension de chaque élément\r\n[…] Essai d\'autonomie et mesure de la tension globale de décharge tout au long de l\'essai\r\n[…] Mesure par sondage de la tension de certains éléments pendant la décharge\r\n[…] Contrôle de l\'état du support\r\n[…] Consignation de l\'installation\r\n[…] Nettoyage, graissage des bornes et vérification du serrage\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEnvironnement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n\"Les batteries sont des DID.En fin de vie, elles doivent être éliminées ou valorisée spécifiquement dans les filières appropriées .\r\nIl doit être réalisé un Bordereau de Suivi de Déchets Industriels code 16 06 01;16 06 02;16 06 03\"\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,NULL,5,0,0,0,1,NULL,NULL,1,3,NULL),
 (16,'40.02.A','Bac à graisse','[…] Curage annuel des canalisations horizontales par les regards (Opération sous traitée)\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (17,'40.02.S','Bac à graisse','[...] Contrôle du niveau de remplissage\r\n[…] Pompage et nettoyage bac à graisses et fécules (Opération sous traitée)\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (18,'11.05.A','Batteries d\'accumulateurs type','[…] Relevé du courant de charge\r\n[…] Mesure de la tension de chaque élément\r\n[…] Test d\'autonomie et mesure de la tension  globale de décharge tout au long de l\'essai\r\n[…] Mesure par sondage de la tension de certains éléments au cours de la décharge\r\n[…] Contrôle de l\'état des supports\r\n[…] Contrôle au pèse acide de chaque élément\r\n[…] Consignation de l\'installation\r\n[…] Nettoyage et graissage des bornes\r\n\r\n------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEnvironnement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n\"Les batteries sont des DID.En fin de vie, elles doivent être éliminées ou valorisée spécifiquement dans les filières appropriées .\r\nIl doit être réalisé un Bordereau de Suivi de Déchets Industriels code 16 06 01;16 06 02;16 06 03\"\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (19,'11.05.T','Batteries d\'accumulateurs type','[…] Contrôle du niveau de l\'électrolyte, appoint éventuel\r\n\r\n------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEnvironnement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n\"Les batteries sont des DID.En fin de vie, elles doivent être éliminées ou valorisée spécifiquement dans les filières appropriées .\r\nIl doit être réalisé un Bordereau de Suivi de Déchets Industriels code 16 06 01;16 06 02;16 06 03\"\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (20,'80.04.S','Barrière automatique parking','[...] Opération sous traitée à _________________________________________\r\n\r\nContrat N° ____________________________\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (21,'51.12.M','Éclairage de sécurité','[…] Contrôle du bon fonctionnement en cas de défaillance de la source normale\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEnvironnement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nles accumulateurs , les tubes fluorescents sont des DID.En fin de vie, ils doivent être collectés dans des containers spécifiques et être recyclés. Il doit être réalisé un Bordereau de Suivi de Déchets Industriels.',NULL,'0.02',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (22,'51.12.S','Éclairage de sécurité','[…] Essai de la commande de mise au repos\r\n[…] Contrôle de l’autonomie (1 heure)\r\n[…] Contrôle de la fixation des blocs\r\n[…] Remplacement des pictogrammes endommagés ou périmés\r\n[…] Contrôle de la présence d\'un stock minimum des lampes et accumulateurs\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEnvironnement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nles accumulateurs , les tubes fluorescents sont des DID.En fin de vie, ils doivent être collectés dans des containers spécifiques et être recyclés. Il doit être réalisé un Bordereau de Suivi de Déchets Industriels.',NULL,'0.05',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (23,'26.08.A','Boite de détente à débit varia','[…] Contrôle de l\'état général\r\n[…] Contrôle et resserrage des connexions électriques\r\n[…] Contrôle des débits d\'air maxi et mini au manomètre différentiel\r\n[…] Contrôle de l\'état de la tringlerie (piston/registre)\r\n[…] Contrôle de l\'état des raccordements aérauliques\r\n[…] Contrôle de l\'encrassement batterie et nettoyage si nécessaire\r\n[…] Contrôle presse-étoupe vanne de régulation\r\n[…] Vérification fonctionnelle de la régulation et servomoteur\r\n[…] Contrôle de l\'état général (fuite d\'air)\r\n[…] Manœuvre des vannes d\'isolement\r\n[…] Relevé des débits et pressions sur fiche\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (24,'31.04.A','Ballon d\'eau chaude sanitaire ','[…] Vidange du ballon et contrôle des parois internes  (Si les parois présentent des signes de corrosion importante prévoir la remise en état du ballon ou son remplacement )\r\n[…] Contrôle et détartrage des faisceaux ou des résistances électrique\r\n[…] Nettoyage interne et désinfection chimique du ballon ((Si nécessaire))\r\n[…] Analyse légionelle en fond de ballon (Opération sous traitée par _____________________________) (Préconisation)\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (25,'31.04.T','Ballon d\'eau chaude sanitaire ','[…] Chasse rapide en partie basse\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.05',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (26,'31.04.S','Ballon d\'eau chaude sanitaire ','[…] Contrôle de la régulation\r\n[…] Contrôle du point de consigne > 55°C\r\n[…] Contrôle du bon fonctionnement des thermomètres\r\n[…] Contrôle de la soupape de sécurité\r\n[…] Contrôle de l\'isolement et de l\'intensité des résistances électriques\r\n[…] Réalisation d\'un choc thermique. Élévation de la température du ballon à 70°C pendant 30 mn\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (27,'31.06.A','Ballon d\'eau chaude sanitaire ','[…] Contrôle du thermostat de régulation\r\n[…] Contrôle du thermostat de sécurité\r\n[…] Contrôle aération haute et basse\r\n----------------------------------------\r\nBRULEUR\r\n[…] Couper le courant sur le coupe circuit, fermer le robinet de barrage gaz\r\n[…] Déconnecter l\'arrivée gaz, les fils électriques du bloc de régulation et la dérivation du thermocouple\r\n[…] Tirez le brûleur horizontalement\r\n[…] Contrôle du bon état des rampes\r\n[…] Contrôle du bon état des injecteurs\r\n[…] Contrôle de la veilleuse et du bon état de la bougie d\'allumage\r\n[…] Nettoyage du thermocouple\r\n[…] Contrôle du bon fonctionnement de l\'allumeur piézo\r\n[…] Contrôle de l\'étanchéité gaz\r\n[…] Contrôle du bon fonctionnement de la veilleuse après remise en service\r\n----------------------------------------\r\nCONDUIT GAZ\r\n[…] Nettoyage intérieur du conduit gaz\r\n[…] Nettoyage intérieur du coupe tirage\r\n[…] Contrôle de l\'étanchéité\r\n\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (28,'31.06.M','Ballon d\'eau chaude sanitaire ','[…] Contrôle absence de fuite\r\n[…] Contrôle du bon fonctionnement de la soupape de sûreté\r\n[…] Chasse par la vanne de vidange pour éliminer les éventuelles boues\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (29,'26.12.A','Batterie terminale eau glacée','[…] Nettoyage et désinfection du bac de récupération des condensats \r\n[…] Contrôle de l\'étanchéité des batteries\r\n[…] Relevé des pertes de charge du circuit eau batteries\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (30,'31.05.A','Ballon d\'eau chaude sanitaire ','[…] Analyse légionelle au robinet (Ost) Sur échantillonnage, points d\'usages les plus éloignés ou peu utilisés\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (31,'31.05.S','Ballon d\'eau chaude sanitaire ','[…] Contrôle de la régulation\r\n[…] Contrôle du point de consigne > 55°C\r\n[…] Contrôle de l\'isolement et de l\'intensité des résistances électriques\r\n[…] Réalisation d\'un choc thermique. Élévation de la température du ballon à 70°C pendant 30 mn\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (32,'60.04.M','Contrôle d\'accès','[…] Sauvegarde du programme',NULL,'0.25',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (33,'60.04.S','Contrôle d\'accès','[..] Opération sous traitée à _________________________________________\r\n\r\nContrat N° ____________________________',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (34,'410.01.T','Compacteur à déchets','[..] Contrôle visuel de l\'état général\r\n[..] Contrôle de la fixation de l\'alimentation électrique et de l\'altération du câble\r\n[..] Resserrage des connexions électriques \r\n[..] Essai de l\'appareil\r\n[..] Contrôle des sécurités et essai de l\'arrêt d\'urgence\r\n[..] Contrôle de l\'état des différents organes mécaniques visibles et accessibles et de l\'état des carters de protection\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (35,'25.03.T','Caloduc','[…] Remplacement des filtres selon besoin\r\n[…] Nettoyage de la batterie\r\n[…] Contrôle de la charge en fluide frigorigène\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (36,'25.03.A','Caloduc','[…] Nettoyage de la batterie\r\n[…] Contrôle de la charge en fluide frigorigène\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (37,'11.07.A','Canalis','[…] Suivi de la procédure de consignation\r\n[…] Contrôle de l\'isolement électrique\r\n[…] Contrôle du verrouillage et organes de manœuvre\r\n[…] Contrôle du serrage des connexions électriques\r\n[…] Suivi de la procédure de déconsignation\r\n\r\n------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (38,'26.07.S','Console à eau','[…] Contrôle de l\'état général\r\n[…] Contrôle du filtre et remplacement si nécessaire\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.05',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (39,'26.07.A','Console à eau','[…] Contrôle du fonctionnement des commutateurs Chaud/Froid/Ventilateur\r\n[…] Contrôle du fonctionnement du thermostat\r\n[…] Contrôle du fonctionnement de la régulation\r\n[…] Contrôle des connexions électriques\r\n[…] Contrôle des protections électriques\r\n[…] Contrôle et dépoussiérage de la batterie évaporateur\r\n[…] Vérification de l\'étanchéité des joints et des flexibles\r\n[…] Contrôle de l\'écoulement et pompe de relevage éventuelle\r\n[…] Nettoyage du bac à condensât\r\n[…] Contrôle du filtre et remplacement si nécessaire\r\n[…] Contrôle et dépoussiérage du moto ventilateur\r\n[…] Nettoyage complet de l\'unité intérieure\r\n[…] Contrôle de la vanne pressostatique\r\n[…] Vérification de l\'étanchéité des joints et des flexibles\r\n[…] Contrôle vanne d\'isolement\r\n[…] Relevé du compteur d\'eau\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (40,'26.06.A','Cassette plafonnière','[…] Contrôle du fonctionnement des commutateurs Chaud/Froid/Ventilateur\r\n[…] Contrôle du fonctionnement du thermostat\r\n[…] Contrôle du fonctionnement de la régulation\r\n[…] Contrôle des connexions électriques\r\n[…] Contrôle des protections électriques\r\n[…] Contrôle et dépoussiérage de la batterie évaporateur\r\n[…] Vérification de l\'étanchéité des joints et des flexibles\r\n[…] Contrôle de l\'écoulement et pompe de relevage éventuelle\r\n[…] Nettoyage du bac à condensât\r\n[…] Contrôle du filtre et remplacement si nécessaire\r\n[…] Contrôle et dépoussiérage du moto ventilateur\r\n[…] Nettoyage complet de l\'unité intérieure\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (41,'26.06.S','Cassette plafonnière','[…] Contrôle de l\'état général\r\n[…] Contrôle du filtre et remplacement si nécessaire\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.05',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (42,'51.10.A','Clapet coupe feu','[…] Contrôle du contact de fin de course et du report service de sécurité\r\n[…] Contrôle des asservissements\r\n[…] Contrôle des joints de scellement et des matériaux réfractaires\r\n[…] Vérification du fonctionnement de la commande manuelle\r\n[…] Enregistrement des essais et contrôles dans le registre de sécurité et sur BT préventif\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.25',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (43,'51.10.T','Clapet coupe feu','[…] Contrôle par simulation du bon fonctionnement des détecteurs et des fusibles\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.25',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (44,'A10001','Centrale d\'extinction incendie','[..] Opération sous traitée à _________________________________________\r\n\r\nContrat N° ____________________________\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,NULL,5,0,0,0,1,NULL,NULL,1,3,NULL),
 (45,'10.01.3A','Cellule Hautes tension','[…] Opération sous traitée à _________________________________________\r\n\r\nContrat N° ____________________________\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'6.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (46,'10.01.A','Cellule Hautes tension','[…] Suivi de la procédure de consignation \r\n[…] Dépoussiérage des cellules\r\n[…] Essai des reports GTB\r\n[…] Suivi de la procédure de déconsignation \r\n[…] Nettoyage du local technique\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (47,'27.01.S','Caisson d\'extraction d\'air','[…] Contrôle des raccordements sur la boite à bornes du moteur\r\n[…] Contrôle de l\'intensité et de l\'isolement du moteur de ventilation\r\n[…] Contrôle de l\'état de la tension des courroies\r\n[…] Contrôle de l\'alignement des poulies\r\n[…] Contrôle des roulements et graissage des paliers\r\n[…] Contrôle de la fixation des volutes\r\n[…] Graissage des registres et contrôle des moto-réducteurs\r\n[…] Contrôle de l\'état des soufflets et plots antivibratiles\r\n[…] Contrôle de la fixation des appareils de mesure et des liaisons équipotentielles\r\n[…] Si contractuel:  Entretien et ramonage des gaines d\'extraction d\'air vicié, de buée de graisse (Opération s/traitée)  \r\n[…] Mesure et enregistrement du débit global minimal d\'air extrait de l\'installation\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (48,'27.01.A','Caisson d\'extraction d\'air','[…] Nettoyage intérieur complet du caisson, ventilateurs, registres...\r\n[…] Nettoyage intérieur complet du circuit de récupération de chaleur si existant\r\n[…] Mesure et enregistrement de la pression statique ou de la vitesse d\'air aux points caractéristiques de l\'installation\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (49,'20.02 A','Chaudière électrique basse pre','[…] Contrôle état et manœuvre des vannes\r\n[…] Contrôle du débit et des sondes de températures départ/retour\r\n[…] Contrôle et essai des sécurités\r\n[…] Essai de soupapes de sécurité\r\n[…] Contrôle des connexions des résistances\r\n[…] Contrôle de l\'isolement des résistances\r\n[…] Contrôle de l\'intensité absorbée par les résistances\r\n\r\n-----------------------------------------------------------------------------------------------------\r\nSécurité\r\n-----------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-----------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (50,'20.04.S','Chaudière fioul  eau chaude ba','[…] Contrôle état et manœuvre des vannes\r\n[…] Contrôle débit et des sondes de températures départ/retour\r\n[…] Contrôle et essai des sécurités\r\n[…] Contrôle état du récupérateur de condensats\r\n[…] Contrôle état et nettoyage de la tête de combustion\r\n[…] Contrôle état et nettoyage de la cellule détection flamme et des électrodes d\'allumage\r\n[…] Contrôle état et nettoyage des filtres FOD\r\n[…] Contrôle étanchéité des raccords FOD à la pression de service \r\n[…] Contrôle connexions boite à bornes du moteur ventilateur\r\n[…] Graissage des paliers du moteur et du ventilateur\r\n[…] Contrôle du servomoteur, des volets et de la tringlerie du système modulant\r\n[…] Contrôle de la dépression foyer\r\n[…] Contrôle du tarage des soupapes de sécurité\r\n[…] Ramonage du conduit de fumées, du carneau et de la chaudière ( Opération sous traitée selon contrat N°        )\r\n[…] Contrôle état des réfractaires et de l\'étanchéité des portes et trappes de visites\r\n[…] Contrôle état du calorifuge\r\n[…] Mise à jour du livret de chaufferie\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'6.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (51,'20.04.T','Chaudière fioul  eau chaude ba','[…] Contrôle brûleur et analyse de la combustion (CO², CO,T°C fumées, indice de noircissement, rendement)\r\n\r\nChaudière neuve (mise en service après le 13/03/00) = Rendement : 89%\r\nChaudière existante Entre 400 et 2000kW = 85%\r\n                                 Entre 2000 et 10 000kW = 86%\r\n                                 Entre 10 000 et 50 000kW =87%      \r\n\r\n[…] Mise à jour du livret de chaufferie\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (52,'20.03.A','Chaudière gaz eau chaude basse','[…] Ramonage du conduit de fumées, du carneau et de la chaudière\r\n[…] Contrôle état des réfractaires et de l\'étanchéité des portes et trappes de visites\r\n[…] Contrôle état du calorifuge\r\n[…] Mise à jour du livret de chaufferie\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (53,'20.03.S','Chaudière gaz eau chaude basse','[…] Contrôle état et manœuvre des vannes\r\n[…] Contrôle débit et des sondes de températures départ/retour\r\n[…] Contrôle et essai des sécurités\r\n[…] Contrôle état du récupérateur de condensats\r\n[…] Contrôle état et nettoyage de la tête de combustion\r\n[…] Contrôle état et nettoyage de l’électrode d’ionisation ou de la cellule détection flamme et des électrodes d’allumage\r\n[…] Contrôle état et nettoyage des filtres gaz\r\n[…] Contrôle étanchéité des raccords gaz à la pression de service à l\'aide d\'un produit moussant\r\n[…] Contrôle connexions boite à bornes du moteur ventilateur\r\n[…] Graissage des paliers du moteur et du ventilateur\r\n[…] Contrôle du servomoteur, des volets et de la tringlerie du système modulant\r\n[…] Contrôle de la dépression foyer\r\n[…]Contrôle du tarage des soupapes de sécurité\r\n[…] Mise à jour du livret de chaufferie\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (54,'20.03.T','Chaudière gaz eau chaude basse','[…] Contrôle brûleur et analyse de la combustion (CO², CO,T°C fumées, indice de noircissement, rendement)\r\n\r\nChaudière neuve (mise en service après le 13/03/00)  = rendement : 90%\r\nChaudière existante  Entre 400 et 2000kW =rendement 86%\r\n                                  Entre 2000 et 10 000kW =rendement 87%\r\n                                  Entre 10 000 et 50 000kW =rendement 88%      \r\n\r\n[…] Mise à jour du livret de chaufferie\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (55,'20.05 S','Chaudière mixte fioul/gaz eau ','[…] Contrôle état et manœuvre des vannes\r\n[…] Contrôle débit et des sondes de températures départ/retour\r\n[…] Contrôle et essai des sécurités\r\n[…] Contrôle état du récupérateur de condensats\r\n[…] Contrôle état et nettoyage de la tête de combustion\r\n[…] Contrôle état et nettoyage de la cellule détection flamme et des électrodes d\'allumage\r\n[…] Contrôle état et nettoyage des filtres FOD\r\n[…] Contrôle étanchéité des raccords FOD à la pression de service \r\n[…] Contrôle connexions boite à bornes du moteur ventilateur\r\n[…] Graissage des paliers du moteur et du ventilateur\r\n[…] Contrôle du servomoteur, des volets et de la tringlerie du système modulant\r\n[…] Contrôle de la dépression foyer\r\n[…] Contrôle du tarage des soupapes de sécurité\r\n[…] Ramonage du conduit de fumées, du carneau et de la chaudière ( Opération sous traitée  selon contrat N°        )\r\n[…] Contrôle état des réfractaires et de l\'étanchéité des portes et trappes de visites\r\n[…] Contrôle état du calorifuge\r\n[…] Mise à jour du livret de chaufferie\r\n\r\n--------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n--------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n--------------------------------------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (56,'20.05 T','Chaudière mixte fioul/gaz eau ','[…] Contrôle brûleur et analyse de la combustion (CO², CO,T°C fumées, indice de noircissement, rendement)\r\n\r\nChaudière neuve (mise en service après le 13/03/00) = Rendement : 89%\r\nChaudière existante Entre 400 et 2000kW = 85%\r\n                                 Entre 2000 et 10 000kW = 86%\r\n                                 Entre 10 000 et 50 000kW =87%      \r\n\r\n[…] Mise à jour du livret de chaufferie\r\n\r\n--------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n--------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n--------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (57,'20.06 S','Chaudière vapeur','[…] Contrôle état et nettoyage des filtres\r\n[…] Contrôle étanchéité des raccords gaz à l\'aide d\'un produit moussant et FOD à la pression de service \r\n[…] Contrôle connexions boite à bornes du moteur ventilateur\r\n[…] Graissage des paliers du moteur et du ventilateur\r\n[…] Contrôle du servomoteur, des volets et de la tringlerie du système modulant\r\n[…] Contrôle de la dépression foyer\r\n[…]  Essai des soupapes de sécurité par soulèvement des contrepoids\r\n[…] Dépose des tampons autoclaves d\'accès aux trous d\'hommes\r\n[…] Dépose de la trappe d\'accès à la chambre de combustion, le cas échéant dépose du brûleur\r\n[…] Dépose des panneaux boulonnés le long du faisceau de convection\r\n[…] Nettoyage sous pression des parois rendus accessibles\r\n[…] Remontage et remplacement des joints\r\n[…] Contrôle état des réfractaires et de l\'étanchéité des portes et trappes de visites\r\n[…] Contrôle état du calorifuge\r\n[…] Ramonage du conduit de fumées, du carneau de la chaudière (Opération sous traitée)\r\n\r\n--------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n--------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n--------------------------------------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (58,'20.06.T','Chaudière vapeur','[…] Analyse physico chimique par un laboratoire spécialisé (PH, TH, TCL, SiO2, Na2S03,Fe, Cu, salinité)\r\n[…] Contrôle brûleur et analyse de la combustion (CO², CO, T°C fumées ,indice de noircissement, rendement)\r\n[…] Contrôle état et manœuvre des vannes\r\n[…] Contrôle de la régulation de remplissage\r\n[…] Essai des sécurités et du dispositif de détection gaz\r\n[…] Contrôle état et nettoyage de la tête de combustion\r\n[…] Contrôle état et nettoyage de l’électrode d’ionisation ou cellule détection flamme et des électrodes d’allumage\r\n\r\n--------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n--------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n--------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL);
INSERT INTO `gamme` (`game_seq`,`game_code`,`game_libelle`,`game_contenu`,`game_consiparti`,`game_dureepres`,`game_dureejour`,`game_verte`,`game_stopservic`,`game_gen_diff`,`game_bool_inactive`,`game_bdocument`,`game_maj_gene`,`game_tope_fk`,`game_dom_fk`,`game_tdef_fk`) VALUES 
 (59,'23.07.S','Circulateur (Sans accouplement','[…] Contrôle de la boite à bornes moteur\r\n[…] Contrôle de l\'intensité absorbée et de l\'isolement du moteur\r\n[…] Contrôle des liaisons équipotentielles de masse\r\n[…] Relevé du delta P de la pompe\r\n[…] Contrôle des roulements\r\n[…] Contrôle de la fixation et des supports antivibratiles\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (60,'20.01 A','Chaudière murale','[…] Contrôle des points de consignes\r\n[…] Contrôle état et manœuvre des vannes\r\n[…] Nettoyage du corps de chauffe\r\n[…] Contrôle étanchéité des raccords gaz\r\n[…] Contrôle de l\'état du récupérateur de condensats  \r\n[…] Contrôle état et nettoyage de la cellule détection flamme     \r\n[…] Contrôle état et nettoyage des électrodes d\'allumage     \r\n[…] Contrôle de l\'apport d\'air neuf     \r\n[…] Essai des sécurités\r\n[…] Ramonage du conduit de fumée ( Opération sous traitée selon contrat N°                       )',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (61,'51.02.A','Extinction automatique CO2','[…] Contrôle des EPI (masque respiratoire) suivant notice constructeur\r\n[…] Tous les 10 ans: Révision de l\'installation par installateur ou organisme qualifié APSAD\r\n[…] Date de la dernière révision:……………..\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (62,'51.02.S','Extinction automatique CO2','[…] Contrôle de la charge ou de la pression des réservoirs\r\n[…] Vérification fonctionnelle des vannes\r\n[…] Vérification fonctionnelle sans émission : des commandes manuelles (bris de glace), des commandes automatiques (détecteurs) \r\n[…] Contrôle de l\'état des flexibles, diffuseurs, canalisations\r\n[…] Contrôle des signaux sonores et visuels (alarme 1 ton, 2 tons, panneaux lumineux)\r\n[…] Contrôle du dispositif de retardement (temporisation < 1 minute)\r\n[…] Vérification fonctionnelle du système d\'arrêt automatique de la ventilation\r\n[…] Vérification fonctionnelle du désenfumage\r\n[…] Vérification fonctionnelle de la fermeture automatique des PCF, CCF, VCF\r\n[…] Contrôle du fonctionnement des alarmes et de leur report\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (63,'11.10.A','Coffret électrique','[…] Essai Auto/Arrêt/Manu\r\n[…] Contrôle de la présence du schéma dans le coffret électrique. Remise à jour du schéma si nécessaire\r\n[…] Essai arrêt d\'urgence\r\n[…] Suivi de la procédure de consignation \r\n[…] Contrôle connexions et bruits et fixations des relais\r\n[…] Essai des reports et télécommandes GTB\r\n[…] Contrôle du serrage des connexions\r\n[…] Contrôle du réglage des relais thermiques par rapport au schéma\r\n[…] Contrôle des temporisations\r\n[…] Contrôle état des goulottes\r\n[…] Contrôle état des presse étoupes\r\n[…] Contrôle fixation du coffret\r\n[…] Nettoyage et dépoussiérage\r\n[…] Suivi de la procédure de déconsignation\r\n\r\n--------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (64,'11.06.A','Colonne montante','[…]  Suivi de la procédure de consignation\r\n------------------------------------------------------------------------------------------------------------------------------------\r\nPied de colonne\r\n[…] Contrôle du serrage des connexions du pied de colonne\r\n[…] Nettoyage et dépoussiérage\r\n------------------------------------------------------------------------------------------------------------------------------------\r\nCoffrets de raccordement\r\n[…] Contrôle de l\'embrochage des coffrets \r\n[…] Contrôle du serrage des connexions de dérivation \r\n[…] Suivi de la procédure de déconsignation\r\n\r\n------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (65,'11.03.A','Batteries de condensateurs','[…] Contrôle de la disponibilité\r\n[…] Contrôle des connexions  ATTENTION A LA CHARGE DES CONDENSATEURS\r\n[…] Dépoussiérage, nettoyage\r\n[…] Contrôle de l\'état des contacteurs\r\n[…] Contrôle de la régulation varmétrique  TG PHI < 0,4\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (66,'24.05.A','Cordon chauffant','[…] Contrôle de la consigne\r\n[…] Contrôle du fonctionnement de la régulation et des sécurités\r\n[…] Contrôle des connexions électriques\r\n[…] Contrôler la qualité diélectrique du cordon à 500 V (supérieur à 10 Mégohms entre T et conducteurs)  \r\n[…] Contrôler l\'intensité et la tension sur le départ du tableau basse tension\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (67,'51.04.A','Colonnes sèches','[…] Contrôle de l\'état du revêtement extérieur Contrôle réglementaire (opération sous- traitée) NF S 61-750\r\n[…] Essai de mise en eau (à prévoir et à exécuter en accord avec le centre de secours)\r\n\r\nOpération sous traitée à _________________________________________\r\n\r\nContrat N° ____________________________\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (68,'51.04.S','Colonnes sèches','Prises\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n[…] Vérification de l\'accessibilité aux prises et aux raccords\r\n[…] Contrôle de la présence des bouchons de prise et de fermeture\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nColonnes\r\n[…] Vérification de l\'absence de corps étrangers dans la colonne\r\n[…] Vérification de la présence de la signalisation\r\n[…] Vérification fonctionnelle\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (69,'A10002','Sous station CPCU','Local chaufferie\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n[…] Contrôle de la bonne ventilation du local\r\n[…] Contrôle de l\'état de l\'éclairage normal et secours\r\n[…] Retouche de peinture (Selon besoin)\r\n[…] Contrôle de l\'étanchéité des presses étoupe, brides et vannes\r\n[…] Contrôle de l\'état des matelas et calorifuges\r\n[…] Contrôle des indicateurs de conduite\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nBouteille de détente\r\n[…] Contrôle de la température départ\r\n[…] Contrôle de la pression départ HP\r\n[…] Contrôle de l\'état du filtre à tamis  (Selon besoin)\r\n[…] Contrôle de la régulation HP (Vanne de détente)\r\n[…] Contrôle des sécurités HP\r\n[…] Contrôle du purgeur de sécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEchangeur\r\n[…] Contrôle de la température départ secondaire\r\n[…] Contrôle de la pression secondaire\r\n[…] Contrôle de la régulation condensat\r\n[…] Contrôle des organes de sécurité(thermostats, pressostats, soupapes) et purgeurs\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nBâche\r\n[…] Contrôle de l\'état général de la bâche\r\n[…] Contrôle des flotteurs bac de condensât   \r\n[…] Contrôle du bon fonctionnement pompe condensât \r\n[…] Contrôle des connexions électriques pompe condensât \r\n[…] Contrôle du clapet,  manchon et support anti vibratile\r\n[…] Contrôle du bon écoulement des eaux de condensation\r\n[…] Nettoyage de la bâche si nécessaire\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nCoffret de régulation\r\n[…] Contrôle du serrage des connexions\r\n[…] Contrôle état des goulottes\r\n[…] Contrôle état des presse étoupe\r\n[…] Contrôle fixation du coffret\r\n[…] Nettoyage et dépoussiérage\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nPompe puisard\r\n[…] Nettoyage de la fosse si nécessaire\r\n[…] Contrôle du bon fonctionnement de la pompe \r\n[…] Contrôle des connexions électriques pompe\r\n[…] Contrôle de l\'organe de coupure\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,NULL,5,0,0,0,1,NULL,NULL,1,3,NULL),
 (70,'25.01.T','Centrale de traitement d\'air','-------------------------------------------------------------------------------------------------------------------------------------\r\nCOMPARTIMENT FILTRATION\r\n[…] Remplacement des filtres si la perte de charge est supérieure à la recommandation du constr',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (71,'25.01.A','Centrale de traitement d\'air','REGULATION\r\n[…] Dépoussiérage des cartes ou des régulateurs\r\n[…] Contrôle serrage des connexions\r\n[…] Vérification des points de consignes\r\n[…] Vérification des valeurs de gain en proportionnel, intégral et dérivé\r\n[…] Contrôle de l\'état de fonctionnement des actionneurs\r\n[…] Contrôle de l\'état et de la cohérence des indications des capteurs\r\n[…] Contrôle des lois de régulations\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nMESURES\r\n[…] Mesure et enregistrement des performances\r\n[…] Mesure et enregistrement de la pression statique ou de la vitesse d\'air aux points caractéristiques de l\'installation\r\n[…] Mesure et enregistrement du débit global minimal d\'air neuf de l\'installation\r\n[…] Consignation des interventions dans le livret d\'entretien\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (72,'25.01.S','Centrale de traitement d\'air','-------------------------------------------------------------------------------------------------------------------------------------\r\nCAISSONS\r\n[…] Nettoyage intérieur complet du caisson, ventilateurs, batteries, registres...\r\n[…] Contrôle de l\'état des ',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (73,'20.09.A','Cuve à fuel','\r\n[…] Contrôle de l\'état des supports, de la cuve et des tuyauteries (corrosion, revêtement)\r\n[…] Contrôle du fonctionnement des détecteurs de fuite et des reports d\'alarme\r\n[…] Contrôle des limiteurs de remplissage\r\n[…] Vérification de la jauge de remplissage\r\n[…] Contrôle de la date de réépreuve\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (74,'24.06.A','Convecteur électrique','[…] Contrôle des fixations\r\n[…] Contrôle de l\'isolement\r\n[…] Contrôle du thermostat et de la régulation \r\n[…] Vérification des raccordements et de l\'état des câbles\r\n[…] Dépoussiérage et nettoyage \r\n[…] Contrôle de la programmation horaire\r\n[…] Contrôle de la liaison à la terre\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (75,'50.03.A','Détection CO Parking','[..] Opération sous traitée à _________________________________________\r\n\r\nContrat N° ____________________________',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (76,'A10003','Détection d\'eau','[…] Opération sous  traité selon contrat N°\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'3.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (77,'51.11.S','Ventilateur de désenfumage','[…] Contrôle de l\'état général\r\n[…] Contrôle de la turbine et du jeu d\'arbre\r\n[…] Contrôle de l\'état de la protection mécanique des courroies\r\n[…] Contrôle de l\'état de la tension des courroies\r\n[…] Contrôle de l\'alignement des poulies\r\n[…] Contrôle des roulements et graissage des paliers\r\n[…] Contrôle des raccordements sur la boite à borne moteur\r\n[…] Contrôle de l\'intensité et de l\'isolement du moteur\r\n[…] Contrôle de l\'état de la cage ou des grilles\r\n[…] Contrôle de la fixation du ventilateur et du moteur\r\n[…] Contrôle de l\'état des plots antivibratiles\r\n[…] Nettoyage complet\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (78,'51.11.T','Ventilateur de désenfumage','[…] Essai du ventilateur, du coffret de relayage   (Dans les IGH, l\'essai trimestriel doit être effectué par le service de sécurité)\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (79,'60.02.A','Digicode','[…] Contrôle de la fixation du boîtier\r\n[…] Contrôle des lignes et des impédances\r\n[…] Contrôle du fonctionnement de la gâche électrique\r\n[…] Essai de l\'installation\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (80,'30.06.A','Disconnecteur','[..] Opération sous traitée à _________________________________________\r\n\r\nContrat N° ____________________________',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (81,'21.05.A','Dry cooler','[…] Contrôle des ventilateurs (fixation, graissage)\r\n[…] Contrôle de l\'état des hélices\r\n[…] Nettoyage et peignage des batteries\r\n[…] Contrôle et examen des ailettes des batteries\r\n[…] Contrôle de l\'état des manchons et plots anti-vibratiles\r\n[…] Contrôle du supportage et de la carrosserie\r\n[…] Contrôle de l\'état de la carrosserie\r\n[…] Contrôle de l\'état des canalisations\r\n[…] Contrôle de l\'isolement et de l\'intensité absorbée des moteurs\r\n[…] Resserrage des connexions électriques\r\n[…] Contrôle de la régulation\r\n[…] Mesure des performances (Lors de l\'identification d\'un dysfonctionnement.)\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (82,'23.12.S','Echangeur','\r\n[…] Contrôle des presses étoupes des vannes\r\n[…] Manœuvre des vannes d\'isolement\r\n[…] Contrôle du calorifuge\r\n[…] Contrôle de la perte de charge primaire\r\n[…] Contrôle de la perte de charge secondaire\r\n[…] Nettoyage du filtre  (Si nécessaire)\r\n[…] Détartrage mécanique ou chimique selon P et spécification du constructeur  (Si nécessaire)\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (83,'31.01.T','Réseaux eau chaude sanitaire','[…] Contrôle des filtres\r\n[…] Contrôle du TH ( 8 < TH < 15 )\r\n[…] Contrôle de la température au point de puisage le plus éloigné\r\n[…] Chasses aux extrémités de boucle et sur les zones à faible débit\r\n[…] Relevé de la consommation en produit de traitement\r\n[…] Contrôle et réglage, si nécessaire, de l\'injection en produit de traitement (mg produit/litre)\r\n[…] Contrôle des calorifuges\r\n[…] Analyse physico-chimique de l\'eau et des dépôts\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (84,'31.01.A','Réseaux eau chaude sanitaire','[…] Contrôle de l\'état des tuyauteries après démontage des manchettes témoins\r\n[…] Rinçage des bypasses\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (85,'30.01.S','Réseaux eau froide','[…] Contrôle de l\'état des tuyauteries après démontage des manchettes témoins\r\n[…] Rinçage des bypasses\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (86,'30.01.T','Réseaux eau froide','[…] Contrôle des filtres\r\n[…] Contrôle de l\'état externe des canalisations\r\n[…] Contrôle du bon fonctionnement détendeurs, réducteurs de pression\r\n[…] Contrôle des anti béliers\r\n[…] Chasses sur l\'ensemble des points bas et sur les points d\'usage à faibles débits\r\n[…] Analyse physico-chimique\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (87,'26.10.A','Ejecto-convecteur','[…] Contrôle et dépoussiérage des batteries\r\n[…] Contrôle de l\'état des buses\r\n[…] Purge de l\'air dans la batterie\r\n[…] Contrôle évacuation condensats et nettoyage du bac\r\n[…] Contrôle du bon fonctionnement de la vanne d\'air\r\n[…] Contrôle calorifuge et état extérieur\r\n[…] Contrôle encombrement et comportement utilisateur \r\n\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.05',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (88,'26.10.S','Ejecto-convecteur','[…] Contrôle de l\'état général\r\n[…] Contrôle du filtre et remplacement si nécessaire\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.05',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (89,'12.02.A','Enseigne','[…] Contrôle du bon fonctionnement de l\'interrupteur crépusculaire\r\n[…] Contrôle de la programmation horaire\r\n[…] Contrôle de la coupure de proximité\r\n[…] Contrôle de l\'état du câblage\r\n[…] Contrôle de la fixation de l\'enseigne\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\nPrésence de haute tension possible\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (90,'110.02.A','Réseaux d\'évacuation EU/EV/EP','[…] Contrôle de l\'étanchéité des joints, absence de fuite\r\n[…] Nettoyage des regards et siphons de sol\r\n[…] Contrôle du bon écoulement des eaux\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (91,'23.10.A','Vase et réservoir d\'expansion ','[…] Contrôle de la pression de gonflage \r\n[…] Contrôle de la date d\'épreuve de l\'appareil sous pression \r\n[…] Date de la dernière épreuve:……………………\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (92,'51.03.A','Extincteurs Mobiles','[…] Opération sous traitée à _________________________________________\r\n\r\nContrat N° ____________________________\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.10',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (93,'51.03.T','Extincteur mobile','[…] Vérification de la présence et accessibilité des extincteurs à leur emplacement\r\n[…] Vérification de leur état extérieur \r\n- présence du plombage \r\n- présence de l\'étiquette avec le nom du vérificateur\r\n- état du corps et de la lance \r\n- diffuseur non obstrué\r\n- dispositif de verrouillage intact',NULL,'0.10',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (94,'51.07.S','Exutoire de fumées','[…] Contrôle de l\'alimentation électrique ou pneumatique\r\n[…] Vérification fonctionnelle de la commande manuelle\r\n[…] Contrôle de l\'état de la sparklet\r\n[…] Contrôle des joints de scellement et des matériaux réfractaires\r\n[…] Contrôle mécanique des pièces en mouvement\r\n[…] Essai des exutoires\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (95,'100.03.A','Fenêtre','[...] Contrôle de l\'aspect général \r\n[...] Contrôle des joints d\'étanchéité\r\n[...] Vérification des fixations\r\n[...] Contrôle des crémones et serrureries\r\n[...] Lubrification des parties mécaniques\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.10',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (96,'23.06.A','Filtre à tamis','[…] Nettoyage du tamis\r\n[…] Contrôle des joints de brides et remplacement si nécessaire\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (97,'10.05.AI','Groupe électrogène','[…]  Opération sous traitée à _________________________________________\r\n\r\nContrat N° ____________________________\r\n\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (98,'10.05.AM','Groupe électrogène','[…]  Opération sous traitée à _________________________________________\r\n\r\nContrat N° ____________________________\r\n\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (99,'10.05.M','Groupe électrogène','[…] \"Essai de démarrage automatique avec une charge minimale de 50% de la puissance du Groupe pendant 30 mn\" \r\n\r\nLorsque le groupe dessert les installations de sécurité\r\n\r\n[…] Contrôle niveau huile moteur\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (100,'10.05.AE','Groupe électrogène','[…]  Opération sous traitée à _________________________________________\r\n\r\nContrat N° ____________________________\r\n\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (101,'21.02.A','Groupe frigorifique centrifuge','[…] Contrôle de l\'étanchéité des circuits frigorifiques >2 Kg\r\n\r\nAttention remplir le certificat de recherche de fuite annuelle\r\n\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEnvironnement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nAttention pour toute intervention sur le circuit frigorifique remplir une fiche d\'intervention sur circuit frigorifique',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (102,'21.02.S','Groupe frigorifique centrifuge','\r\n[…] Contrôle du fonctionnement général\r\n[…] Intervention Sous traitance :\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEnvironnement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nAttention pour toute intervention sur le circuit frigorifique remplir une fiche d\'intervention sur circuit frigorifique',NULL,NULL,5,0,0,0,1,NULL,NULL,1,3,NULL),
 (103,'21.01.A','Groupe frigorifique à piston','\r\n[…] Contrôle de l\'étanchéité des circuits frigorifiques >2 Kg\r\n\r\nAttention remplir le certificat de recherche de fuite annuelle\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEnvironnement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nAttention pour toute intervention sur le circuit frigorifique remplir une fiche d\'intervention sur circuit frigorifique',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (104,'21.01.S','Groupe frigorifique à piston','\r\n[…] Contrôle du fonctionnement général\r\n[…] Contrôle de la charge en fluide frigorigène\r\n[…] Contrôle des pertes de charges du condenseur et de l\'évaporateur\r\n[…] Essai des pressostats HP/BP\r\n[…] Essai de la sonde de présence d\'eau évaporateur\r\n[…] Essai du thermostat antigel\r\n[…] Contrôle des intensités absorbées\r\n[…] Contrôle de l’état de la ou des batterie(s)\r\n[…] Contrôle de l’état du ou des ventilateur(s)\r\n[…] Contrôle des connexions électriques des compresseurs\r\n[…] Contrôle de l\'isolement des compresseurs\r\n[…] Changement du déshydrateur\r\n[…] Test de l\'acidité de l\'huile\r\n[…] Contrôle des plots anti-vibratiles\r\n[…] Contrôle des manchons de dilatation\r\n[…] Vidange en fonction des nombres d\'heures de fonctionnement ou de résultat négatif des tests d\'acidité\r\n[…] Contrôle de l\'état de calorifuges\r\n[…] Mesure des performances\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEnvironnement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nAttention pour toute intervention sur le circuit frigorifique remplir une fiche d\'intervention sur circuit frigorifique',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (105,'21.04.A','Groupe frigorifique scroll','[…] Contrôle de l\'étanchéité des circuits frigorifiques >2 Kg\r\n\r\nAttention remplir le certificat de recherche de fuite annuelle\r\n\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEnvironnement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nAttention pour toute intervention sur le circuit frigorifique remplir une fiche d\'intervention sur circuit frigorifique',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (106,'21.04.S','Groupe frigorifique scroll','\r\n[…] Contrôle du fonctionnement général\r\n[…] Intervention Sous traitance :\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEnvironnement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nAttention pour toute intervention sur le circuit frigorifique remplir une fiche d\'intervention sur circuit frigorifique',NULL,NULL,5,0,0,0,1,NULL,NULL,1,3,NULL),
 (107,'21.03.A','Groupe frigorifique à vis','[…] Contrôle de l\'étanchéité des circuits frigorifiques >2 Kg\r\n\r\nAttention remplir le certificat de recherche de fuite annuelle\r\n\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEnvironnement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nAttention pour toute intervention sur le circuit frigorifique remplir une fiche d\'intervention sur circuit frigorifique',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (108,'21.03.S','Groupe frigorifique  à vis','\r\n[…] Contrôle du fonctionnement général\r\n[…] Intervention Sous traitance :\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEnvironnement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nAttention pour toute intervention sur le circuit frigorifique remplir une fiche d\'intervention sur circuit frigorifique',NULL,NULL,5,0,0,0,1,NULL,NULL,1,3,NULL),
 (109,'60.05.H','Gestion technique centralisé','\r\n[…] Analyse des informations au fil de l’eau et déclenchement des interventions\r\n[…] Vérification des points de consignes\r\n[…] Edition des journaux d’alarmes, des analyses et des relevés sous tendance\r\n[…] Optimisation du fonctionnement des installations par téléréglage\r\n[…] Modification des programmes horaires\r\n[…] Création de points ponctuels, de synthèses ou de groupes de commande',NULL,NULL,5,0,0,0,1,NULL,NULL,1,3,NULL),
 (110,'60.05.M','Gestion technique centralisé','[…] Sauvegarde du programme',NULL,NULL,5,0,0,0,1,NULL,NULL,1,3,NULL),
 (111,'60.05.T','Gestion technique centralisé','\r\n[…] Contrôle des réseaux de communication entre le superviseur et les sous-stations\r\n[…] Analyse de l’historique et des événements survenus\r\n[…] Purge des fichiers\r\n[…] Sauvegarde système\r\n[…] Mise à jour logiciel',NULL,NULL,5,0,0,0,1,NULL,NULL,1,3,NULL),
 (112,'A10004','Hotte de cuisine','[…] Intervention sous traitée et obligatoire en raison  du décrets des installations alimentées au gaz\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,NULL,5,0,0,0,1,NULL,NULL,1,3,NULL),
 (113,'26.13.A','Humidificateur','LAVEUR A RUISSELLEMENT\r\n[…] Analyse d\'eau pour recherche légionella\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nATOMISEUR\r\n[…] Analyse d\'eau pour recherche légionella\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (114,'26.13.T','Humidificateur','LAVEUR A RUISSELLEMENT\r\n[…] Contrôle du taux de déconcentration\r\n[…] Contrôle de la pompe de recyclage\r\n[…] Contrôle et manœuvre du système de vidange automatique\r\n[…] Contrôle flotteur et électrovanne d\'alimentation automatique en eau\r\n[…] Contrôle et nettoyage des buses de pulvérisation\r\n[…] Contrôle de l\'étanchéité du bac\r\n[…] Nettoyage et désinfection du bac par solution chlorée. Les équipements doivent être nettoyés et désinfectés avec une solution de chlore concentré à 50 milligrammes de chlore libre par litre d\'eau froide\r\n[…] Contrôle de l\'état des nids d\'abeilles\r\n[…] Dépose des nids d’abeilles en cas d\'arrêt\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nATOMISEUR\r\n[…] Vidange, nettoyage sommaire et contrôle de l\'étanchéité du bac\r\n[…] Contrôle de l\'étanchéité des raccordements pneumatiques\r\n[…] Contrôle et nettoyage des buses d\'injection\r\n[…] Contrôle flotteur et électrovanne d\'alimentation automatique en eau\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nVAPEUR\r\n[…] Vidange des humidificateurs en période de non humidification\r\n[…] Contrôle de l\'intensité nominale et de l\'isolement des électrodes\r\n[…] Contrôle et nettoyage des buses d\'injection\r\n[…] Contrôle flotteur et électrovanne d\'alimentation automatique en eau\r\n[…] Contrôle et manœuvre du système de vidange automatique\r\n[…] Contrôle de l\'étanchéité des raccordements vapeur\r\n[…] Nettoyage de la cuve et des électrodes\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (115,'32.01.A','Séparateur d\'hydrocarbure','[..] Opération sous traitée à _________________________________________\r\n\r\nContrat N° ____________________________',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (116,'60.01.A','Interphonie','[…] Contrôle des liaisons d\'écoute\r\n[…] Contrôle des connexions électriques\r\n[…] Contrôle des lignes et des impédances\r\n[…] Essai de l’installation\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (117,'11.02.A','Inverseur de source','[…] Essai des commutateurs de sélection S1/S2\r\n[…] Essai de l\'inversion des sources\r\n[…] Contrôle de l\'intensité générale et de la tension sur chaque phase\r\n[…] Contrôle de l\'équilibrage des phases\r\n[…] Contrôle du réglage des temporisations\r\n[…] Contrôle du relayage général (bruit, fixation…)\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (118,'12.01.M','Source lumineuse et appareilla','[…] Remplacement ponctuel des sources lumineuses défectueuses\r\n[…] Remplacement ponctuel des prises de courant, interrupteurs et boutons poussoir défectueux\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (119,'105.06.A','Mobilier armoire','[...] Ouverture fermeture des portes\r\n[...] Contrôle des glissières\r\n[...] Contrôle des serrures\r\n[...] Contrôle de la stabilité de l\'armoire\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.10',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (120,'100.05.A','Mobilier bureaux','[...] Ouverture et fermeture des tiroirs\r\n[...] Contrôle des pieds de bureaux\r\n[...] Contrôle des serrures\r\n[...] Contrôle de la fixation et ancrage\r\n[...] Contrôle de la stabilité du bureau\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.10',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (121,'26.11.A','Moduline','[…] Contrôle de la régulation, du bilame\r\n[…] Nettoyage\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.15',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (122,'30.09.S','Maintien de pression','[…]Contrôle du pressostat de commande\r\n[…]Contrôle des pressions d\'asservissement et des report d\'alarme\r\n[…]Contrôle de la boite à bornes moteur\r\n[…]Contrôle de l\'intensité moteur\r\n[…]Contrôle de l\'isolement et des liaisons équipotentielles\r\n[…]Dépoussiérage du ventilateur de refroidissement du moteur\r\n[…]Contrôle des roulements et graissage éventuel\r\n[…]Contrôle de l\'accouplement\r\n[…]Contrôle de la protection mécanique des parties tournantes\r\n[…]Contrôle de la fixation de l\'ensemble et des plots antivibratiles\r\n[…]Contrôle du filtre à tamis et nettoyage éventuel\r\n[…]Contrôle du fonctionnement du clapet anti-retour\r\n[…]Contrôle des déverseurs\r\n[…]Vidange et rinçage de la bâche\r\n[…]Remplacement de la signalisation si nécessaire\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (123,'26.04.A','Module de traitement d\'air','[…] Contrôle de l\'état des raccordements hydrauliques et des calorifuges\r\n[…] Contrôle de l\'état et nettoyage du conduit d\'évacuation des condensats\r\n[…] Contrôle de l\'état de la connectique de la platine de régulation et de commande\r\n[…] Contrôle de l\'état des câbles d\'alimentation électrique\r\n[…] Contrôle du filtre et remplacement si nécessaire\r\n[…] Contrôle du fonctionnement du moto-ventilateur\r\n[…] Contrôle du fonctionnement de la régulation et des vannes motorisées\r\n[…] Contrôle et enregistrement de tous les paramètres de fonctionnement\r\n[…] Essai des commandes groupées et des reports d\'information GTB\r\n[…] Essai des disjoncteurs différentiels\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (124,'26.04.S','Module de traitement d\'air','[…] Contrôle de l\'état général\r\n[…] Contrôle du filtre et remplacement si nécessaire\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.05',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (125,'70.01.T','Nacelle de nettoyage','[…] Opération sous  traité selon contrat N°\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (126,'410.02.S','Nettoyage centralisé par le vi','TURBINE - MOTEUR\r\n[...] Contrôle des connexions électriques\r\n[...] Contrôle des raccordements sur la boite à bornes du moteur\r\n[...] Contrôle de l\'intensité absorbée du moteur et comparaison par rapport à l\'intensité nominale constructeur\r\n[...] Contrôle de l\'isolement moteur\r\n[...] Contrôle du calibrage des fusibles et du réglage de la protection thermique\r\n[...] Contrôle de l\'état et de la tension des courroies\r\n[...] Contrôle de l\'alignement des poulies\r\n[...] Contrôle des roulements et graissage paliers (50heures)\r\n[...] Contrôle des organes de serrage\r\n[...] Contrôle de l\'état des soufflets et plots antivibratiles\r\n[...] Contrôle des liaisons équipotentielles\r\n[...] Nettoyage complet turbine, moteur et cartouche filtre\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (127,'410.02.T','Nettoyage centralisé par le vi','CAISSON DE DEPOUSSIERAGE PRIMAIRE A VOIE HUMIDE\r\n[...] Contrôle de la propreté et du niveau d\'eau\r\n[...] Contrôle de l\'état et nettoyage, des crépines d\'aspiration\r\n[...] Contrôle de l\'encrassement et vidange des poussières\r\n[...] Contrôle de l\'étanchéité des portes\r\n[...] Contrôle du traitement des surfaces des parois internes\r\n[...] Contrôle de la vanne de vidange et de son étanchéité et du réglage de la protection thermique\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nCAISSON DE DEPOUSSIERAGE SECONDAIRE A VOIE HUMIDE\r\n[...] Contrôle de la propreté et du niveau d\'eau\r\n[...] Contrôle de l\'encrassement et vidange des poussières\r\n[...] Contrôle de l\'état et nettoyage, des crépines d\'aspiration\r\n[...] Contrôle des purges et de leurs étanchéités\r\n[...] Contrôle du traitement des surfaces des parois internes\r\n[...] Contrôle de la vanne de vidange et de son étanchéité\r\n\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (128,'10.06.A','Onduleur','[…] Opération sous  traité selon contrat N°\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL);
INSERT INTO `gamme` (`game_seq`,`game_code`,`game_libelle`,`game_contenu`,`game_consiparti`,`game_dureepres`,`game_dureejour`,`game_verte`,`game_stopservic`,`game_gen_diff`,`game_bool_inactive`,`game_bdocument`,`game_maj_gene`,`game_tope_fk`,`game_dom_fk`,`game_tdef_fk`) VALUES 
 (129,'10.06.M','Onduleur','[…] Contrôle de la ventilation et remplacement du filtre si nécessaire\r\n[…] Contrôle état des batterie, absence de fuite.\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (130,'25.02.A','Pompe à chaleur','[…] Contrôle étanchéité éléments constituant le confinement des fluides frigorigènes >2 Kg\r\n\r\nAttention remplir le certificat de recherche de fuite annuelle\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEnvironnement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nAttention pour toute intervention sur le circuit frigorifique remplir une fiche d\'intervention sur circuit frigorifique',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (131,'25.02.S','Pompe à chaleur','[…] Contrôle de la régulation\r\n[…] Contrôle des pressostats HP/BP\r\n[…] Contrôle de la sonde d\'eau condenseur/évaporateur\r\n[…] Contrôle du thermostat antigel\r\n[…] Contrôle du réglage du détendeur\r\n[…] Contrôle de l\'intensité des compresseurs\r\n[…] Contrôle de l\'isolement des compresseurs\r\n[…] Remplacement du déshydrateur\r\n[…] Contrôle de l\'acidité de l\'huile\r\n[…] Contrôle des plots antivibratiles\r\n[…] Contrôle des manchons de dilatation\r\n[…] Contrôle de l\'état des calorifuges\r\n[…] Contrôle des connexions électriques\r\n[…] Mesure des performances\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEnvironnement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nAttention pour toute intervention sur le circuit frigorifique remplir une fiche d\'intervention sur circuit frigorifique',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (132,'26.03.S','Pompe à chaleur (Sur boucle)','[…] Contrôle du filtre et remplacement si nécessaire\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.05',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (133,'26.03.A','Pompe à chaleur (Sur boucle)','[…] Contrôle du fonctionnement de la régulation et des sécurités\r\n[…] Contrôle du fonctionnement du thermostat \r\n[…] Contrôle de la commande Chaud/Froid/Vitesse ventilateur\r\n[…] Contrôle des connexions électriques et état des câbles\r\n[…] Contrôle de l\'état de la batterie évaporateur\r\n[…] Contrôle de l\'écoulement et pompe de relevage éventuelle\r\n[…] Nettoyage du bac à condensât\r\n[…] Contrôle du fonctionnement du ventilateur\r\n[…] Contrôle de l\'intensité et tension du ventilateur\r\n[…] Contrôle de la charge frigorifique et de l\'étanchéité du circuit\r\n[…] Contrôle de l\'acidité du fluide frigorigène\r\n[…] Contrôle du filtre deshydrateur\r\n[…] Contrôle des pressions HP/BP\r\n[…] Contrôle des pressostats HP/BP (Chaîne de sécurité)\r\n[…] Contrôle de l\'intensité et l\'isolement du compresseur\r\n[…] Contrôle de la tension du compresseur en fonctionnement\r\n[…] Contrôle de l\'état du calorifuge\r\n[…] Contrôle des presse étoupes\r\n[…] Nettoyage complet de l\'unité intérieure\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.05',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (134,'12.03.A','Paratonnerre','[…] Opération sous  traité selon contrat N°',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (135,'51.09.M','Porte coupe feu','[…] Inspection technique\r\n[…] \"Contrôle du bon fonctionnement des P.C.F\r\n- essai en manuel \r\n- essai par simulation du fonctionnement des organes de détection\"\r\n[…] Contrôle de l\'état des galets et de l\'ensemble câbles-poulies\r\n[…] Nettoyage des rails et glissières\r\n[…] Vérification de la liberté de fonctionnement des dispositifs de fermeture\r\n[…] Vérification de l\'absence d\'objet sous la porte\r\n[…] Inspection des systèmes de détection (voir chapitre \"Système de sécurité incendie\")\r\n[…] Contrôle par simulation du bon fonctionnement des détecteurs et des fusibles\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (136,'51.09.S','Porte coupe feu','[…] Contrôle de l\'état des galets et des câbles des portes coulissantes\r\n[…] Nettoyage des rails et glissières\r\n[…] Vérification de la liberté de fonctionnement des dispositifs de fermeture\r\n[…] Vérification de l\'absence d\'obstacle sur la porte\r\n[…] Inspection des systèmes de détection et vérification des sources d\'alimentation\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (137,'51.09.A','Porte coupe feu','[…] Contrôle de l\'alimentation électrique\r\n[…] Contrôle de l\'état de la sparklet\r\n[…] Contrôle du contact de fin de course et du report service de sécurité\r\n[…] Contrôle des joints de scellement et des matériaux réfractaires\r\n[…] Vérification du fonctionnement de la commande manuelle\r\n[…] Contrôle de l\'asservissement électrique du ventilateur\r\n[…] Enregistrement des essais et contrôles dans le registre de sécurité et sur BT préventif\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (138,'30.03.A','Pompe doseuse','[…] Contrôle de la programmation de l\'injection\r\n[…] Contrôle du bon fonctionnement de l\'électrovanne pilote\r\n[…] Nettoyage de la vanne, de la canne d\'aspiration et de la crépine\r\n[…] Manœuvre de la robinetterie\r\n[…] Contrôle des clapets d\'aspiration et de refoulement\r\n[…] Resserrage des presse-étoupes et réfection si nécessaire\r\n[…] Contrôle des connexions électriques\r\n[…] Nettoyage du bac\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (139,'20.07.S','Poste de livraison Gaz','[…] Contrôle de l\'étanchéité du circuit\r\n[…] Manœuvre des vannes (hormis la vanne de barrage gaz)\r\n[…] Contrôle de l\'état des supports et des tuyauteries (corrosion, revêtement)\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (140,'100.02.S','Porte battante','[…] Contrôle visuel de l’aspect général\r\n[…] Contrôle des becs de canne\r\n[…] Contrôle du fonctionnement de la serrure \r\n[…] Contrôle du jeu de la porte\r\n[…] Contrôle visuel des paumelles\r\n[…] Contrôle du ferme porte\r\n[…] Contrôle de la présence des collerettes d’habillage\r\n[…] Graissage des charnières ( selon besoin )',NULL,'0.10',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (141,'51.06.M','Poteaux et bouches incendie','[…]Contrôle visuel de l\'accessibilité et de l\'état apparent, absence de fuites.\r\n[…]Présence de la signalisation (bouches)\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (142,'51.06.S','Poteaux et bouches incendie','[…] Désengorgement de la vidange du coffre (bouches), ou de la colonne (poteaux).\r\n[…] Vérification de l\'état des bouchons, raccords, joints,…\r\n[…] Vérification de l\'état de la soupape\r\n[…] Vérification du fonctionnement du régulateur\r\n[…] Graissage des tiges filetée du régulateur, charnière, genouillères, tourillons, …\r\n[…] Essais de fonctionnement comprenant le contrôle de la pression statique et du débit.  Ost  Inscription sur le registre de sécurité\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (143,'23.08.S','Pompe de circulation','\r\n[…] Contrôle de l\'état de l\'accouplement et de sa protection mécanique\r\n[…] Contrôle de la boite à bornes moteur\r\n[…] Contrôle de l\'intensité absorbée et de l\'isolement du moteur\r\n[…] Contrôle des liaisons équipotentielles de masse\r\n[…] Dépoussiérage du ventilateur de refroidissement du moteur\r\n[…] Relevé du delta P de la pompe\r\n[…] Contrôle des paliers\r\n[…] Contrôle des roulements\r\n[…] Contrôle de l\'alignement du moteur et de la pompe\r\n[…] Contrôle de la fixation et des supports antivibratiles\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (144,'31.02.S','Préparateur  eau chaude sanita','[…] Contrôle de l\'absence de fuite\r\n[…] Contrôle du point de consigne (<55°C)\r\n[…] Contrôle de la fixation de l\'appareil\r\n[…] Remplacement des joints (selon besoin)\r\n[…] Remplacement de la cartouche thermostatique\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,NULL,5,0,0,0,1,NULL,NULL,1,3,NULL),
 (145,'24.03.S','Rideau d\'air chaud','[…] Contrôle du filtre et remplacement si nécessaire\r\n[…] Dépoussiérage des batteries et du moto ventilateur\r\n[…] Contrôle de l\'intensité et de l\'isolement du moto ventilateur \r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nBatterie chaude\r\n[…] Purge de l\'air de la batterie\r\n[…] Contrôle du fonctionnement de la régulation et des électrovannes\r\n[…] Contrôle de la robinetterie d\'isolement, manœuvre des vannes\r\n[…] Contrôle des presses étoupes\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nBatterie électrique\r\n[…] Contrôle de l\'intensité batterie électrique\r\n[…] Contrôle du fonctionnement de la régulation et des sécurités\r\n[…] Contrôle des connexions électriques\r\n[…] Contrôle de l\'état du calorifuge\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (146,'24.01.A','Radiateur','[…] Purge de l\'air\r\n[…] Contrôle du robinet thermostatique\r\n[…] Contrôle de la robinetterie d\'isolement\r\n[…] Contrôle des presse-étoupes\r\n[…] Dépoussiérage\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.25',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (147,'24.07.S','Batterie terminale électrique','[…] Contrôle de la régulation\r\n[…] Vérification des intensités absorbées\r\n[…] Vérification de l\'état des épingles\r\n[…] Contrôle des thermostats de sécurité\r\n[…] Resserrage des connexions\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (148,'24.04.S','Panneau rayonnant','[…] Contrôle de l\'intensité et de l\'isolement\r\n[…] Contrôle du fonctionnement de la régulation et des sécurités\r\n[…] Contrôle des connexions électriques\r\n[…] Dépoussiérage et nettoyage du déflecteur\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (149,'A10005','Régulation','[…] Dépoussiérage des cartes ou des régulateurs\r\n[…] Contrôle et serrage des connexions\r\n[…] Vérification des points de consignes\r\n[…] Vérification des valeurs de gain en proportionnel, intégral et dérivé\r\n[…] Contrôle de l’état et de la cohérence des indications des capteurs\r\n[…] Contrôle de l’état et du fonctionnement des actionneurs\r\n[…] Contrôle de tous les scénarios de fonctionnement en mode normal et dégradé\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,NULL,5,0,0,0,1,NULL,NULL,1,3,NULL),
 (150,'32.02.A','Pompe de relevage et fosse','\r\n[…] Contrôle de l\'état de l\'accouplement\r\n[…] Contrôle de la boite à bornes du moteur\r\n[…] Contrôle de l\'intensité absorbé et de l\'isolement du moteur\r\n[…]Nettoyage de la roue et de la crépine\r\n[…] Contrôle de l\'état du manchon de refoulement ou du raccord souple\r\n[…] Nettoyage complet du puisard et pompage de la fosse de relevage      \r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (151,'32.02.S','Pompe de relevage et fosse','\r\n[…] Contrôle du bon fonctionnement des flotteurs et de ses asservissements \r\n[…] Essai des séquences de démarrage et de mise en sécurité\r\n[…]  Contrôle de l\'étanchéité du clapet de refoulement\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (152,'22.01.A','Réseau Aéraulique','[..] Vérification des gaines: étanchéité, raccordement\r\n[..] Nettoyage des grilles d\'air neuf et de rejet\r\n[..] Contrôle des positions des registres\r\n[..] Nettoyage et réglage des bouches d\'extraction VMC\r\n[..] Nettoyage des diffuseurs de soufflage et d\'extraction (Hors moduline)\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'8.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (153,'23.01.A','Réseau hydraulique','[…] Contrôle de l\'absence de fuite\r\n[…] Contrôle des manchons de dilatation (recommandation des constructeurs: -Ne pas peindre les manchon et prévoir le remplacement tout les 10 ans )\r\n[…] Contrôle des débits sur vannes de réglage (utilisation de la mallette) \r\n[…] Contrôle des thermomètres et des manomètres\r\n[…] Contrôle des purgeurs\r\n[…] Contrôle des filtres\r\n[…] Contrôle du calorifuge\r\n[…] Contrôle du collecteur des réseaux de récupération de purges\r\n[…] Contrôle des pots à boues et évacuations des boues par chasse rapide \r\n[…] Contrôle des supports de tuyauterie\r\n[…] Retouche de peinture\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (154,'51.05.A','Réseau incendie armé','Réseau d\'alimentation\r\n[…] \"Vérifier pour le réseau d\'alimentation ou de réalimentation des sources :\r\n- étanchéité \r\n- fonctionnement des manomètres\r\n- pression de l\'eau au manomètre situé en amont du R.I.A le plus défavorisé\r\n- vérifier le fonctionnement en eau à plein débit du RIA le plus défavorisé et d\'un autre RIA (différent chaque trimestre) jusqu\'à écoulement d\'une eau claire\"\r\n -------------------------------------------------------------------------------------------------------------------------------------             \r\nPompes et surpresseurs\r\n[…] \"Vérifier le moteur d\'entraînement des pompes : \r\n- fonctionnement sans saccade du surpresseur\r\n- le dispositif de mise en route automatique doit fonctionner 3 fois consécutives sans défaillance avec un arrêt d\'environ 1 minute entre chaque démarrage.\"\r\n-------------------------------------------------------------------------------------------------------------------------------------            \r\nRIA\r\n[…] \"Vérifier l\'état de tous les R.I.A par mise sous pression de service et contrôle d\'aspect : \r\n- du tuyau semi rigide en le déroulant complètement sur toute sa longueur\r\n- des fixations d\'extrémité\r\n- des joints d\'étanchéité\"\r\n[…] Consignation du contrôle sur chaque RIA (Date et résultat de la vérification, signature de l\'intervenant)\r\n[…] Changer tous les joints d\'étanchéité de chaque R.I.A et remplacer les tuyaux semi-rigides si nécessaire\"Tous les 10 ans - 5 ans si APSAD\"\r\n[…] Contrôler l\'état interne des tuyauteries par prélèvement pour analyse des manchettes prévues à cet effet\"Tous les 10 ans - 5 ans si APSAD\"\r\n\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (155,'51.05.M','Réseau incendie armé','[…] Vérification de l\'étanchéité et du fonctionnement des vannes de contre barrage, des RIA et de tous les organes mécaniques de l\'installation\r\n[…] Vérification de l\'étanchéité et du fonctionnement de la source d\'eau et contrôle du niveau d\'eau\r\n[…] Vérification de l\'état des dévidoirs (rotation, pivotement, choc éventuel)\r\n[…] Vérification de la présence de tous les éléments constitutifs des RIA (robinet diffuseur, ou autres accessoires)\r\n[…] Vérification de la mise en eau non sous pression des RIA (prêt à fonctionner)\r\n[…] Relevé de la pression sur le manomètre du RIA le plus éloigné\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (156,'80.05.S','Rideau métallique','[...] Contrôle des glissières. Graissage si nécessaire.\r\n[...] Réglage de la tension des chaînes\r\n[...] Contrôle de réducteurs (niveaux)\r\n[...] Vérification de fonctionnement\r\n[...] Réglage des fins de course\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (157,'23.05.A','Vannes et robinetterie','[…] Manœuvre des vannes d\'isolement\r\n[…] Graissage des tiges de vannes\r\n[…] Resserrage des presse-étoupes\r\n[…] Réfection des presse-étoupes\r\n[…] Contrôle des joints de brides et remplacement si fuyards\r\n[…] Contrôle présence étiquette de repérage\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (158,'A10006','Ronde technique','\r\n[…] Contrôle de la disponibilité des équipements sous contrat\r\n\r\n[…] Relevé des compteurs\r\n\r\nCPCU                                   ………………… m3\r\n\r\nGAZ                                     . . ……………….m3\r\n\r\nFUEL                                    ………………….Litres\r\n\r\nELEC                                   .…………………kWh\r\n\r\nAppoint EG                          . …………………m3\r\n\r\nAppoint EC                         ………………….. m3\r\n\r\nAppoint tour aéro                  . …………………m3\r\n\r\nECS                                   ………………….. m3\r\n\r\nAUTRE                             …………………..\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (159,'50.01.T','Système d\'alarme incendie','[…] Contrôle de l\'aspect des déclencheurs manuels \" Bris de glace\"\r\n[…] Contrôle de la charge de batterie des blocs autonomes d\'alarme sonore\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (160,'50.01.S','Système d\'alarme incendie','[…] Contrôle de la tension de la batterie\r\n[…] Essai des signaux sonores et lumineux (Dérangement lignes, Alarme feu, mise hors service, défaut d\'alimentation,…..)\r\n[…] Essai de l\'ensemble des déclencheurs manuels \" bris de glace\"\r\n[…] Contrôle du bon fonctionnement des blocs autonomes d\'alarme sonore\r\n[…] Contrôle des reports d\'alarmes\r\n[…] Essai des commandes manuelles de la baie de signalisation\r\n[…] Remplacement des batteries des sources auxiliaires\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (161,'31.03.A','Bloc sanitaire (Homme et femme','Lavabos\r\n\r\n[…] Analyse bactériologique et légionelle(Préconisation)\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nDouches\r\n[…] Analyse légionelle Semestriel pour les ERP\r\n[…] \"Remplacer les éléments périphériques de distribution (Joints, filtres de robinet, pommes et flexibles de douches) en fonction de leur état d\'usure.\"\r\n[…] \"Détartrage des pommes de douches dans une solution à Ph acide telle que: \r\nAcide sulfamique ; Vinaigre blanc pendant 15 mn \" (Si nécessaire)\r\n[…] Rinçage puis désinfection dans une solution chlorée contenant au moins 50 mg/L de chlore libre (13 ml d\'eau de Javel dans 10 litres d\'eau) pendant 30 minutes avant repose (Si nécessaire)\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (162,'31.03.M','Bloc sanitaire (Homme et femme','[…] Contrôle absence de fuite\r\n[…] Contrôle de l\'écoulement des lavabos, urinoirs, WC\r\n[…] Contrôle de l\'état de la robinetterie, mousseurs, mobilier sanitaire\r\n[…] Contrôle de l\'éclairage\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.10',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (163,'31.03.S','Bloc sanitaire (Homme et femme','Lavabos\r\n[…] Contrôle absence de fuite\r\n[…] Contrôle du mécanisme de la bonde\r\n[…] Manœuvre et contrôle des vannes d\'isolement\r\n[…] Contrôle du fonctionnement séchoir à main\r\n[…] \"Détartrage des mousseurs dans une solution à Ph acide telle que:\r\n Acide sulfamique ; Vinaigre blanc pendant 15 mn \"(Si nécessaire)\r\n[…] Rinçage puis désinfection des mousseurs dans une solution chlorée contenant au moins 50 mg/L de chlore libre (13 ml d\'eau de Javel dans 10 litres d\'eau) pendant 30 minutes avant repose (Si nécessaire)\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nWC\r\n[…] Contrôle absence de fuite\r\n[…] Contrôle du robinet d\'arrêt\r\n[…] Contrôle de l\'écoulement WC\r\n[…] Contrôle état et fixation abattant WC\r\n[…] Contrôle du bon fonctionnement de la chasse d\'eau WC\r\n[…] Contrôle du bon fonctionnement du mécanisme d\'eau\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (164,'90.02.S','Assécheur d\'air','[…] Contrôle du fonctionnement général\r\n[…] Contrôle de l\' intensité absorbée et de l\'isolement électrique\r\n[…] Contrôle de l’étanchéité des circuits frigorifiques\r\n[…] Essai des pressostats HP/BP\r\n[…] Essai du thermostat antigel et du pressostat huile\r\n[…] Contrôle de l’état du ventilateur et de la  batterie\r\n[…] Contrôle du bon écoulement des eaux de condensation\r\n[…] Resserrage des connexions électriques\r\n[…] Nettoyage du ventilateur et de la batterie\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (165,'60.06.S','Sonorisation','[..] Contrôle général de l\'installation\r\n[..] Nettoyage et vérification des connexions\r\n[..] Vérification tension alimentation\r\n[..] Vérification des batteries et chargeurs\r\n[..] Contrôle ampli des hauts parleurs\r\n[..] Essais du système\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (166,'51.01.A','Extinction automatique sprinkl','[…] Contrôle de l\'état des supports et des canalisations\r\n[…] Contrôle du dispositif antigel\r\n[…] Contrôle du dispositif anticorrosion\r\n[…] Essai des performances initiales\r\n[…] Rinçage des canalisations (tous les 1 à 6 ans selon la qualité de l\'eau)\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nPoste de contrôle sprinkler\r\n[…] Vérification du joint d\'étanchéité, de l\'ouverture totale du clapet\r\n[…] Nettoyage du clapet d\'alarme\r\n[…] Nettoyage du filtre et de l\'injecteur d\'arrivée d\'eau de la turbine du gong hydraulique et graissage des pièces en rotation \r\n[…] Contrôle du fonctionnement de l\'accélérateur et des exhausteurs s\'ils existent, selon les  préconisations des constructeurs\r\n[…] Pour les installations sous air, contrôle du démarrage automatique du compresseur d\'air par chute volontaire de la pression d\'air\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nCanalisation en amont du poste\r\n[…] Essai d\'écoulement pour contrôle de la propreté de l\'eau en bout de réseau\r\n[…] Contrôle de la protection cathodique des réseaux en acier\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (167,'51.01.M','Extinction automatique sprinkl','[…] Contrôle de la disposition des sprinklers par rapport aux obstacles et disposition des locaux\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nMatériel de rechange\r\n[…] Contrôle de la présence dans le stock des lots de matériels de rechange suivants :\r\n\r\nMoteur Diesel du surpresseur :\r\n1 cartouche filtre à huile avec joints  \r\n1 cartouche filtre à gasoil avec joints\r\n1 jeu de courroies\r\n1 jeu  de jeu complet de joints\r\n1 jeu complet de durits\r\n1 injecteur.\r\nSprinkler de même type:\r\n12 sprinklers, installation de classe I\r\n24 sprinklers, installation de classe II\r\n36 sprinklers, installation de classe III\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (168,'51.01.S','Extinction automatique sprinkl','Poste de contrôle sprinkler\r\n\r\n[…] Manœuvre de la vanne d\'arrêt du poste amont\r\n[…] Pour les installations de type alternatif, procéder au passage sous eau ou sous air selon la saison\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (169,'26.02.S','Climatiseur Split system','[…] Contrôle de l\'état général\r\n[…] Contrôle du fonctionnement de la régulation et des sécurités\r\n[…] Contrôle du fonctionnement du thermostat \r\n[…] Contrôle de la commande Chaud/Froid/Vitesse ventilateur\r\n[…] Contrôle des connexions électriques\r\n[…] Contrôle de l\'état des câbles\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSplit unité intérieure\r\n[…] Contrôle de la batterie évaporateur\r\n[…] Contrôle de l\'écoulement et pompe de relevage éventuelle\r\n[…] Nettoyage du bac à condensât\r\n[…] Contrôle du filtre et remplacement si nécessaire\r\n[…] Nettoyage et dépoussiérage du ventilateur\r\n[…] Contrôle de l\'intensité du ventilateur\r\n[…] Contrôle de la tension du ventilateur en fonctionnement\r\n[…] Contrôle du fonctionnement normal de la batterie électrique\r\n[…] Contrôle du thermostat de sécurité\r\n[…] Nettoyage complet de l\'unité intérieure\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSplit unité extérieure\r\nContrôle de la charge frigorifique et de l\'étanchéité du circuit\r\nContrôle de l\'acidité du fluide frigorigène\r\nContrôle du filtre deshydrateur\r\nContrôle des pressions HP/BP\r\nContrôle des pressostats HP/BP (Chaîne de sécurité)\r\nContrôle de l\'intensité et l\'isolement du compresseur\r\nContrôle de la tension du compresseur en fonctionnement\r\nContrôle de l\'état du calorifuge\r\nContrôle du pressostat se sécurité haute pression\r\nContrôle des silentblocs\r\nNettoyage complet de l\'unité extérieure\r\nContrôle de la charge frigorifique et  de l\'étanchéité du circuit\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (170,'50.02.T','Détection incendie','[…] Contrôle de l\'aspect des déclencheurs manuels (Bris de glace)\r\n[…] Contrôle de la charge des batteries des blocs autonomes d\'alarmes sonores\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (171,'50.02.S','Détection incendie','[…] Opération sous traitée selon contrat N°\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (172,'100.04.A','Store','[...] Contrôle de la fixation \r\n[...] Contrôle des guides\r\n[...] Contrôle des connexions électriques\r\n[...] Contrôle des lacettes\r\n[...] Contrôle du bon fonctionnement\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.10',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (173,'30.10.A','Surpresseur','[…] Contrôle du pressostat de commande\r\n[…] Relevé des pressions de fonctionnement\r\n[…] Contrôle des pressions d\'asservissement\r\n[…] Contrôle de la boite à bornes moteur\r\n[…] Contrôle de l\'intensité moteur\r\n[…] Contrôle de l\'isolement et des liaisons équipotentielles\r\n[…] Dépoussiérage du ventilateur de refroidissement du moteur\r\n[…] Contrôle des roulements et graissage éventuel\r\n[…] Contrôle de l\'accouplement\r\n[…] Contrôle de la protection mécanique des parties tournantes\r\n[…] Contrôle de la fixation de l\'ensemble et des plots antivibratiles\r\n[…] Contrôle du filtre à tamis et nettoyage éventuel\r\n[…] Contrôle du fonctionnement du clapet anti-retour\r\n[…] Essai du basculement automatique P1/P2\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (174,'11.08.A','Tableau  électrique d\'étage','[…] Essai Auto/Arrêt/Manu\r\n[…] Essai arrêt d\'urgence\r\n[…] Contrôle de l\'intensité et de l\'équilibrage des phases\r\n[…] Contrôle de la présence du schéma dans l\'armoire électrique. Remise à jour du schéma si nécessaire\r\n[…] Essai des disjoncteurs différentiels\r\n[…] Essai des reports et télécommandes GTB\r\n[…] Contrôle cohérence des indicateurs de mesure en façade\r\n[…] Suivi de la procédure de consignation \r\n[…] Contrôle du serrage des connexions\r\n[…] Contrôle du calibrage des fusibles par rapport au schéma\r\n[…] Contrôle du pouvoir coupe circuit des disjoncteurs par rapport au schéma\r\n[…] Contrôle des liaisons équipotentielles\r\n[…] Contrôle état des goulottes\r\n[…] Contrôle état des presse-étoupes\r\n[…] Contrôle fixation de l\'armoire\r\n[…] Nettoyage et dépoussiérage\r\n[…] Suivi de la procédure de déconsignation \r\n[…] Contrôle thermique infrarouge Opération sous traitée\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (175,'23.04.S','Traitement des réseaux eau gly','[…] Contrôle du PH ( = 9 )\r\n[…] Relevé de la consommation en produit de traitement\r\n[…] Contrôle et réglage, si nécessaire, de l\'injection en produit de traitement (mg produit/litre d\'appoint)\r\n[…] Mesure de la protection antigel\r\n[…] Analyse physico-chimique de l\'eau et des dépôts  Ost\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (176,'110.01.A','Entretien terrasse','[…]  Opération sous traitée à _________________________________________\r\n\r\nContrat N° ____________________________\r\n\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (177,'11.01.A','TGBT','[…] Contrôle fonctionnement éclairage armoire\r\n[…] Contrôle état et fixation des chemins de câbles\r\n[…] Suivi de la procédure de consignation \r\n[…] Nettoyage et dépoussiérage\r\n[…] Graissage des articulations et contacts mécaniques\r\n[…] Contrôle du serrage des jeux de barre  en fonction de la thermographie  \r\n[…] Contrôle du serrage des connexions  en fonction de la thermographie \r\n[…] Contrôle connexions, bruits et fixations des relais\r\n[…] Contrôle de la présence du schéma\r\n[…] Contrôle du pouvoir coupe-circuit des disjoncteurs par rapport au schéma\r\n[…] Contrôle du réglage des relais thermiques par rapport au schéma\r\n[…] Contrôle du réglage des relais magnétiques par rapport au schéma\r\n[…] Contrôle des liaisons équipotentielles\r\n[…] Contrôle de l’alimentation auxiliaire et essai de décharge\r\n[…] Remplacement des batteries auxiliaires  Tous les 3 à 5 ans\r\n[…] Contrôle de la date du dernier remplacement\r\n[…] Sauvegarde des programmes automates\r\n[…] Contrôle du réglage des disjoncteurs différentiels et essais\r\n[…] Essai des reports et commandes GTB\r\n[…] Remise à jour du schéma si nécessaire\r\n[…] Suivi de la procédure de déconsignation \r\n[…] Contrôle cohérence des indicateurs de mesure en façade\r\n[…] Contrôle thermographie infrarouge   Ost\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (178,'23.02.T','Traitement des réseaux fermés','[…] Contrôle du TH (=0°C)\r\n[…] Contrôle du PH (=9,5)\r\n[…] Contrôle teneur en sulfites ( >40 mg )\r\n[…] Relevé de la consommation en produit de traitement\r\n[…] Contrôle et réglage, si nécessaire, de l\'injection en produit de traitement (mg produit/litre d\'appoint)\r\n[…] Analyse physico-chimique de l\'eau   Ost   (Préconisation)\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (179,'23.03.T','Traitement des réseaux ouverts','[…] Contrôle du TH ( = 0°C )\r\n[…] Contrôle du PH ( 8,5 < PH < 9,3 )\r\n[…] Contrôle du taux de concentration ( < 3 )\r\n[…] Relevé de la consommation en produit de traitement\r\n[…] Contrôle et réglage ,si nécessaire, de l\'injection en produit de traitement (mg produit/litre d\'appoint)\r\n[…] Injection ponctuelle, si nécessaire, d\'un produit de traitement bactéricide et algicide\r\n[…] Analyse physico-chimique de l\'eau   Ost\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (180,'21.06.M','Tour de refroidissement','[…] Contrôle du bon fonctionnement du traitement d\'eau\r\n[…] Relevé du compteur d\'eau d\'appoint\r\n[…] Contrôle du niveau bas du bac\r\n[…] Relevé des températures d\'eau E/S\r\n[…] Contrôle du taux de déconcentration\r\n[…] Contrôle de l\'état de propreté des surfaces\r\n[…] Analyse d\'eau pour recherche de LEGIONELLA\r\n            - Pour les installations soumises à autorisation recherche de légionelle mensuelle\r\n            - Pour les installations soumises à déclaration recherche de légionelle bimestrille\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (181,'21.06.S','Tour de refroidissement','[…] Contrôle de l\'état des packings et du circuit de pulvérisation\r\n[…] Contrôle de l\'entartrage et de la corrosion du bac\r\n[…] Contrôle du système d\'appoint d\'eau\r\n[…] Contrôle du bon fonctionnement de la déconcentration automatique\r\n[…] Contrôle de l\'intensité de la résistance antigel et du cordon chauffant ( voir gamme cordon chauffant )\r\n[…] Contrôle du delta P pompe de pulvérisation ( tour à circuit fermé )\r\n[…] Contrôle du delta P batterie d\'échange ( tour à circuit fermé )\r\n[…] Contrôle de l\'état de la tension des courroies\r\n[…] Contrôle de l\'état de la protection mécanique du système de transmission\r\n[…] Contrôle de l\'alignement des poulies\r\n[…] Contrôle roulements et graissage paliers\r\n[…] Contrôle des raccordements sur la boite à bornes du moteur\r\n[…] Contrôle de l\'intensité et de l\'isolement du moteur de ventilation\r\n[…] Contrôle de la fixation des volutes\r\n[…] Contrôle de l\'état des plots antivibratiles\r\n[…] Contrôle de la fixation des appareils de mesure et des liaisons équipotentielles\r\n[…] Contrôle de la cohérence des appareils de mesure\r\n[…] Mesure et enregistrement des performances si nécessaire\r\n[…] Renseignement du livret d\'entretien \r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'4.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (182,'21.06.A','Tour de refroidissement','[…] Vidange, nettoyage et désinfection des circuits d\'eau et des parties périphériques. Désinfection ( annuelle ou avant chaque remise en service après un arrêt prolongé) par choc chloré (30 à 50 mg/litre de chlore libre avec au moins 2 à 3 heures de circulation) puis rinçage. \r\n[…] Renseignement du livret d\'entretien\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'6.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (183,'10.04.A','Transformateur à Huile','[…] Contrôle de la présence et de l\'état du dispositif de rétention sous le transformateur \r\n[…] Suivi de la procédure de consignation \r\n[…] Contrôle de l\'état et de la fixation des chemins de câbles\r\n[…] Contrôle du serrage des connexions\r\n[…] Contrôle du circuit de la mise à la terre en fonction du régime de neutre\r\n[…] Dépoussiérage du transformateur\r\n[…] Test de la protection thermique du transformateur\r\n[…] Test de la protection thermique DGPT2 du transformateur\r\n[…] Prélèvement du diélectrique pour analyse   \r\n[…] Contrôle de la date du dernier prélèvement  Ost  Fréquence préconisée par le constructeur  2 à 5 ans \r\n[…] Essai des reports GTB\r\n[…] Suivi de la procédure de déconsignation \r\n[…] Nettoyage du local technique\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (184,'10.03.A','Transformateur PCB','[…] Contrôle de la présence et de l\'état du dispositif de rétention sous le transformateur \r\n[…] Contrôle de la présence de l\'étiquette jaune  fixée sur l\'appareil portant la mention : \"Cet appareil  contient des PCB qui pourraient contaminer l\'environnement et dont l\'élimination est réglementée\"\r\n[…] Suivi de la procédure de consignation \r\n[…] Contrôle de l\'état et de la fixation des chemins de câbles\r\n[…] Contrôle du serrage des connexions\r\n[…] Contrôle du circuit de la mise à la terre en fonction du régime de neutre\r\n[…] Dépoussiérage du transformateur\r\n[…] Test de la protection thermique du transformateur\r\n[…] Prélèvement du diélectrique pour analyse   Ost Fréquence préconisée par le constructeur 2 à 5 ans\r\n[…] Contrôle de la date du dernier prélèvement\r\n[…] Essai des reports GTB\r\n[…] Suivi de la procédure de déconsignation \r\n[…] Nettoyage du local technique\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nEnvironnement\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\n\r\n\"Les appareils contenant des PCB et ayant fait l\'objet d\'une déclaration ou d\'un acte valant déclaration doivent porter un marquage indélébile reprenant les indications suivantes :\r\nAppareil contenant des PCB:concentration mesurée ou supposée (en ppm de la masse), date de la mesure (éventuelle),date de la déclaration.\r\nLes appareils décontaminés ayant contenu des PCB doivent porter le marquage indélébile suivant : Appareil décontaminé ayant contenu des PCB: le liquide contenant des PCB a été remplacé : \r\npar (nom du substitut) ;(date) ;\r\npar (nom de l\'entreprise).\r\nConcentration en PCB : \r\n- de l\'ancien liquide (ppm en masse) ;\r\n- du nouveau liquide (ppm en masse)\r\nle marquage indélébile  (format minimum 50 x 75 mm) doit être visible depuis l\'accès principal du local. A défaut, un marquage doit être apposée à l\'entrée du local.\"',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (185,'10.02.A','Transformateur sec','[…] Suivi de la procédure de consignation\r\n[…] Contrôle  de l\'état et de la fixation des chemins de câbles\r\n[…] Contrôle des protections disjoncteurs\r\n[…] Contrôle du serrage des connexions, de l\'absence d\'échauffements, d\'amorçage\r\n[…] Contrôle du circuit de la mise à la terre en fonction du régime de neutre\r\n[…] Dépoussiérage du transformateur\r\n[…] Contrôle de la consigne du thermostat d\'alarme et du thermostat de déclenchement selon préconisations constructeur \r\n[…] Essai des reports GTB\r\n[…] Suivi de la procédure de déconsignation\r\n[…] Nettoyage du local technique\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL);
INSERT INTO `gamme` (`game_seq`,`game_code`,`game_libelle`,`game_contenu`,`game_consiparti`,`game_dureepres`,`game_dureejour`,`game_verte`,`game_stopservic`,`game_gen_diff`,`game_bool_inactive`,`game_bdocument`,`game_maj_gene`,`game_tope_fk`,`game_dom_fk`,`game_tdef_fk`) VALUES 
 (186,'26.05.A','Unité gainable','[…] Mesure du débit global minimal d\'air neuf de l\'installation\r\n[…] Mesure et enregistrement des performances\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (187,'26.05.S','Unité gainable','[…] Contrôle du bon fonctionnement du moteur de ventilation\r\n[…] Contrôle de l\'intensité et de l\'isolement de la batterie électrique\r\n[…] Contrôle  et essais des sécurités des batteries électrique\r\n[…] Nettoyage du bac de récupération des condensats\r\n[…] Contrôle de l\'étanchéité des batteries\r\n[…] Contrôle de l\'état des soufflets et plots antivibratiles\r\n[…] Contrôle des liaisons équipotentielles\r\n[…] Contrôle des presse-étoupes\r\n[…] Contrôle des vannes et servomoteur\r\n[…] Nettoyage intérieur complet du caisson\r\n[…] Nettoyage extérieur complet du caisson\r\n[…] Remplacement des filtres si nécessaire\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRégulation\r\n[…] Dépoussiérage des cartes ou des régulateurs\r\n[…] Contrôle serrage des connexions\r\n[…] Vérification des points de consignes et paramètres de réglages\r\n[…] Contrôle de l\'état de fonctionnement des actionneurs\r\n[…] Mesures\r\n[…] Mesure du débit global minimal d\'air neuf de l\'installation\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (188,'11.11.A','Variateur de vitesse','[…] Dépoussiérage du variateur\r\n[…] Contrôle et serrage des connexions\r\n[…] Vérification des paramètres de commande et de sécurité\r\n[…] Contrôle du signal d\'entrée et de sortie\r\n[…] Contrôle de la ventilation de l\'armoire et remplacement du filtre si nécessaire\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'1.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (189,'26.09.S','Ventilo-convecteur','[…] Contrôle du filtre et remplacement si nécessaire\r\n[…] Contrôle du fonctionnement des commutateurs Chaud/Froid/Ventilateur\r\n[…] Contrôle du bon fonctionnement de la régulation et des électrovannes\r\n[…] Contrôle des connexions électriques\r\n[…] Contrôle et dépoussiérage du moto ventilateur\r\n[…] Contrôle et dépoussiérage des batteries\r\n[…] Contrôle évacuation et pompe de relevage éventuelle\r\n[…] Nettoyage du bac à condensât\r\n[…] Contrôle calorifuge et état extérieur\r\n[…] Contrôle du fonctionnement normal de la batterie électrique\r\n[…] Contrôle du thermostat de sécurité\r\n[…] Contrôle de l\' encombrement\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'0.50',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (190,'51.08.A','Volet coupe feu','[…] Contrôle de l\'alimentation électrique\r\n[…] Contrôle de l\'état de la sparklet\r\n[…] Contrôle du contact de fin de course et du report service de sécurité\r\n[…] Contrôle des joints de scellement et des matériaux réfractaires\r\n[…] Vérification du fonctionnement de la commande manuelle\r\n[…] Contrôle de l\'asservissement électrique du ventilateur\r\n[…] Enregistrement des essais et contrôles dans le registre de sécurité et sur BT préventif\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (191,'51.08.M','Volet coupe feu','[…] Contrôle par simulation du bon fonctionnement des détecteurs et des fusibles\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (192,'51.08.S','Volet coupe feu','[…] Contrôle de l\'état des galets et des câbles des portes coulissantes\r\n[…] Nettoyage des rails et glissières\r\n[…] Vérification de la liberté de fonctionnement des dispositifs de fermeture\r\n[…] Vérification de l\'absence d\'obstacle sur la porte\r\n[…] Inspection des systèmes de détection et vérification des sources d\'alimentation\r\n\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (193,'27.02.S','Ventilateur centrifuge','[…] Contrôle de l\'état général\r\n[…] Contrôle de l\'état de la volute\r\n[…] Contrôle de l\'état de la protection mécanique des courroies\r\n[…] Contrôle de l\'état de la tension des courroies\r\n[…] Contrôle de l\'alignement des poulies\r\n[…] Contrôle des roulements et graissage des paliers\r\n[…] Contrôle des raccordements sur la boite à bornes du moteur\r\n[…] Contrôle de l\'intensité et de l\'isolement du moteur de ventilation\r\n[…] Contrôle de la fixation de la volute et du moteur\r\n[…] Contrôle de l\'état des plots antivibratiles\r\n[…] Nettoyage complet\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (194,'27.03.S','Ventilateur hélicoïdal','[…] Contrôle de l\'état général\r\n[…] Contrôle de l\'hélice et du jeu d\'arbre\r\n[…] Contrôle de l\'état de la protection mécanique des courroies\r\n[…] Contrôle de l\'état de la tension des courroies\r\n[…] Contrôle des roulements et graissage des paliers\r\n[…] Contrôle des raccordements sur la boite à bornes du moteur\r\n[…] Contrôle de l\'intensité et de l\'isolement du moteur \r\n[…] Contrôle de l\'état de la cage ou des grilles\r\n[…] Contrôle de la fixation du ventilateur et du moteur\r\n[…] Contrôle de l\'état des plots antivibratiles\r\n[…] Nettoyage complet\r\n\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nSécurité\r\n-------------------------------------------------------------------------------------------------------------------------------------\r\nRespect des procédures de consignation\r\nPort des équipements de protection individuelle\r\n-------------------------------------------------------------------------------------------------------------------------------------',NULL,'2.00',5,0,0,0,1,NULL,NULL,1,3,NULL),
 (195,'CO.001','Il fait trop chaud','Merci d\'intervenir',NULL,NULL,NULL,0,0,0,1,NULL,NULL,3,3,1),
 (196,'CO.002','Il fait trop froid','Merci d\'intervenir',NULL,NULL,NULL,0,0,0,1,NULL,NULL,3,3,1),
 (197,'CO.003','Trop de bruit','Merci d\'intervenir',NULL,NULL,NULL,0,0,0,1,NULL,NULL,3,3,NULL),
 (198,'CO.004','Trop de vent','Merci d\'intervenir',NULL,NULL,NULL,0,0,0,1,NULL,NULL,3,3,1),
 (199,'CO.005','WC bouché','Merci d\'intervenir',NULL,NULL,NULL,0,0,0,1,NULL,NULL,3,3,NULL),
 (200,'CO.006','Lavabo bouché','Merci d\'intervenir',NULL,NULL,NULL,0,0,0,1,NULL,NULL,3,3,NULL),
 (201,'CO.007','Poubelle pleine','Merci d\'intervenir',NULL,NULL,NULL,0,0,0,1,NULL,NULL,3,3,NULL),
 (202,'CO.008','Plus de courant','Merci d\'intervenir',NULL,NULL,NULL,0,0,0,1,NULL,NULL,3,3,2);


--
-- Definition of table `gamme_attr`
--

